http___lipovica.hr_radijator-solar.html_1.xml
1.1 2.1 3.1 4.1 5.1 6.1 6.2 7.1 7.2 7.3 8.1 8.2 8.3 9.1 10.1 10.2 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 18.2 19.1 20.1 20.2 21.1 21.2 22.1 22.2 22.3 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1
Radiator manufacturing program The pedestrian columns Gallery The SOLAR radiator In general SOLAR is a new generation aluminium radiator. The SOLAR radiator is the result of careful researching buyers' needs. It is exemplified by a simple and elegant shape and excellent thermal characteristics. It blends in well into any ambient and takes up very little space. Various radiator heights are available further facilitating its conformance to various requirements in areas that require heating. Once installed, your worries are over. Discrete and completely reliable, SOLAR will make sure you're feeling comfortable and warm. The radiator is made from aluminium alloy, allowing fast heat transfer and is guaranteed by an almost unlimited lifetime. SOLAR plus LIPOVICA, the leading manufacturer of die cast aluminium radiators, has always given much attention to customer needs and wants, including market trends. The results are the SOLAR+ radiators. The SOLAR+ radiators have been designed to allow simple and elegant connecting to installations carried out in the flooring or the wall, with the mountable regulation valves situated on the left or right-hand side. For each type of SOLAR radiator, there are four product versions available of the SOLAR+ products possessing the following designations: - DP – mountable valve on the right-hand side; connections for floor installations - DZ – mountable valve on the right-hand side; connections for wall installations - LP – mountable valve on the left-hand side; connections for floor installations - DZ – mountable valve on the left-hand side; connections for wall installations Each ORION+ and SOLAR+ radiator consists of two appropriate radiator sections with stop valves installed in the lower sections. These stop valves allow the radiator to be connected to or disconnected from the heating installation, and with the appropriate fitting, the radiators can be fitted to all types of piping installations. The structure provides an optimal distance of the radiator from the wall or floor. A mountable valve is located in the upper radiator hub, which on account of its design, provides a balanced system and very precise manual or automatic regulation of water flow through the radiator. The characteristics of the mountable valve can be seen in the diagram. Automatic regulation is achieved by installing a thermostat head on the mountable vent. The SOLAR+ radiators offer simple installation and straightforward connecting to appropriate radiator models. This requires two standard radiator connectors containing seals that allow SOLAR+ radiators to be connected to standard SOLAR radiators. The standard radiators are always added directly adjacent to the mountable valves. In order to gain optimal utilisation of the SOLAR+ radiators, it is recommended that the thermostat heads be installed on the mountable valves. We stress that only DANFOS thermostat heads may be installed on the mountable valves. The distance between the incoming and outgoing is 80 mm. the outgoing is the external column, whereas the external is the incoming. Technical characteristics Accessories Reduction coupling Plug ORION/SOLAR console Nipple Gasket Spacer Foot SOLAR
1.1 2.1 3.1 4.1 5.1 5.2 6.1 6.2 6.3 7.1 7.2 7.3 8.1 9.1 9.2 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 17.2 18.1 19.1 19.2 20.1 20.2 21.1 21.2 21.3 22.1 22.2 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 45.1 45.2 45.3 46.1 46.2 46.3 47.1 48.1 49.1 49.2 50.1 51.1 52.1 52.2 53.1 54.1 54.2 54.3 55.1 56.1 57.1 58.1 59.1 60.1 61.1 62.1 63.1 64.1 65.1 66.1 67.1 68.1 69.1 70.1 71.1 72.1 73.1 74.1
