http___www.imi-hydronic.com_srb-rs_products-solutions_Balansiranje_i_kontrola_Balansni-ventili_Balansni-ventili_STAF-R__1.xml
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 12.1 13.1 14.1 15.1 15.2 16.1 17.1 18.1 19.1 20.1 21.1 22.1 22.2 23.1 23.2
Compression coupling for PEX-pipes High-performing and flexible compression coupling for PEX pipes in heating, cooling and tap water systems. Available in a comprehensive Dy range of 12-63 mm – enabling faster installation – as well as a wide range of sizes. Technical description Applications: Heating and cooling systems. Tapwater systems. Process systems where the media does not affect the incoming material. Function: FPL-PX compression coupling for PEX pipes. Dimensions: Pressure class: PN 6/PN 10 or the pipe pressure. Temperature: Max. working temperature: 95°C or the pipe pressure. Material: Parts which are subject to water contact: AMETAL® Allen screws and lockring: Stainless steel O-rings (40-63 mm): EPDM rubber AMETAL® is the dezincification resistant alloy of IMI Hydronic Engineering. Surface treatment: Delivered as non-plated (yellow) or surface treated (chrome/nickle plated). See each product table. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 14.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 31.2
Balansni ventil – PN 16 (DN 65-150) – Bronza Prirubnički ventil od bronze sa izuzetnim hidrauličkim performansama i impresivnim opsegom primene. STAF-R je idealan za upotrebu u intstalacijama grejanja i hlađenja i sistemima potrošne vode. Tehnički opis Namena: Sistemi grejanja i hlađenja Sistemi potrošne vode Funkcija: Balansiranje Predregulacija Merenje Zatvaranje (izbalansirano vreteno za ventile) Dimenzije: Klasa pritiska: Temperatura: Max. radna temperatura: 120°C Ako su Vam potrebni ventili za veće max. radne temperature (max.150°C), molimo kontaktirajte IMI Hydronic Engineering. Min. radna temperatura: -20°C Materijal: Kućište: Bronza CuSn5Zn5Pb5 Pečurka, poklopac i vreteno: AMETAL®. Zaptivka na sedištu: Vreteno sa EPDM prstenom Zatvarač na poklopcu: Hromirani čelik Ručica: Poliamid AMETAL® je legura otporna na koroziju i zaštićena od strane IMI Hydronic Engineering. Označavanje: Kućište: TA, PN, DN, CE, strelica za smer proticanja, materijala i datum livenja (godina, mesec, dani). Licem u lice: ISO 5752 serija 1, BS 2080 i EN 558-1 serija 1. Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.