http___www.keramikakanjiza.com_tehnicke-karakteristike__1.xml
1.1 1.2 1.3 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 23.2 24.1 24.2 24.3 25.1 26.1 27.1 28.1 29.1 29.2 30.1 31.1 32.1 33.1 34.1 34.2 34.3 35.1 36.1 36.2 37.1 38.1 38.2 39.1 39.2 40.1 41.1 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 51.1 52.1 52.2 53.1 54.1 55.1 55.2 55.3 56.1 57.1 58.1 58.2 58.3 59.1 60.1 60.2 61.1 62.1 62.2 63.1 64.1 65.1 66.1
"Keramika Kanjiža" doo from Kanjiža produces dry pressed floor and wall ceramic tiles (so-called monocuttura and monoporosa), as well as decorative accessories. The floor tiles are frost resistant, suitable for installation outside. Our ceramic tiles, in all their segments, meet the requirements of the harmonized European standard SRPS EN 14411. Since December 2005, the standard SRPS EN 14411 applies, published with the permission of the European Committee for Standardization CEN. This standard is an identical international standard EN 14411 which is compulsorily applied in all member states of the European Union. The CE-mark is a symbol of product conformity, developed in accordance with the harmonized standard that meets the important requirements of the Construction Products Directive. SRPS EN 14411 Ceramic tiles - Definition, classification, characteristics and designation -Defines terms and determines classifications, characteristics and requirements for designation of ceramic tiles with the best commercial quality (first class). According to the standard, the ceramic tiles are classified into groups according to the manner of production and water absorption. Group A Extruded ceramic tiles Group B Dry pressed tiles Ia Water absorption less than 0,5% Ib Water absorption from 0,5 to 3% IIa Water absorption from 3 to 6% IIb Water absorption from 6 to 10% III Water absorption more than 10% Glazed (GL) Unglazed (UGL) Floor tiles Group B Ib Wall tiles Group B III In the attachments for the standards SRPS EN 14411 for A to L, for each product group there are given minimal technical requirements in terms of dimensions and quality of visible surfaces, as well as physical and chemical properties. Group B Ib Attachment H Group B IIIAttachment K Testing methods used for determination of the product characteristics are described in the standards SRPS ISO 10545. SRPS ISO 10545-1 Sampling and basis for acceptance - This standard determines the number of samples that should be checked from the series and a maximal number of allowed mistakes. SRPS ISO 10545-2 Determination of dimensions and quality of visible surface - This standard establishes a method for determining the mesurement characteristics (length, width, thickness, flatness of sides, deviation for a right angle, and flatness of the surface) and quality of the surface of ceramic tiles. SRPS ISO 10545-3 Determination of water absorption, apparent porosity, apparent relative density and bulk density - This testing establishes a method for determination of water absorption and apparent porosity of ceramic tiles. SRPS ISO 10545-4 Determination of modulus of rupture and fracture strength - Establishes a testing method for determining the fracture strength. Obtained data indicate the load that the tile can bear. SRPS ISO 10545-7 Determination of surface abrasion resistance of glazed tiles -PEI classification - The glaze resistance to surface abrasion is being determined. The procedure is perfomed by rotation of assets for abrasion and assessment of the abrasion effect, by visual comparison of tiles exposed to abrasion and tiles which were not exposed to abrasion. The product assessment is performed from 0 to 5, depending on the speed of rotation tools and occurence of damages (5 is the highest class of resistance of glazed tiles according to the surface abrasion). PEI - classification of glazed floor tiles in relation to their abrasion resistance PEI 0 Glazed tiles in this class are not recommended for application on floors. PEI 1 Appropriate for covering floor surfaces where people walk only in shoes with soft soles or barefoot, without dirt which scratches the floor surface (for example, residential bathrooms and bedrooms without direct access from outside). PEI 2 Appropriate for covering floor surfaces where people walk in soft or plain shoes, usually with small quantities of dirt which scratches the surface (for example, rooms and living rooms in houses and apartments, with the exception of the kitchen, the doorway and crowded rooms). PEI 3 Appropriate for covering floor surfaces where people often walk in plain shoes, with little dirt which scratches the floor (for example, residential kitchens, halls, corridors, balconies, terraces). This does not refer to exceptional footware, for example - studdied boots. PEI 4 Appropriate for floors with normal movement of people with slightly more dirt which scratches the floor (for example entrances, public kitches, hotels, exibition and retail space). PEI 5 Appropriate for floors with constant great natural load and presence of dirt which scratches (for example, public surfaces such as commercial centers, airport interior rooms, hotel lobbies and application in industry). This classification is valid for application in usual conditions. The information about abrasive resistance of floor tiles is indicated under the figures of