http___www.imi-hydronic.com_ba_products-solutions_Balancing-and-control_Regulacijski-ventili_Balansirajui-i-regulacijski-ventili_TBV-C__1.xml
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 15.1 17.1 18.1 18.2 19.1 19.2 20.1 20.2 21.1 22.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 33.2 34.1 34.2 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 44.2 45.1 46.1 47.1 48.1 49.1 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 58.2
Pressure independent balancing and control valve (PIBCV) Designed for modulating control of terminal units in heating and cooling systems, the TBV-CMP ensures optimum performance over a long lifetime. Correct control characteristic contributes to a linear circuit characteristic for accurate hydronic control. The TBV-CMP together with our balancing instruments gives possibility for advanced measuring and diagnostic. Technical description Application: Heating and cooling systems. Functions: Control Pre-setting (of flow) Differential pressure control Measuring Shut-off (for isolation during system maintenance) Flushing Dimensions: Pressure class: Differential pressure (ApV): Max. differential pressure: 350 kPa (AHmax) Min. differential pressure: 15 kPa (AHmin) (Valid for position 10, fully open. Other positions will require lower differential pressure, check with the software HySelect.) Flow range: The flow (qmax) can be pre-set within the range: Minimum controllable flow: DN 15 LF: 3 l/h DN 15 NF: 7 l/h DN 20 NF: 10 l/h DN 25 NF: 20 l/h Temperature: Max. working temperature: 120°C Min. working temperature: -20°C Lift: 4 mm Characteristic: See diagrams under "Valve characteristics". Leakage rate: Tight sealing Material: Valve body: AMETAL® Valve plug: PPS (polyphenylsulphide) Seat seal: EPDM/Stainless steel (DN 15-20). EPDM/AMETAL® (DN 25). Spindle seal: EPDM O-ring Valve insert: AMETAL®, PPS (polyphenylsulphide) Spring: Stainless steel Spindle: Nedox® coated AMETAL® Membrane: HNBR AMETAL® is the dezincification resistant alloy of IMI Hydronic Engineering. Marking: Body: TA, PN 16, DN, inch size and flow direction arrow. Identification ring on measuring point: White = Low flow (LF) Black = Normal flow (NF) Actuators: See separate information on EMO TM. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 14.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 23.2 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 38.2
Balansirajući ventil za krajnje potrošače, za dvopoložajnu regulaciju Predviđen za primjenu na krajnjim potrošačima, u sustavima grijanja i hlađenja, TBV-C jamči preciznu regulaciju toplovodnog grijanja i optimalni učinak za dugog vijeka trajanja. IMI Hydronic Engineering AMETAL® legura otporna na decinfikaciju, na minimum smanjuje opasnost od propuštanja. Tehnički opis Primjena: Sustavi grijanja i hlađenja. Funkcije: Regulacija Balansiranje Prethodno podešavanje Mjerenje Zaporna funkcija (za odvajanje tijekom održavanja sustava) Dimenzije: Razred tlaka: Temperatura: Max. radna temperatura: 120°C Min. radna temperatura: -20°C Nepropusnost: Čvrsto brtvljenje Materijal: Kućište ventila: AMETAL® Brtva sjedišta ventila: Disk ventila od EPDM (DN 15-20). EPDM/AMETAL® (DN 25). Brtva vretena: EPDM O-brtveni prsten Umetak ventila: AMETAL® , PPS (polifenilsulfid) Povratna pruga: Nehrđajući čelik Vreteno: AMETAL® presvučen Nedox® Spojne cijevi s ravnim krajevima: Navojna spojnica: AMETAL® AMETAL® je IMI Hydronic Engineering legura otporna na decinifikaciju. Označavanje: Kućište ventila: TA, PN 16/150, DN, veličina u inčima i strelica smjera strujanja. Identifikacijski prsten na mjernom priključku: Bijele boje: Mali protok (LF) Crne boje Normalni protok (NF) Pogoni: Vidjeti zasebnu informaciju na EMO T. Proizvodi, tekstovi, fotografije, crteži i dijagrami u ovoj brošuri podložni su promjenama od strane IMI Hydronic Engineering, bez prethodne obavijesti ili obrazloženja. Za više informacija o proizvodima i specifikacijama molimo posjetite nas na www.imi-hydronic.com.