http___www.imi-hydronic.com_ba_products-solutions_Pressurisation-and-Water-quality_Odravanje-tlaka_Ekspanzijske-posude-sa-zranim-jastukom_Ekspanzijska-posuda-s-membranom-__1.xml
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 11.2 12.1 13.1 15.1 16.1 18.1 19.1 19.2 20.1 21.1 22.1 23.1 24.1 25.1 25.2 26.1 27.1 28.1 29.1 30.1 30.2
Compression coupling for metallic pipes This is a supremely flexible compression coupling for metallic pipes, soft and hard copper pipes and soft steel pipes in heating, cooling and tap water systems. The same body fits up to seven sizes of all different pipes, ensuring quick and easy installation and saving money by reducing storage space. Technical description Applications: Heating and cooling systems. Tapwater systems. Process systems where the media does not affect the incoming material. Gas systems (natural gas, propane and butane) Function: FPL compression coupling for soft and hard copper pipes and soft steel pipes. NOTE! FPL is not approved for gas installations in combination with steel pipes. A support bush must be used with soft copper and steel pipes. Dimensions: The large combination possibilities – one connection body size handles several pipe dimensions by only changing the thrust nut and cone – reduces the required storage space substantially. Pressure class: Temperature: Max. working temperature: 100°C. For temperatures over 100°C, please contact closest sales office. Material: Parts which are subject to water contact: AMETAL® AMETAL® is the dezincification resistant alloy of IMI Hydronic Engineering. Surface treatment: Delivered as non-plated (yellow) or surface treated (chrome/nickle plated). See each product table. Approvals: Approved by Gastec for gas installations with copper pipes: Certificate Q06/004 (Couplings approved for gas are marked in the product tables). Bodies are marked with: The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 21.2
Od 6L do 750L Linija ekspanzijske posude s fiksnom membranom su idealne za manje sustave grijanja i hlađenja do 750 L. Linija ovih posuda ima jednostavan dizajn i robusnu konstrukciju. Tehnički opis Primjene: Sustavi grijanja i hlađenja. Medij: Neagresivni i netoksični mediji. Dodatak antifriza do 49%. Tlak: Min. dopušteni tlak, PSmin: 0 bar Max. dopušteni tlak, PS: ovisno o tipu Radna temperatura: Material: Posuda : Čelik Gumena membrane : SBR Transport i skladištenje: Na suhom mjestu, zaštićeno od smrzavanja. Approvals: CE testirano prema PED/DEP 97/23/EC. Proizvodi, tekstovi, fotografije, crteži i dijagrami u ovoj brošuri podložni su promjenama od strane IMI Hydronic Engineering, bez prethodne obavijesti ili obrazloženja. Za više informacija o proizvodima i specifikacijama molimo posjetite nas na www.imi-hydronic.com.