http___www.imi-hydronic.com_srb-rs_products-solutions_Balansiranje_i_kontrola_Regulatori-diferencijalnog-pritiska_Regulatori-diferencijalnog-pritiska_TA-PILOT-R__1.xml
1.1 2.1 2.2 2.3 3.1 4.1 5.1 5.2 6.1 7.1 7.2 7.3 7.4 8.1 9.1 9.2 9.3 10.1 11.1 11.2 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 19.2 20.1 20.2 21.1 22.1 22.2 23.1 23.2 24.1 25.1 25.2 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 37.2
Dirt and magnetite separator with Cyclonic technology Comprehensive range of products for sludge and magnetite separation in heating and cooling water systems. The number of potential applications as well as their modular construction is unique. Its new cyclonic technology takes dirt separation efficiency to the next level Key features High separation efficiency with Cyclonic technology Cleans your system in fewer cycles, each time reducing dirt particles that would normally deposit in the system with each additional cycle. The dirt collected can be easily and quickly flushed out with the help of the drain valve. High efficiency independent of dimension Dirt separator efficiency increases as flow velocity increases. The pressure drop remains stable during operation regardless of the amount of dirt collected. Even higher protection for higher flows, e.g. in cooling applications. Suitable for heating and cooling installations. Cleans and protects the installation Protects critical investments from malfunction and even failure due to dirt, such as boilers, pumps, valves, chillers, and calorie meters. No clogging risk. Reduces maintenance of equipment needed over system lifetime and associated costs. Magnet Accessory Optimizes separation efficiency even further for sludge and magnetite (black iron oxide) deposits which consist of finer magnetic particles. Easy handling and cleaning. Technical description Application: Heating and chilled water systems. Media: Non-aggressive and non-toxic system media. Addition of antifreeze agent up to 50%. Pressure: Max. admissible pressure, PS: PN 16 Min. admissible pressure, PSmin: 0 bar Temperature: Max. admissible temperature, TS: 110 °C Min. admissible temperature, TSmin: -10 °C Material: Steel. Color beryllium. Marking: Body: flow direction arrow. Label: DN, PN, TS and TSmin. Connection: Flanges according to EN 1092-1. Welding ends. Grooved ends. Transportation and storing: In dry places. Approvals: Constructed according to PED/DEP 97/23/EC. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 2.4 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 20.1 21.1 22.1 24.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 61.1 62.1 63.1 64.1 65.1 65.2
Regulator diferencijalnog pritiska upravljan Pilot ventilom sa podesivim vrednostima TA-PILOT-R je regulator diferencijalnog pritiska visokih perfomansi konstruisan da održava stabilan diferencijalni pritisak na opterećenju. Sa vrhunskom tačnošću TA-PILOT-R pruža precizne i stabilne uslove za superiorni autoritet modulovano kontrolisanih kontrolnih ventila, dodatno on ograničava buku i pojednostavljuje balansnu proceduru. TA-PILOT-R je regulator diferencijalnog pritiska koji se instalira na povratni cevovod. Merni niplovi omogućuju merenje pritiska u cilju dijagnostike. Ključne karakteristike Jednostavno rukovanje i ugradnja Vrlo mala težina i mala ukupna dimenzija ventila. Precizna i stabilna regulacija diferencijalnog pritiska Neprevaziđena tačnost zahvaljujući novoj PILOT tehnologiji. Merenje i dijagnostika sistema Jedinstvene karakteristike za validaciju i bolje razumevanje ponašanja sistema za smanjenje potrošnje energije. Tehnički opis Namena: Sistemi grejanja i hlađenja. Ugradnja na povratnoj cevi. Funkcija: Regulacija diferncijalnog pritiska Predregulacija Ap na opterećenju (ApL) Merenje (ApL) Dimenzije: Klasa pritiska: PN 16 i PN 25 Maksimalni diferencijalni pritisak (ApV): Područje podešavanja: *) Fabrički podešene vrednosti Veličina propuštanja: Nepropusno zatvaranje Temperatura: Maksimalna radna temperatura: - sa mernim niplovima, standardna verzija: 120°C - sa mernim niplovima, dvostruko obezbeđenim: 150°C Min. radna temperatura: -20°C Radni fluid: Voda ili neutralne tečnosti, mešavine vode i glikola. (za ostale radne fluide kontaktirati IMI Hydronic Engineering.) Materijal: Kućište ventila: Nodularni liv EN-GJS-400 Kućište Pilot-a: AMETAL® O-rings: EDPM Zaptivka sedišta ventila: EPDM/Nerđajući čelik Mehanizam vretena ventila: Nerđajući čelik i mesing Membrana: EPDM Opruge: Nerđajući čelik Vijci i navrtke: Nerđajući čelik AMETAL® je legura otporna na koroziju i zaštićena od strane IMI Hydronic Engineering. Obrada površine: Kućište Pilot-a: Nije tretirano. Kućište ventila: elektroforetsko bojenje. Označavanje: TA, IMI, DN, PN, Kvs, Tmin/max, serijski broj, materijal kućišta ventila i strelica smera strujanja, nalepnica, ApL opseg. Identifikacija boje na vrhu pilota: 10-50 kPa: Plava 30-150 kPa: Narandžasta 80-400 kPa: Siva CE-označavanje: *) Označeno na kućištu. Prirubnice: PN 16, PN 25: Prirubnice prema EN-1092-2, tipa 21. Razmak čeonih površina, prema EN 558 serija 3. Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.