http___www.imi-hydronic.com_ba_products-solutions_Balancing-and-control_Regulatori-diferencijalnog-tlaka_Prestrujni-ventil_PM-512__1.xml
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 12.1 13.1 14.1 14.2 15.1 16.1 17.1 18.1 19.1 20.1 20.2 21.1 21.2 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 36.2
Differential pressure controller with adjustable set-point These differential pressure controllers for heating and cooling systems are particularly effective in situations requiring high temperatures and/or pressure drop. Also suitable for use on the secondary side in district heating and comfort cooling systems. Ductile iron body - painted with duasolid that offers good rust protection. Technical description Application: Heating and cooling systems with variable flow. District heating substations, primary side. Functions: Differential pressure control over the load. Closes at increasing Ap. Dimensions: Pressure class: PN 16 and PN 25 Max. differential pressure (ApV): 1600 kPa = 16 bar Setting range: Ap is adjustable within 10-60 kPa, 50-150 kPa, 130-250 kPa and 100-400 kPa. Delivery setting: 10 kPa, 50 kPa, 130 kPa and 100 kPa. Temperature: Max. working temperature: 150°C Min. working temperature: -10°C Media: Water and neutral fluids, water-glycol mixtures. Material: Valve body: Ductile iron EN-GJS-400 Actuator body: Ductile iron EN-GJS-400 Diaphragm: EPDM Valve seat: Stainless steel Valve plug: Stainless steel with EPDM insert Surface treatment: Duasolid painting. Marking: TA, DN, PN and flow direction arrow. Flanges: According to EN-1092-2:1997, type 21. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 2.4 3.1 4.1 5.1 6.1 7.1 8.1 9.1 11.1 12.1 13.1 14.1 15.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 32.1 32.2
Prestrujni ventil Ventil za sniženje tlaka nalazi primjenu u sustavima grijanja i hlađenja promjenjivog protoka. PM 512 odlikuje se mekom NBR membranom dugog vijeka trajanja, a također je opremljen pomoćnom oprugom koja djeluje kao sigurnosna u funkciji otvaranja, u slučaju otkazivanja. Izveden je za jednostavno rukovanje u skučenim prostorima. Tijelo ventila od nodularnog lijeva elektroforetski je obojano, za optimalnu zaštitu od korozije. Tehnički opis Primjena: Sustavi grijanja i hlađenja promjenjivog protoka. Funkcija: Linijski prestrujni ventil s pneumatskom oprugom. Otvara pri povišenju ulaznog tlaka. Dimenzije: Razred tlaka: PN 25 ili PN 16 (DN 100-125) Max. diferencijalni tlak (ApV): 1 600 kPa = 16 bar Područje namještanja: Temperatura: Max. radna temperatura: 100°C Min. radna temperatura: -10°C Radni medij: Voda i neutralni radni mediji, mješavine vode i glikola. Materijal: Tijelo ventila: Nodularni lijev EN-GJS-400 Membrana i brtve: NBR, EPDM Površinska obrada: Elektroforetsko bojanje. Označavanje: TA, DN, PN, Kvs, oznaka materijala i strelica smjera strujanja. Prirubnice: Proizvodi, tekstovi, fotografije, crteži i dijagrami u ovoj brošuri podložni su promjenama od strane IMI Hydronic Engineering, bez prethodne obavijesti ili obrazloženja. Za više informacija o proizvodima i specifikacijama molimo posjetite nas na www.imi-hydronic.com.