http___mgc.com.hr_proizvodi_tiresca-sabirnice__1.xml
1.1 1.2 2.1 2.2 2.3 2.4 2.5 2.6 2.7 3.1 3.2 3.3 3.4 3.5 4.1 5.1 5.2 6.1
The direct attached TIRESCA® insulation consists of a vacuum cast epoxy resin. On the whole lenght of... The direct attached TIRESCA® insulation consists of a vacuum cast epoxy resin. On the whole lenght of the bar, the insulation is covered with a corrugated polyamide protection tube. This tube provides an effective barrier against moisture ingress, a good protection against shocks and is UV radiation resistant (tested according to ASTM D 2565). The selected quality authorizes as well an indoor or outdoor use. The single bars are manufactured in lenghts up to 10 meters. For longer bus runs or by tight place conditions where only short pieces can be installed, the single busbars are joined together on site. The conductor is made up of a cylindrical aluminium alloy type EN AW-6101B T7, or of an electrolytic copper E Cu ETP H. The TIRESCA® busbars, type TEL, are fully insulated within the range up to 3,6 kV. The TIRESCA® busbars, type TE, are partially insulated and designed for MV applications in indoor or outdoor switchyards. They offer a protection against short circuits from phase to earth and phase to phase caused by small animals, branches or other objects. An additional feature is to reduce the distances between the phases, to minimise the required space when limited. The type TE is mounted on support insulators with clamp. Each individual busbar is being tested according to an electrical routine test in our factory Busbars: IP 67. Connecting sleeves: IP 54 as standard or IP 68 as an option -40° do +40°C (other on request)
1.1 2.1 2.2 2.3 2.4 2.5 2.6 3.1 4.1 4.2 4.3 4.4 5.1 6.1 6.2 7.1
TIRESCA® izolacija sastoji se od epoksidne smole koja se ulijeva pod vakuumom i zaštićuje omotačem... TIRESCA® izolacija sastoji se od epoksidne smole koja se ulijeva pod vakuumom i zaštićuje omotačem od valovite poliamidne cijevi. Valovita cijev štiti sabirnicu od mehaničkih oštećenja, prodora vlage i otporna je na atmosferilije i UV zračenje (testirano po ASTM D2565). Kvalitetna valovita cijev omogućuje uporabu sabirnice u zatvorenim i na otvorenom prostoru. Vodič se izrađuje od okrugle šipke ili cijevi, kao materijal koristi se aluminijska legura EN-AW-6101B T7 ili elektrolitni bakar ETP H. Pojedinačne sabirnice proizvode se u duljinama do 10m. Duljina i broj sabirnica jednog voda ovisi o dostupnom prostoru na mjestu montaže. Potpuno izolirani TIRESCA® strujni sustav tip TEL koristi se u području do 3,6 kV. Djelomično izolirani TIRESCA® strujni-sustav tip TE koristi se na unutrašnje-vanjskim postrojenjima u području srednjih napona. Izvedba tip TE nudi zaštitu postrojenja od izbijanja kratkog spoja prema zemlji i između faza, malih životinja i grana, kao i drugih objekata. Nadalje, omogućuje smanjenje minimalnih razmaka između sabirnica u skučenim prostorima. Tip TE ugrađuje se na nosivie izolatore sa obujmicama. Svaka pojedinačna sabirnica rutinski se električno ispituje u našoj tvornici Strujne sabirnice = IP 67. Izolirajuće navlake i zaštitna kućišta standardno IP 64, opcionalno su moguće više razine zaštite do IP 68. -40° do +40°C (moguće i više, na zahtjev)