floor tiles. SRPS ISO 10545-8 Determination of linear thermal expansion - he coefficient of linear thermal expansion is being determined for a range of room temperature up to 100 °C. The value indicates the extent to which the placed tile will expand due to temperature changes. This information should be taken into consideration during the determination of fugue thickness between the tiles. SRPS ISO 10545-9 Determination of thermal shock resistance - The tiles are exposed to abrupt temperature changes and afterwards the occurence of damages is being checked. SRPS ISO 10545-10 Determination of moisture expansion - This standard establishes a method for determination of moisture expansion of ceramic tiles. The data help to determine the dimension between tiles. SRPS ISO 10545-11 Determination of crazing resistance of glazed surfaces - Occurence of cracks on the surface of glazed tiles is performed after treating them with compressed stream at a pressure of 500 kPa and temperature of 159 °C, for two hours in an autoclave. SRPS ISO 10545-12 Determination of frost resistance - According to this method, the tiles are exposed to freezing and thawing within a temperature range from -5 °C to +5 °C, for at least 100 cycles. This testing simulates the prodcut behavior in external climate conditions. SRPS ISO 10545-13 Determination of resistance to chemicals - This testing determines the tiles' resistance to the effect of household chemicals, salts in the water of a swimming-pool, acid, base and resistance to the effect of a 'pencil with HB hardness'. Depending on the type of chemicals and resistance of tiles, they are divided in the following classes: Household chemicals and salts in the water of a swimming-pool GA with no visible effects GB small changes in the appearance or if the tiles did not pass the testing with a 'pencil with HB hardness' GC siginificant changes Acids and bases (low concentrations) GLA with no visible effects GLB small changes in the appearance or if the tiles did not pass the testing with a 'pencil with HB hardness' GLC siginificant changes Acids and bases (high concentrations) GHA with no visible effects GHB small changes in the appearance or if the tiles did not pass the testing with a 'pencil with HB hardness' GHC siginificant changes SRPS ISO 10545-14 Determination of stain resistance - The visible surface of the tiles is exposed to contact with assets that create stains, and classification is performed after removal. The classification is performed from 5 to 1 depending on the ease of removing the stains, whereupon the stains are most easily removed at class 5. DIN 51130:2004-06 Determination of anti-slip properties for floor tiles For bigger floor surfaces, industrial and commercial purposes, it is desirable that the friction coefficient is higher than the one used in houses. The German standard DIN 51130:2004-06 defines the procedure and serves for testing and classification of anti-slip properties of floor coverings which have been stipulated for use in working rooms and areas where danger of slipping exists. The accepted angle is determined on a floor coating with applied lubricated asset (oil) and the person who performs control with control shoes moves forward-backward on the floor coating which is being controlled and which starts to tilt from its horizontal state and the inclination increases up to an accepted angle, i.e. an angle when the controller reaches the boundary of safe walking. The accepted angle is used for assessment of the degree of slip resistance. DIN 51097:02.80 Determination of characteristics for prevention of slips The characteristics of floor coatings according to this standard are assessed in conditions of moisture, on the treads of floor coverings which are used in bathrooms, changing rooms, toilets and similar rooms. During the execution of the procedure, a liquid is continuously and uniformly applied for testing the floor covering which will start to tilt from its horizontal position and the inclination will grow up to an accepted angle, i.e. an angle when the controller reaches the boundary of safe walking. The person who performs control moves forward-backward on the floor coating which is being controlled, barefoot. Depending on the achieved inclination angle, the tested coverings could be classified in the following groups: The information about slip resistance of floor tiles is indicated under the figures of floor tiles. SRPS U. F2.011 Finishing works in structural engineering - Execution of ceramic works - The standard determines a procedure for wall and floor cladding with ceramic tiles inside of premises, as well as outside. In the process of automatic packaging, the ceramic tiles are packed in a cardboard boxes in which the industrial printer prints the basic data for identifying the product. The first printed line contains: date, identification number of the classifier and product name. The second printed line contains: number of work order and product code, product class, product shade and caliber, that is, dimension of the floor tiles: 0105120100 AMORE BIANCO 000000 KL1 N51 - example for wall tiles 000000 xxxxx KL1 N51 CAL3 - example for floor tiles which are classified according to dimensions Each pallete of finished product contains a barcode, which helps to identify the tiles.
