http___www.imi-hydronic.com_hr_products-solutions_Balancing-and-control_Regulatori-diferencijalnog-tlaka_Regulatori-diferencijalnog-tlaka_STAP-DN-65-100__1.xml
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 13.1 15.1 15.2 16.1 17.1 18.1 20.1 21.1 21.2 22.1 22.2 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 43.2
Differential pressure controller The flanged STAP is a high-performing differential pressure controller that keeps the differential pressure over the load constant. This delivers accurate and stable modulating control, ensures less risk of noise from control valves, and results in easy balancing and commissioning. STAP’s unrivalled accuracy and compact size make it particularly suitable for use on the secondary side of heating and cooling systems. Technical description Application: Heating (not steam) and cooling systems. Function: Differential pressure control Adjustable Ap Measuring points Shut-off Dimensions: Pressure class: Max. differential pressure (ApV): 350 kPa (117 ft H2O/51 PSI) Setting range: 20-80 kPa resp 40-160 kPa. Temperature: Max. working temperature: 120°C Min. working temperature: -10°C Material: Valve body: Ductile iron EN-GJS-400-15 (~ASTM A536 Grade 60-40-18, ISO 1083 Grade 400-15) Bonnet: AMETAL® Cone: AMETAL® Spindles: AMETAL® O-rings: EDPM rubber Seat seal: Plug with EPDM O-ring Membrane: Reinforced EPDM rubber Spring: Stainless steel Handwheel: Polyamide AMETAL® is the dezincification resistant alloy of IMI Hydronic Engineering. Surface treatment: Valve body: Epoxy painting. Marking: Body: TA, Class 150, DN, CE, ASTM 60-40-18, flow direction arrow and casting date (year, month, day). Bonnet and handwheel: Label with STAP, DN, PN, ApL in Ft H2O, PSI and kPa, and bar code. Face to face: ISO 5752 series 1 and EN 558-1 series 1. Flanges: Class 150 according to ASME/ANSI B16.42 (~ PN 20 according to ISO 7005-2). The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 13.1 15.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 43.1 43.2
Regulatori diferencijalnog tlaka - DN 65-100 Prirubnički STAP je regulator diferencijalnog tlaka, visoke učinkovitosti, koji tijekom opterećenja održava konstantni diferencijalni tlak. Omogućava precizno i stabilno modulacijsko upravljanje, jamči manje razvijanje šumova od regulacijskih ventila, što rezultira nenadmašnom preciznošću te jednostavnim balansiranjem i puštanjem u rad STAP regulacijskih ventila, kao i kompaktnom veličinom i čini ih posebno prikladnim za primjenu na sekundarnom dijelu sustava grijanja i hlađenja. Tehnički opis Primjena: Sustavi grijanja i hlađenja. Funkcije: Regulacija diferencijalnog tlaka Podesivi Ap Mjerni priključci Zaporna funkcija Dimenzije: Razred tlaka: Max. diferencijalni tlak (ApV): Područje podešavanja: 20* - 80 kPa odnosno 40* - 160 kPa. *) Tvorničko podešavanje Temperatura: Max. radna temperatura: 120°C Min. radna temperatura: -10°C Materijal: Kućište ventila, Sivi lijev EN-GJL-250 (GG-25) Kapa vretena: AMETAL® Konus AMETAL® Vretena: AMETAL® O-brtveni prsteni: EPDM guma Brtva sjedišta ventila: Čep s EPDM O-brtvenim prstenom Membrana: Armirana EPDM guma Opruga: Nehrđajući čelik Ručno kolo: Poliamid AMETAL® je IMI Hydronic Engineering legura otporna na decinifikaciju. Površinska zaštita: Kućište ventila: Epoksidna boja. Označavanje: Tijelo ventila: TA, PN 16, DN, CE, 250 Cl, strelica smjera strujanja i datum lijevanja (godina, mjesec, dan). Kapa vretena i ručno kolo: Naljepnica sa STAP, DN, ApL 20-80 odnosno 40-160 kPa i barkod. Dužina od čela do čela: ISO 5752 serije 1, BS 208 Prirubnice: Proizvodi, tekstovi, fotografije, crteži i dijagrami u ovoj brošuri podložni su promjenama od strane IMI Hydronic Engineering, bez prethodne obavijesti ili obrazloženja. Za više informacija o proizvodima i specifikacijama molimo posjetite nas na www.imi-hydronic.com.