http___www.imi-hydronic.com_hr_products-solutions_Thermostatic-control_Termostati-i-pogoni_Termostati_Termostat-E__1.xml
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 7.2 8.1 9.1 9.2 10.1 11.1 11.2
Electronic room temperature controller for proportional and three-point actuators The constantly operating and three-point thermostatic room temperature controllers E 1 or E 3 respetively in conjunction with the corresponding actuators are employed in the field of heating, aerating and air condition engineering. Especially in those cases where elevated requirements for an accurate temperature control or a controlled system of high degrees of difficulty pevail opitmal control results can be achieved. Technical description The Thermostats E 1 and E 3 are micro-processor-operated electronic room temperature controllers with incorporated sensors and adjustab PI control behaviour. The Thermostat E 1 with constant control behaviour (0 – 10 V) allows connecting proportionally operating motorized actuators, e.g. EMO 1 or EMO TM. The Thermostat E 3 with a three-point output signal will be used in conjunction with three-point motorized actuators such as e.g. EMO 3 or in case of a puls-width modulated output signal (PWM) with two-point actuators, e.g. EMO T or EMOtec. The setting value is adjustable between 10° and 30°C. An upper or lower limitation of the setting value range can be effected by arranged hidden stops. A"presence" push-button allows during heating mode, e.g. a room temperature set back by 4 K. Control lights indicate the operating mode such as "presence" and heating or cooling. Two inputs for potential-free normally open (n/o) contacts allow connecting, for the temperature set back (X1), an external timing clock or for the purpose of a change-over from heating to cooling mode (c/o) an external switch respectively. There are further connecting possibilities for an external temperature sensor (Text), dew point detector (TP) and for a setting value shift (w). The thermostatic controllers E 1 and E 3 are designed for an installation on a wall or on a recessed (concealed) socket. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 3.1 4.1 5.1 5.2 6.1 6.2 6.3 7.1 7.2 7.3 7.4 7.5 7.6 8.1 9.1 9.2
Elektronički regulator temperature prostorije za proporcionalne i tropoložajne pogone Elektronički regulator temperature prostorije za proporcionalne i tropoložajne pogone, koriste se u sustavima grijanja i klimatizacije. Tehnički opis Termostati E 1 i E 3 su mikroprocesorski upravljani elektronički regulatori temperature prostorije s ugrađenim senzorima i podesivim PI regulacijskim ponašanjem. Termostat E 1 s konstantnim regulacijskim ponašanjem (0 - 10 V) omogućava priključak proporcionalnih pogona s motornim pogonom, npr. EMO 1 ili EMO TM. Termostat E 3 s 3-položajnim izlaznim signalom koristi se u spoju s 3-položajnim pogonima s motornim pogonom, kao što je npr. EMO 3 ili u slučaju izlaznog signala (PWM) moduliranog po širini simbola, s 2-položajnim pogonima, npr. EMO T ili EMOtec. Vrijednost namještanja podesiva je između 10° i 30°C. Gornje ili donje ograničenje područja vrijednosti namještanja može se izvesti raspoređenim uvučenim graničnicima. Pritisni gumb „prisutnosti“ tijekom režima grijanja omogućava npr. zadršku temperature prostorije za 4 K. Kontrolne lampice pokazuju radno stanje, kao što je „prisutnosti“ i grijanje ili hlađenje. Dva ulaza za bespotencijalno normalno otvorene (n/o) kontakte omogućavaju spajanje za temperaturnu zadršku (X1), vanjski uklopni sat s vremenskim programatorom ili vanjsku sklopku u svrhu prespajanja sa režima grijanja na režim hlađenja (c/o). Postoje daljnje mogućnosti spajanja za vanjski senzor temperature (Text), detektor temperature rosišta (TP) i za pomak namještene vrijednosti (w). Termostatski regulatori E 1 i E 3 predviđeni su za instaliranje na zid ili na uvučenu (zaklonjenu) utičnicu. Proizvodi, tekstovi, fotografije, crteži i dijagrami u ovoj brošuri podložni su promjenama od strane IMI Hydronic Engineering, bez prethodne obavijesti ili obrazloženja. Za više informacija o proizvodima i specifikacijama molimo posjetite nas na www.imi-hydronic.com.