http___mgc.com.hr_proizvodi_duresca-sabirnice__1.xml
1.1 2.1 3.1 3.2 3.3 3.4 3.5 3.6 4.1 4.2 4.3 5.1 6.1 7.1 8.1 8.2 8.3 8.4 8.5 8.6 8.7 9.1 10.1 10.2 11.1 11.2 12.1 13.1 13.2 13.3 13.4 13.5 14.1
The conductor is made up of a cylindrical aluminium alloy type EN AW-6101B T7, or of an electrolytic... The conductor is made up of a cylindrical aluminium alloy type EN AW-6101B T7, or of an electrolytic copper. The insulation lies directly on the conductor and consists of wrapped paper dried under vacuum and impregnated with EPOXY resin. Conductive grading layers are embedded during the wrapping in the insulation for the field control. An earth screen in copper of min. 50 mm2 is embedded in the insulation. It is, in case of an exceptional failure, the best protection for the people and the installation. On the whole lenght of the bar, the surface of the insulation is covered by a protection tube. This tube provides an effective barrier against moisture ingress and an good protection against shocks. The single bars are manufactured in lengths up to 10 meters. For longer bus runs or by tight place conditions where only short pieces can be installed, the single busbars are joined together on site. The joints are flexible or rigid and are also electrically shielded by insulating sleeve. The single bars are custom made and their installation consists mainly of the easy assembly of standard components. The high current connection and the sealing flange are adapted to the GIS connection. SF-6 postrojenja. The connection to the transformer can be insulated or bare. For the fully insulated connection, the transformer is equipped with an oil-oil bushing. The busbar to bushing connection is protected by an insulating cylinder. The bushing is custom design to match with the transformer on one side and with the insulating cylinder on the other side. For this reason it is advantageous that the bushings are provided by MGC. An open connection from the Duresca bus bar terminal to the transformer bushing terminal is also available. The outdoor ends of the bars are protected by silicone or porcelain insulators similar to those of outdoor bushings. The adjustment of the length occurs in the insulating sleeves through the use of flexible connectors. Each single bar is subject to a routine test schedule which consists of: measuring of capacitance, tan delta, partial discharges and 50 Hz withstand voltage test. Each GIS connection part is additionally pressure tested to check its sealing properties. Busbars IP 67. Cylinder and protection boxes IP 64 as standard, IP 68 on request. -40° do +40°C (other ranges on request) The insulation body is protected by a high quality (PA12) corrugated tube in polyamide. Furthermore, the corrugation provides an increase of the creepage distance on the end of the busbar. The selected quality authorizes as well an indoor or outdoor use. The good behaviour in the severe climatic conditions was checked according to the ASTM Cd 2565 standard and tested in an independant laboratory. MGC has used this type of protection tube for more than 20 years. In case of particular requirement in an heavely polluted area the polyamid corrugated protection tube could be replaced by one in CrNisteel or Aluminium.
1.1 2.1 3.1 4.1 4.2 4.3 4.4 4.5 4.6 5.1 5.2 5.3 6.1 7.1 7.2 8.1 9.1 10.1 10.2 10.3 10.4 11.1 11.2 11.3 12.1 13.1 13.2 13.3 14.1 14.2 15.1 16.1 17.1 17.2 17.3 17.4 18.1 18.2 18.3 18.4
Kvalitetan visoko vrijedan sustav sabirnica koji osigurava životni vijek veći od 30 godina, te pruža... Kvalitetan visoko vrijedan sustav sabirnica koji osigurava životni vijek veći od 30 godina, te pruža kompaktan dizajna i uske radijuse savijanja. Posebno projektirani sustav koji omogućuje jednostavnu brzu montažu te uporabu bez održavanja. Vodič se sastoji od okrugle aluminijske šipke ili cijevi izrađene od legure EN AW-6101B T7, ili iz elektrolitno-bakrene šipke. Na njemu direktno leži Duresca izolacija iz krep papira, koja se impregnira epoksidnom smolom pod vakuumom. Provodni slojevi postavljaju se tijekom procesa omatanja u izolaciju radi usmjeravanja strujnog polja. Uzemljujući sloj, koji se sastoji od bakrenog pletiva minimalnog presjeka 50mm2, je također utopljen u izolaciju i čini eklektično polje sigurnim na dodir. Izolacijska površina je cijelom duljinom sabirnice zaštićena čvrsto nanesenom glatkom ili valovitom rebrastom zaštitnom oplatom. Ona štiti od prodora vlage i daje dodatno mehaničku zaštitu. Pojedinačne sabirnice proizvode se u dužinama do 10 metara. Kod duljih vodova ili kada se zbog manjka prostora mogu postaviti samo kraći komadi sabirnice, pojedinačne sabirnice se spajaju tijekom postavljanja. Ova spojna mjesta mogu biti kruta ili fleksibilna i zaštićuju se putem zaštitnih navlaka čime su sigurna na dodir. Pojedinačne sabirnice proizvode se na mjeru u našoj tvornici. Montaža se sastoji od jednostavnih vijčanih spojeva u sustavu dogradnih jedinica. Visokonaponski spoj na prirubnici prilagođava se dimenzijama i izvedbama SF-6 postrojenja. Spajanje na transformator izvodi se ili potpuno izolirano ili bez zaštite. Kod potpuno izoliranog priključka transformator je opremljen uljnim izolatorom. Spojno mjesto sabirnica-izolator zaštićuje se izoliranom navlakom. Izolator se na transformatorskoj strani prilagođava posebnostima proizvođača transformatora, sa druge strane dimenzije vodilice i prirubnice moraju odgovarati izolacijskoj navlaci. Zbog toga je prednost što MGC isporučuje i transformatorske izolatore. Spojevi se također mogu izvoditi direktno na kleme transformatora postavljenih na otvorenom. Slobodni krajevi su tada opskrbljeni silikonskim navlakama ili porculanskim izolatorima kao kod normalnih izolatora za vanjsku primjenu. Dužina sabirnice može se podešavati preko izolatorskih cilindara. Svaka pojedinačna sabirnica rutinski se električno ispituje u našoj tvornici. Ispitivanja se sastoje od: ispitivanje kapaciteta, faktora gubitka i mjerenja djelomičnog pražnjenja te ispitivanja napona pri 50 Hz. Svaki priključak na SF-6 postrojenja ispituje se na hermetičnost. Strujne sabirnice = IP 67. Izolirajuće navlake i zaštitna kućišta standardno IP 64, opcionalno su moguće više razine zaštite do IP 68. -40° do +40°C (moguće i više, na zahtjev) Izolirajuće tijelo RIP (smolom impregnirani papir) zaštićeno je visokokvalitetnom rebrastom poliamidnom cijevi (kvalitete PA12). Ona osigurava poboljšanje puzavosti do kraja sabirnice i omogućuje unutarnju i vanjsku primjenu. Ponašanja poliamidne cijevi ispitana su na stroge klimatske uvjete od strane neovisnih laboratorija i potvrđeno odgovaraju standardu ASTM D 2565. MGC koristi ovu zaštitnu cijev već više od 20 godina. Ukoliko se pred vanjsku zaštitnu oplatu strujnih sabirnica postavljaju posebni zahtjevi, poliamidna cijev zamjenjuje se metalnom oplatom iz CrNi čelika ili aluminija. Time se posebno povećava mehanička zaštita sabirnice. Primjena u korozivnim ili prljavijim uvjetima je sigurna. Možemo garantirati visoki životni vijek proizvoda u teškim područjima primjene.