http___www.imi-hydronic.com_hr_products-solutions_Thermostatic-control_Termostati-i-pogoni_Termostati_Termostat-P__1.xml
1.1 2.1 2.2 3.1 4.1 4.2 5.1 5.2 5.3 5.4 5.5 5.6 6.1 6.2 7.1 7.2 7.3 7.4 7.5 8.1 9.1 9.2
Electronic room thermostat with clock for thermal actuators The Thermostat P room temperature controller is used in connection with the corresponding actuators in the fields of heating, ventilation and air-conditioning technology. For time-dependent individual room temperature control, the Thermostat P is used for e. g. residential and commercial buildings with radiators, floor heating systems, ceiling cooling systems or blower convectors etc.. Technical description The Thermostat P is an electronic two-point room thermostat with built-in sensor and is used in connection with e. g. thermal actuators for time-dependent room temperature control with operating modes "only heating" or "only cooling". With its pulsewidth modulation output signal (PWM), it has an almost constant control behaviour, internally adjustable on two-point output signal. The model with analog switch clock makes it possible to create a weekly program by positioning the switch tabs. Depending on the program, it switches between two operating modes, (day mode and night mode). The corresponding setting value can be set between 5 °C and 30 °C. An operating mode switch makes it possible to select between day, night or automatic mode. The model has control lamps for the heating, cooling or night mode operating state. With a separate switch clock output, additional room temperature controllers with temperature set-back inputs can be controlled. The models with digital switch clock are menu-driven via four buttons. The display shows the current room temperature, time and operating modes. The internal real-time clock is equipped with an automatic daylight saving. Time programs with weekly or daily program. Three time programs are preset and changeable. The temperature is adjustable between 7 ° C and 32 ° C. The temperature is achieved due to the self-learning heating curve at the selected time. Models with 230 V or 24 V operating voltage or for battery operation, each with potential-free changeover contact. The Thermostat P is designed for installation on the wall or on recessed (concealed) switch boxes. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 3.1 4.1 4.2 5.1 5.2 5.3 5.4 5.5 5.6 6.1 6.2 6.3 6.4 6.5 6.6 6.7 6.8 7.1 8.1 8.2
Elektronički regulator temperature prostorije s uklopnim satom, za termičke pogone Termostat P primjenjuje se u kombinaciji s pogonima na polju grijanja, ventilacije i klimatizacije. Termostat P može se koristiti i za regulaciju sobne temperature s vremenskim podešavanjem u stanovima, uredskim prostorima grijanim radijatorima ili podnim grijanjema. Tehnički opis Termostat P je elektronički 2-položajni sobni termostat s ugrađenim senzorom i koristi se u spoju s npr. termičkim pogonima za regulaciju temperature prostorije vođenu vremenom, s režimima rada „samo grijanje“ ili „samo hlađenje“. Sa svojim izlaznim signalom moduliranim po širini impulsa (PWM), on ima gotovo konstantno regulacijsko ponašanje, interno je podesiv na 2-položajni izlazni signal. Model s analognim uklopnim satom omogućava kreiranje tjednog programa, pozicioniranjem uklopnih tipki. Ovisno od programa, on prespaja između dva režima rada (dnevni režim i noćni režim). Odgovarajuća podešena vrijednost može se namjestiti između 5 °C i 30 °C. Prekidač režima rada omogućava biranje između dnevnog, noćnog ili automatskog režima rada. Termostat ima kontrolne lampice za grijanje, hlađenje ili stanje noćnog režima rada. Sa zasebnim izlazom uklopnog sata može se upravljati dodatnim regulatorima temperature prostorije, s ulazima temperaturne zadrške. Modeli s digitalnim uklopnim satom vođeni su menijem pomoću četiri gumba. Na displeju se pokazuje trenutačna temperatura prostorije, vrijeme i režimi rada. Interni sat realnog vremena opremljen je s automatskom uštedom za dnevnog svjetla. Vremenski programi s tjednim ili dnevnim programom. Tri vremenska programa prethodno su podešena i mogu se promijeniti. Temperatura je podesiva između 7 °C i 32 °C. Temperatura se postiže zahvaljujući krivulji grijanja za odabrano vrijeme. Modeli s 230 V ili 24 V radnog napona ili za rad na baterije, svaki s bespotencijalnim preklopnim kontaktom. Termostat P namijenjen je za instaliranje na zid ili na uvučene uklopne kutije. Proizvodi, tekstovi, fotografije, crteži i dijagrami u ovoj brošuri podložni su promjenama od strane IMI Hydronic Engineering, bez prethodne obavijesti ili obrazloženja. Za više informacija o proizvodima i specifikacijama molimo posjetite nas na www.imi-hydronic.com.