1.1 1.2 1.3 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 23.2 24.1 24.2 24.3 25.1 26.1 27.1 28.1 29.1 29.2 30.1 31.1 32.1 33.1 34.1 34.2 34.3 35.1 36.1 36.2 37.1 38.1 38.2 39.1 39.2 40.1 41.1 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 51.1 52.1 52.2 53.1 54.1 55.1 55.2 55.3 56.1 57.1 58.1 58.2 58.3 59.1 60.1 61.1 62.1 62.2 63.1 64.1 65.1 66.1
"Keramika Kanjiža" doo iz Kanjiže proizvodi suvo presovane, jednom pečene podne i zidne keramičke pločice (takozvanu monokoturu i monoporozu) kao i ukrasnu galanteriju. Podne pločice su otporne na mraz, pogodne su za postavljanje spolja. Naše keramičke pločice u svim segmentima ispunjavaju zahteve harmonizovanog evropskog standarda SRPS EN 14411. Od decembra 2005. godine primenjuje se standard SRPS EN 14411, objavljen uz dozvolu Evropskog komiteta za standardizaciju CEN. Ovaj standard je identičan međunarodnom standardu EN 14411 koji se obavezno primenjuje u svim članicama evropske unije. CE-znak je simbol usaglašenosti proizvoda, izrađenog u skladu sa harmonizovanim standardom koji ispunjava bitne zahteve direktive za građevinske proizvode. SRPS EN 14411 Keramičke pločice - Definicije, klasifikacija, karakteristike i obeležavanje -Definiše termine i utvrđuje klasifikacije, karakteristike i zahteve za obeležavanje keramičkih pločica najboljeg komercijalnog kvaliteta (prva klasa). Prema standardu keramičke pločice se uvrstavaju u grupe prema načinu proizvodnje i upijanju vode. Grupa A Vučene (ekstrudirane) keramičke pločice Grupa B Suvo presovane pločice Ia Upijanje vode manje od 0,5% Ib Upijanje vode od 0,5 do 3% IIa Upijanje vode od 3 do 6% IIb Upijanje vode od 6 do 10% III Upijanje vode preko 10% Glazirane (GL) Neglazirane (UGL) Podne pločice Grupa B Ib Zidne pločice Grupa B III U prilozima standarda SRPS EN 14411 od A do L, za svaku grupu proizvoda su dati minimalni tehnički zahtevi u pogledu mera i kvaliteta vidne površine kao i fizičkih i hemijskih svojstva. Grupa B Ib Prilog H Grupa B III Prilog K Metode ispitivanja korišćene za određivanje karakteristika proizvoda su opisane u standardima SRPS ISO 10545. SRPS ISO 10545-1 Uzimanje uzoraka i osnove za prihvatanje - Ovaj standard utvrđuje broj uzoraka koje treba proveriti iz partije i maksimalni broj dozvoljenih grešaka. SRPS ISO 10545-2 Određivanje mera i kvaliteta vidne površine - Ovim standardom utvrđuje se metoda za određivanje mernih karakteristika (dužina, širina, debljina, pravost stranica, odstupanje od pravog ugla, ravnost površine) i kvalitet površine keramičkih pločica. SRPS ISO 10545-3 Određivanje upijanja vode, prividne poroznosti, prividne relativne zapreminske mase i zapreminske mase - Ovim ispitivanjem se utvrđuje metoda za određivanje upijanja vode i prividne poroznosti keramičkih pločica. SRPS ISO 10545-4 Određivanje modula loma pri savijanju i čvrstoće pri lomu - Utvrđuje metodu ispitivanja za određivanje čvrstoće pri lomu. Dobijeni podatak ukazuje na opterećenje koju pločica može podneti. SRPS ISO 10545-7 Određivanje otpornosti glaziranih pločica prema površinskom habanju -PEI klasifikacija - Ocenjuje otpornost glazure prema površinskom habanju. Postupak se vrši rotiranjem sredstva za habanje i ocenjivanjem delovanja habanja, vizuelnim poređenjem