http___www.imi-hydronic.com_ba_products-solutions_Balancing-and-control_Regulacijski-ventili_Balansirajui-i-regulacijski-ventili_TA-COMPACT-P__1.xml
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 23.1 25.1 26.1 26.2 27.1 28.1 28.2 29.1 30.1 31.1 32.1 32.2 32.3 33.1 34.1 35.1 36.1 36.2 37.1 38.1 40.1 41.1 41.2 42.1 42.2 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 59.1 60.1 61.1 62.1 63.1 64.1 65.1 66.1 67.1 68.1 69.1 71.1 72.1 73.1 73.2
For small pressure independent circuits The TA-COMPACT-DP is the ideal solution for zone control of small circuits, enables setting of max. flow and prevent control valves from too high differential pressure. TA-COMPACT-DP combines 5 functions: differential pressure control, balancing, control, diagnostics and shut-off. Key features 5 in 1 concept reduces costs Installing one valve with 5 functions reduces investment costs and installation time. Saves energy and money Balanced and pressure independent circuits protects systems against over flows and too high energy consumption. Zone control Time controlled circuits can save up to 20% energy. Noise protection Differential pressure control protects control valves from too high differential pressure. Technical description Application: Heating and cooling systems. Functions: Pre-setting (max. flow) Differential pressure control Control Measuring (AH, T, q) Shut-off (for isolation during system maintenance – see also Leakage rate) Dimensions: Pressure class: Differential pressure (AH): Max. differential pressure (AHmax): 400 kPa = 4 bar Min. differential pressure (AHmin): DN 15: 18 kPa = 0,18 bar DN 20: 21 kPa = 0,21 bar DN 25: 25 kPa = 0,25 bar (Valid for the most demanding settings. Other settings will require a lower AH. Check with graphs under "Sizing" or software HySelect.) AHmax = The maximum allowed pressure drop over the circuit, to fulfill all stated performances. AHmin = The minimum needed pressure drop over the circuit, for proper differential pressure control. Setting range: Indication of recommended setting range. For more detailed information see "Sizing". DN 15: ApL 10 kPa, 60-300 l/h DN 20: ApL 10 kPa, 160-840 l/h Temperature: Max. working temperature: 90°C Min. working temperature: -10°C Media: Water or neutral fluids, water-glycol mixtures. Lift: 4 mm Leakage rate: Leakage flow ≤ 0,01% of max. recommended flow (setting 10) in correct flow direction. (Class IV according to EN 60534-4). Characteristics: Linear, best suited for on/off control. Material: Valve body: AMETAL® Valve insert: AMETAL® Valve plug: Stainless steel Spindle: Stainless steel Spindle seal: EPDM O-ring Ap insert: AMETAL®, PPS (polyphenylsulphide) Membrane: EPDM and HNBR Springs: Stainless steel O-rings: EPDM AMETAL® is the dezincification resistant alloy of IMI Hydronic Engineering. Marking: TA, IMI, PN 16, DN and flow direction arrow. Grey handwheel: TA-COMPACT-DP and DN. Connection: Male thread according to ISO 228. Connections (accessories) with female and male threads NPT according to ANSI/ASME B1.20.1-1983, or for soldering according to ASME/ANSI B16.18. Connection to actuator: Actuators: See separate information on EMO T. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 23.1 25.1 26.1 27.1 30.1 30.2 31.1 32.1 33.1 34.1 36.1 41.1 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 51.1 51.2 52.1 53.1 54.1 55.1 56.1 57.1 58.1 59.1 60.1 61.1 62.1 63.1 64.1 65.1 66.1 67.1 67.2 68.1 69.1 70.1 72.1 73.1 74.1 74.2
Regulacijsko balansirajući ventil neovisan o promjeni dinamičkog tlaka (PIBCV) Regulacijsko balansirajući ventil neovisan o promjeni dinamičkog tlaka TA-COMPACT-P osigurava optimalne perfomanse u dugom vremenskom periodu. Podesiva vrijednost maksimalnog protoka omogućava projektirani protok i spriječava prekoračenje protoka za preciznu hidroničku kontrolu. TA-COMPACT-P zajedno s našim mjernim uređajima omogućava napredno mjerenje i dijagnostiku. Glavne značajke Precizno hidroničko balansiranje Fino podesive vrijednosti maksimalnog protoka spriječavaju prekoračenje protoka kroz potrošače. Ugradnja bez ograničenja Uski i kompaktni oblik pojednostavljuje ugradnju, pristup svim funkcijama s jedne strane pojednostavljuje rad i rukovanje. Potpuna kontrola sistema Precizno mjerenje protoka i jedinstvena dijagnostička funkcija za veliku uštedu energije i visoku pouzdanost sistema. Visoka pouzdanost AMETAL® i nehrđajući čelik garantiraju visoku otpornost na koroziju i smanjuju rizik od curenja. Tehnički opis Primjena: Sustavi grijanja i hlađenja. Funkcije: Regulacija Predpodešavanje (maks. protok) Kontrola diferencijalnog tlaka Mjerenje (AH, T, q) Zaporna funkcija (za odvajanje tijekom održavanja sustava – vidi također u Nepropusnost) Dimenzije: Razred tlaka: Diferencijalni tlak (ApV): Max. diferencijalni tlak (ApVmax): 400 kPa = 4 bar Min. diferencijalni tlak (ApVmin): (Vrijedi za poziciju 10, potpuno otvoreno. Ostale pozicije zahtijevaju manji diferencijalni tlak, provjeriti u programu HySelect.) ApVmax = Maksimalno dozvoljeni pad tlaka na ventilu, kako bi zadovoljili navedene vrijednosti. ApVmin = Minimalno preporučeni pad tlaka na ventilu, za ispravnu kontrolu diferencijalnog tlaka. Raspon protoka: Protok (qmax) može biti prednamješten u rasponu: DN 15 LF: 44 - 245 l/h qmax = l/h za svaku prednamještenu poziciju i potpuno otvorenom ventilu. LF = mali protok Temperatura: Max. radna temperatura: 90°C Min. radna temperatura: -10°C Radni medij: Voda ili neutralne tekućine, mješavine vode i glikola. Hod: 4 mm Nepropusnost: Propusnost ≤ 0,01% od max. qmax (pozicija 10) i ispravan smjer protoka. (Klasa IV prema EN 60534-4). Karakteristike: Linearna, ali prilagođena za on/off kontrolu. Materijal: Kućište ventila: AMETAL® Uložak ventila: AMETAL® Klip ventila: Nehrđajući čelik Vreteno: Nehrđajući čelik Brtva vretena: EPDM O-brtveni prsten Ap uložak: PPS Membrana: EPDM i HNBR Opruge: Nehrđajući čelik O-brtveni prsteni: EPDM AMETAL® je IMI Hydronic Engineering legura otporna na decinifikaciju. Označavanje: TA, IMI, PN 16, DN i smjer protoka. Sivi rukohvat: TA-COMPACT-P i DN. Za verziju s malim protokom LF. Priključak: Vanjski navoj prema ISO 228. Priključak na pogon: Pogoni: Vidjeti zasebnu informaciju na EMO T. Proizvodi, tekstovi, fotografije, crteži i dijagrami u ovoj brošuri podložni su promjenama od strane IMI Hydronic Engineering, bez prethodne obavijesti ili obrazloženja. Za više informacija o proizvodima i specifikacijama molimo posjetite nas na www.imi-hydronic.com.