Its main features are to: èècapture all the data related to the turbines (wind speed and direction, position of the nacelle, active and reactive power, RPM of the generator, etc.), machine status (run, ready, stop, emergency, service, etc.), and events/ alarms (error code from the turbine); èèmonitor the status of the medium and high voltage switching devices and the main electrical parameters (active and reactive power, voltage and phase currents, cosj, network frequency, etc.), the exceeding of thresholds and the possible causes of trips; èèsend commands: stop, reset and start the turbines, open and close the substation switches, apply the active power limitations to meet the constraints imposed by the Network Operator, etc.; èèmonitor the status of weather stations, either isolated or connected to the wind farm (towers with different types of sensors installed at different heights: wind speed and direction, atmospheric pressure, temperature, humidity, etc.); èèview and manage alarms, which are also notified to operators in the control room and in the field; these notifications will be sent by the system when, for example, a threshold is exceeded, such as temperature or pressure of a specific component of the turbine, or when an operating mechanism of the electrical substation is opened; èèanalyse all of the data for a set period of time, obtaining the trends of the variables, aggregated curves, list of events/alarms that occurred for both the turbines and the electrical substation, etc.