pločica izloženih habanju i pločica koje nisu bile izložene habanju. Ocenjivanje proizvoda se vrši od 0 do 5, u zavisnosti od broja obrtaja rotirajućeg sredstva i pojave oštećenja (5 je najviša klasa otpornosti glaziranih pločica prema površinskom habanju). PEI - klasifikacija glaziranih podnih pločica u odnosu na njihovu otpornost prema habanju PEI 0 Glazirane pločice u ovoj klasi ne preporučuju se za korišćenje na podovima. PEI 1 Prikladno za pokrivanje podnih površina u kojima se hoda isključivo u obući sa mekanim đonovima ili bosonog, bez nećistoća koje grebu podnu površinu (na primer stambena kupatila i spavaće sobe bez direktnog pristupa spolja). PEI 2 Prikladno za pokrivanje podnih površina u kojima se hoda u mekanoj ili običnoj obući sa uobičajeno malim količinama nečistoće koja grebe površinu (na primer sobe i prostori za dnevni boravak u kućama i stanovima sa izuzetkom kuhinja, ulaza i prostora u kojima je veliki promet). PEI 3 Prikladno za pokrivanje podnih površina gde se često hoda u običnoj obući sa malo nečistoće koja grebe pod (na primer stambene kuhinje, holovi, hodnici, balkoni, terase). Ne odnosi se na izuzetnu obuću, na primer čizme okovane ekserima. PEI 4 Prikladno za podove tamo gde se odvija uobičajen promet sa nešto više nečistoće koja grebe pod (na primer ulazi, javne kuhinje, hoteli, izložbeni i prodajni prostori). PEI 5 Prikladno za podove sa stalnim velikim prohodnim opterećenjem i prisutnom prljavštinom koja grebe (na primer javne površine kao što su trgovački centri, unutrašnje aerodromske prostorije, hotelska predvorja i primena u industriji). Ova klasifikacija važi za primenu pod uobičajenim uslovima. Informacija o otpornosti podnih pločica prema habanju navedena je ispod slike podnih pločica. SRPS ISO 10545-8 Određivanje linearnog termičkog širenja - Određuje se koeficijent linearnog termičkog širenja za opseg od sobne temperature do 100 °C. Vrednost pokazuje u kojoj meri će se postavljena pločica širiti usled temperaturnih promena. Ovaj podatak treba da se uzme u obzir prilikom određivanja debljine fuge između pločica. SRPS ISO 10545-9 Određivanje otpornosti prema temperaturnom šoku - Pločica se izlaže nagloj promeni temperature i nakon toga se proverava pojava oštećenja. SRPS ISO 10545-10 Određivanje širenja vlaženjem - Ovim standardom se utvrđuje metoda za određivanje širenja keramičkih pločica vlaženjem. Podatak pomaže prilikom dimenzionisanja fuge između pločica. SRPS ISO 10545-11 Određivanje otpornosti prema vlasavosti glaziranih pločica - Vrši se provera pojave pukotina na površini glazirane pločice nakon tretiranja sa parom na pritisku od 500 kPa i temperaturi od 159 °C, dva sata u autoklavu. SRPS ISO 10545-12 Određivanje otpornosti prema mrazu - Po ovoj metodi pločice se izlažu smrzavanju i otapanju u temperaturnom opsegu od -5 °C do +5 °C, najmanje 100 ciklusa. Ovo ispitivanje simulira ponašanje proizvoda u spoljašnjim klimatskim uslovima. SRPS ISO 10545-13 Određivanje otpornosti prema hemikalijama - Ovim ispitivanjem se utvrđuje otpornost pločica prema dejstvu hemikalija za domaćinstvo, soli u vodi bazena za plivanje, kiselina, baza i otpornost prema dejstvu olovke HB tvrdoće. U zavisnosti od vrste hemikalija i otpornosti pločice se dele u