http___www.waterpurificationsystem.com.tw_ga_reverse-osmosis-system.html_1.xml
1.1 2.1 3.1 4.1 4.2 4.3 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 22.1 23.1 24.1 25.1 26.1 27.1 27.2 27.3
Model: RD Reverse Osmosis System Product Overview ROTEK compact commercial reverse osmosis system is a durable piece of equipment which, with proper care and maintenance will last for many years. RD series systems are part of a family of reverse osmosis units designed for operation with fresh and brackish feedwaters having TDS values below 2,000ppm. Models are available with permeate outputs of between 250 and 1000 litres/hr as shown in the specifications tables. Product Features * High pressure stainless steel membrane housing * Low Energy TFC spiral membrane * High pressure S/S braided flexible hose * Rotary vane pump / anti-corrosion multistage pump * Microprocessor controller with TDS readout * Automatic flush with raw water * Low feedwater pressure sensor * Storage tank level sensor input * Permeate and reject flow rotameters * Adjustable pressure regulator valve * Liquid filled pressure gauges (Filter Feed, RO Feed) * Concentrate recycling valve * Electro-polished stainless steel frame Specifications Feed Water Requirments TDS: < 2,000 ppm (choose BW systems when exceed) Turbidity: < 1.0 NTU (required pre-treatment when exceed) SDI: < 5.0 (required pre-treatment when exceed) Hardness: < 50 ppm (required pre-treatment when exceed) Residual Chlorine: < 0.1 ppm (required pre-treatment when exceed) Feed water quality, pressures and flow rates have a significant impact on the performance of any reverse osmosis system. To ensure reliable and consistent long-term performance, it is important to supply feed water having the minimum specifications detailed below. If your feed water supply is marginal, you should consider using a feed water break tank and booster pump to supply the system.
1.1 2.1 3.1 4.1 4.2 4.3 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 22.1 23.1 24.1 25.1 26.1 27.1
múnla: RD droim ar ais osmosis Córas forbhreathnú táirge rotek córas osmosis droim ar ais dhlúth tráchtála píosa durable trealamh a, le cúram cuí agus cothabháil ar feadh blianta fada. Tá rd córais sraith chuid de theaghlach na n-aonad osmosis a athrú atá deartha le haghaidh oibriú le feedwaters úr agus goirt a bhfuil luachanna Teachtaí Dála faoi bhun 2,000 csm. Tá samhlacha atá ar fáil le dtréscaoileann aschuir idir 250 agus 1000 lítear / hr mar a thaispeántar sna táblaí sonraíochtaí. táirge gnéithe * dhosmálta brú tithíochta membrane ard cruach * fuinneamh membrane íseal bíseach TFC * brú ard s / s braided píobáin solúbtha * caidéil eite rothlacha /frith - caidéil ilchéime creimeadh * rialtóir microprocessor le readout Teachtaí Dála * flush uathoibríoch le huisce amh * braiteoir brú íseal Feedwater * stóráil umar ionchur braiteoir leibhéal * dtréscaoileann agus rotameters sreabhadh dhiúltú * comhla rialtóir adjustable bhrú * brúmhéadair leachtach a líonadh (beatha scagaire, ro beatha) * comhla athchúrsála díriú * electro - snasta déanta as cruach dhosmálta fráma Sonraíochtaí beatha uisce requirments Teachtaí Dála: < sreabhadh uisce caolaithe (Roghnaigh córais bw nuair a théann) mhoirtiúlacht: < 1.0 NTU (gá réamh - chóireáil nuair a théann) SDI: < 5.0 (gá réamh - chóireáil nuair a théann) chruas: < sreabhadh uisce caolaithe (gá réamh - chóireáil nuair a théann) clóirín iarmharach: < 0.1 Raon leathan Ph (gá réamh - chóireáil nuair a théann) Cháilíocht an uisce beatha, tá brúnna agus rátaí sreabhadh tionchar suntasach ar fheidhmíocht aon chóras osmosis a athrú. a chinntiú iontaofa agus comhsheasmhach fada - fheidhmíocht téarma, tá sé tábhachtach a chur ar fáil uisce beatha a bhfuil na sonraíochtaí íosta sonraithe thíos. má tá do sholáthar uisce beatha imeallach, ba cheart duit smaoineamh ag baint úsáide as beatha umar sos uisce agus teanndáileog caidéil a sholáthar ar an gcóras.