http___www.imi-hydronic.com_srb-rs_products-solutions_Balansiranje_i_kontrola_Regulaciioni-ventili-i-Pogoni_Kombinovani-kontrolni-i-balansni-ventili-za-male-terminalne-potroae_TA-COMPACT-T__1.xml
1.1 2.1 2.2 2.3 2.4 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 14.1 16.1 17.1 18.1 19.1 20.1 20.2 21.1 21.2 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 40.1 41.1 42.1 42.2
Control valve with return temperature controller for cooling systems TA-COMPACT-T is an On/Off control valve with built-in return temperature controller that guarantees requested return temperature from terminal units in cooling systems. Correct return temperature increases energy efficiency of the entire system and helps to protect chillers against low temperature. Hydronic balancing by means of return temperature control limits overflows and provides energy savings. A measuring point makes temperature measuring possible. Technical description Applications area: Cooling systems with variable flow. Installation in return pipe. Functions: Control Return temperature control Temperature measuring Shut-off Dimensions: Pressure class: Temperature range: Return temperature: 8°C - 18°C Delivery setting: 12°C Temperature: Max. working temperature: 50 °C Min. working temperature: -10 °C Media: Water or neutral fluids, water-glycol mixtures. (For other media contact IMI Hydronic Engineering.) Lift: 4 mm Materials: Valve body: Corrosion resistant gunmetal O-rings: EPDM rubber Valve seat gasket: EPDM rubber Return spring: Stainless steel Valve inserts: Brass Spindle: Niro-steel spindle with double O-ring sealing. Handwheel: ABS Marking: TAH, PN 16, DN and flow direction arrow. Black protection cap. Connection to actuator: Actuators: See separate information on EMO T. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 2.4 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 14.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 40.1 41.1 42.1 42.2
Kontrolni ventil sa regulatorom povratne temperature za rashladne sisteme TA-COMPACT-T je on/off kontrolni ventil sa ugrađenim regulatorom povratne temperature koji osigurava zahtevanu povratnu temperaturu iz terminalnih jedinica u rashladnim sistemima. Pravilno podešena povratna temperatura zadržava visoku efikasnost celog sistema i štiti čilere od sindroma niske povratne temperature. Hidronično balansiranje bazirano na osnovu regulacije povratne temperature ograničava protoke i pruža uštedu energije. Merni nipl omogućava merenje temperature. Tehnički opis Namena: Rashladni sistemi sa promenljivim protokom. Ugradnja na povratnoj cevi. Funkcija: Kontrola Regulacija povratne temperature Merenje temperature Zatvaranje Dimenzije: Nazivni pritisak: Temperaturni opseg: Povratna temperatura: 8°C - 18°C Fabrički predpodešena vrednost: 12°C Temperatura: Max. radna temperatura: 50°C Min. radna temperatura: -10°C Radni fluid: Voda ili neutralne tečnosti, mešavine vode i glikola. (za ostale radne fluide kontaktirati IMI Hydronic Engineering.) Hod: 4 mm Materijal: Kućište: Na koroziju otporna legura bakra O-rings: EPDM Zaptivka sedišta ventila: EPDM Povratna opruga: Nerđajući čelik Uložak ventila: Mesing Vreteno: Čelično vreteno sa duplim O-ring zaptivanjem. Ručica: ABS Oznaka: TAH, PN 16, DN i strelica smera strujanja. Crna šatitna kapa. Priključak za pogon: Pogoni: Pogledajte više informacija u EMO T-u. Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.