Proizvodni program stupića Galerije Radijator SOLAR Općenito SOLAR je aluminijski radijator nove generacije. Radijator SOLAR je rezultat pažljivog istraživanja želja kupaca. Odlikuje se jednostavnošću i elegancijom oblika te odličnim termičkim osobinama. Uklapa se u svaki ambijent i zauzima vrlo malo mjesta. U ponudi se nalaze različite visine radijatora što dodatno olakšava njegovo prilagođavanje različitim zahtjevima prostora koje treba zagrijati. Kad ga jednom ugradite, prestaje svaka Vaša briga. Diskretno i nepogrešivo, SOLAR će se pobrinuti da vam bude ugodno i toplo. Ovaj radijator zrađen je od aluminijske legure koja omogućava brzi prijenos topline i garantira gotovo neograničen vijek trajanja. SOLAR plus LIPOVICA, kao vodeći proizvođač aluminijskih lijevanih radijatora, oduvijek je veliku pozornost posvećivala potrebama i željama kupaca te kretanjima na tržištu. Rezultat takve orijentacije jesu SOLAR+ radijatori. To su radijatori modela SOLAR projektirani na način koji omogućava elegantan i jednostavan priključak na instalacije izveden u podu ili u zidu te s ugrađenim regulacijskim ventilom s lijeve ili desne strane. Za svaki tip radijatora SOLAR na raspolaganju su četiri inačice proizvoda SOLAR+ sa sljedećim oznakama : - DP - ugradbeni ventil s desne strane; priključak za instalaciju u podu - DZ - ugradbeni ventil s desne strane; priključak za instalaciju u zidu - LP - ugradbeni ventil s lijeve strane; priključak za instalaciju u podu - LZ - ugradbeni ventil s lijeve strane; priključak za instalaciju u zidu Svaki radijator Solar+ ili Orion+ sastoji se od dva odgovarajuća članka radijatora koji u donjem dijelu imaju ugrađene zaporne ventile. Navedeni zaporni ventili omogućuju priključak radijatora na instalaciju grijanja ili isključenje radijatora iz instalacije grijanja, a pomoću odgovarajućeg "fitinga" mogu se priključiti na sve vrste cijevnih instalacija. Sama konstrukcija omogućava optimalno udaljavanje radijatora od zida ili poda . U gornjoj glavčini radijatora nalazi se ugradbeni ventil koji zahvaljujući svojoj konstrukciji omogućava balansiranje sustava i vrlo preciznu ručnu ili automatsku regulaciju protoka vode kroz radijator. Karakteristike ugradbenog ventila mogu se vidjeti na dijagramu. Automatska regulacija postiže se ugradnjom termostatske glave na ugradbeni ventil . SOLAR+radijatori odlikuju se jednostavnom ugradnjom i jednostavnim spajanjem na odgovarajući tip radijatora. Za to su potrebne dvije obične radijatorske spojnice sa brtvama pomoću kojih se SOLAR+ radijatori spajaju sa standardnim Solar radijatorima. Standardni radijator dodaje se uvijek nasuprot ugradbenom ventilu. Zbog optimalnog iskorištenja Solar+ radijatora preporuča se ugradnja termostatske glave na ugradbeni ventil. Napominjemo da je na ugradbeni ventil moguća montaža isključivo DANFOS termostatske glave. Razmak polaza i povrata je 80mm. Polaz je vanjski članak, unutarnji je povrat. Tehničke karakteristike Pribor Redukcije Čep Konzola ORION/SOLAR Spojnica Brtva Distančnik Nogica SOLAR Cijena Cijene su bez PDV- a, informativnog karaktera. Za sve ostale detalje molimo da se obratite u službu prodaje, tel. 044/569-130. Upute POŠTOVANI ! Za grijanje vašega doma odabrali ste radijator LIPOVICA čime ste odabrali kvalitetu , trajnost, pouzdanost i vrhunski dizajn. Stoga vas molimo da pri samoj kupnji pregledate i ustanovite da je proizvod neoštećen , a svoju eventualnu primjedbu iznesete prodavaču. Da bi proizvod besprijekorno radio te da bi njegova upotreba bila dugotrajna i pouzdana pažljivo proučite uvjete garancije, te upute za instaliranje , rad i održavanje radijatora. UPUTA ZA MONTAŽU Poznata je prednost člankastih aluminijskih radijatora da se mogu lagano sastaviti i rastaviti na bilo kojem mjestu ovisno o vašoj potrebi i želji. Ako niste dovoljno obučeni za montažu radijatora preporučamo da to prepustite stručnim i ovlaštenim osobama koje se bave instalacijom i montažom grijanja odnosno radijatora. Pod uvjetom da ste odabrali tip radijatora i napravili proračun potrebnog broja članaka za vaš prostor, možete pristupiti montaži koju trebate izvesti isključivo prema preporuci proizvođača koja obuhvaća sljedeće zahtjeve: 1.Prilikom montaže radijatora koristiti isključivo konzole Lipovica ili adekvatne (vidi skicu za montažu), koje omogućuju tih i nesmetan rad radijatora. 