sledeće klase: Hemikalije za domaćinstvo i soli u vodi bazena za plivanje: GA bez vidljivih efekata GB male promene u izgledu ili ako pločice nisu prošle test olovke HB tvrdoće GC značajne promene Kiseline i baze (malih koncentracija) GLA bez vidljivih efekata GLB male promene u izgledu ili ako pločice nisu prošle test olovke HB tvrdoće GLC značajne promene Kiseline i baze (velikih koncentracija) GHA bez vidljivih efekata GHB male promene u izgledu ili ako pločice nisu prošle test olovke HB tvrdoće GHC značajne promene SRPS ISO 10545-14 Određivanje otpornosti prema stvaranju mrlja - Vidna površina pločice se dovodi u kontakt sa sredstvom za stvaranje mrlja, nakon odstranjivanja vrši se klasifikacija. Klasifikacija se vrši od 5 do 1 u zavisnosti od lakoće uklanjanja mrlje, pri čemu se kod klase 5 najlakše uklanja mrlja. DIN 51130:2004-06 Određivanje antikliznih svojstava za podne pločice Za veće podne površine, industrijske i komercijalne namene poželjno je da je koeficjenat trenja viši od onih koji se koristi u kućama. Nemački standard DIN 51130:2004-06 definiše postupak i služi za testiranje i klasificiranje anti kliznih svojstava podnih obloga koji su predviđeni za korišćenje u radnim prostorima i područjima gde je prisutna opasnost od klizanja. Prihvaćeni ugao se utvrđuje na podnoj oblozi premazanoj sa sredstvom za podmazivanje (ulje) a osoba koja sprovodi kontrolu sa kontrolnim cipelama kreće se napred - nazad po kontrolisanoj podnoj oblozi koja se počinje naginjati od horizontalnog stanja i nagib raste do prihvaćenog ugla tj.ugla pri kom kontrolor dostiže granicu sigurnog hodanja. Prihvaćeni ugao služi za ocenu stepena otpornosti na klizanje. DIN 51097:02.80 Utvrđivanje karakteristika za sprečavanje klizavosti U uslovima vlažnosti, na gazištima podnih obloga koje se koriste u kupatilu, svlačionicama, sanitarnim čvorovima i sličnim prostorijama, ocenjuju se karakteristika podnih obloga po ovom standardu. Tokom izvođenja postupka kontinualno i jednolično se nanosi tečnost na test podnu oblogu koja se počinje naginjati od horizontalnog stanja i nagib raste do prihvaćenog ugla tj.ugla pri kom kontrolor dostiže granicu sigurnog hodanja. Osoba koja sprovodi kontrolu kreće se napred - nazad po kontrolisanoj podnoj oblozi bosih nogu. U zavisnosnosti od postignutog ugla nagiba test obloge se mogu svrstati u sledeće grupe: Informacija o otpornosti podnih pločica prema klizanju navedena je ispod slike podnih pločica. SRPS U.F2.011 Završni radovi u građevinarstvu - Izvođenje keramičarskih radova - Standard utvrđuje postupak za oblaganje zidova, podova keramičkim pločicama u unutrašnjosti objekta i spolja. U procesu automatskog pakovanja keramičke pločice se pakuju u kartonsku ambalažu na koju industrijski štampač štampa osnovne podatke identifikacije proizvoda. U prvom redu štampa se: datum, identifikacioni broj klasera i ime proizvoda. U drugom redu štampa se: broj radnog naloga i šifra proizvoda, klasa proizvoda, nijansa proizvoda i kaliber odnosno dimenzija za podne pločice: AMORE BIANCO KL1 N51 - primer za zidne pločice 000000 xxxxx KL1 N51 CAL3 - primer za podne pločice koje se razvrstavaju po dimenzijama Svaka paleta gotovog proizvoda sadrži bar-cod, pomoću koga se pločice identifikuju.