2.Brtvila koja upotrebljavate prilikom spajanja dodatnih elemenata na bateriju (članci, redukcije ) moraju biti isključivo proizvod Lipovice ili iste kvalitete(otporne na antifriz, mineralna ulja i sl.) . Nisu potrebna nikakva dodatna sredstva (masti , paste i sl.) jer se i bez tih sredstava osigurava učinkovit rad. Nepridržavanje dovodi do neželjenog propuštanja medija i oštećenja boje. Obavezno korištenje redukcija i spojnica Lipovica ili adekvatnih. Samo te spojnice i redukcije garantiraju jednostavnu montažu i siguran rad. Ako se prilikom montaže, spojnice i redukcija ne mogu zavrnuti rukom treba obratiti pozornost na onečišćenje navoja jer će u protivnome doći do oštećenja istoga. 4.Prilikom sastavljanja članaka potrebno je ostvariti i odgovarajući moment zatezanja od min. 40 Nm. 5.Radijatorsku bateriju nikako ne postavljati u neposrednoj blizini izvora koji svojim agresivnim kemijskim djelovanjem mogu dovesti do oštećenja boje. 6.Postojeću zaštitnu foliju i bočne kartonske poklopce ne skidati dokle god traju radovi u prostoru, jer time onemogućavate oštećenja boje i druge neželjene posljedice. Bilo bi poželjno i da sačuvate bar kod naljepnicu koja se nalazi na ambalaži sa svim podacima o proizvodu. Preporučen broj konzola na broj članaka u bateriji UPUTA ZA RAD Sistem se puni običnom vodom uz eventualni dodatak sredstava protiv smrzavanja , pazeći pri tome da pH otopine bude u granicama 7- 9,5. Preporučena tvrdoća demineralizirane vode 0-4 º DH. Kada sistem grijanja nije u stalnom radu, a vanjska temperatura padne ispod -5 ºC, voda u sistemu se može smrznuti , a radijatori popucati. Ne preporučuje se česta izmjena vode (medija) u sistemu (jednom napunjeni sistem se samo nadopunjava). Preporučeni radni tlak je 1-3 bara. Za određena tržišta (Rusija, Ukrajina itd.) isporučujemo radijatore s radnim tlakom 16 bara. uz max temperaturu vode od 110 ºC što znači da sustav grijanja mora obavezno sadržavati sigurnosni ventil koji će onemogućiti porast pritiska i oštećenje proizvoda bilo u vrijeme sezone ili van sezone grijanja. U vrijeme kada sistem grijanja nije duže u upotrebi (van sezone grijanja) ne zatvarati ventile na bateriji jer može zbog dilatacijskih procesa doći do neželjenih posljedica (puknuća članaka u bateriji). Šumovi i žuborenja koji se mogu javiti u tijeku rada isključivo su uzrok prisutnosti zraka u sistemu pa je dobro povremeno nadzirati pritisak i vršiti ispuštanje zraka iz sistema kako bi se omogućio optimalan rad radijatora. UPUTA ZA ODRŽAVANJE Proizvode prije montaže treba skladištiti u suhim prostorima bez direktne izloženosti sunčevoj svjetlosti. Proizvode treba čistiti neagresivnim i neabrazivnim čistilima (meka krpa). Za čišćenje prašine između članaka koristiti za to primjenjive četke. Radijator treba biti uvijek napunjen vodom ,a zrak ispušten iz sistema. Garancijska izjava IZJAVLJUJEMO: Da je proizvod izrađen u skladu sa propisima Europske norme E 442 koja regulira tehničke specifikacije i zahtjeve za radijatore i izmjenjivače topline te da će radijatori Lipovica besprijekorno raditi u garancijskom roku pod uvjetom da se koristi u skladu s njegovom namjenom i uputama za montažu , rad i održavanje. Da ćemo na Vaš zahtjev, u dogovoru sa Vama, besplatno otkloniti eventualni nedostatak na proizvodu u najkraćem mogućem roku od trenutka prijave kvara. Garancija neće vrijediti u sljedećim slučajevima: - Ako se ne pridržava uputa za montažu, rad i održavanje - Ako se prilikom montaže koriste neoriginalni rezervni dijelovi i pribor - Za kvarove i oštećenja nastala zbog nestručnog i nebrižljivog rukovanja sa proizvodom - Ako nije priložen potvrđen garancijski list, kao i račun o kupnji proizvoda. Kupac može reklamaciju prijaviti neposredno prodavaču prilikom kupnje ili proizvođaču nakon ugradnje odnosno početka rada u garancijskom roku od 20 godina. Za ugrađeni ventilski sklop na radijatorima Orion + i Solar + jamstvo je 18 mjeseci.