http___www.imi-hydronic.com_srb-rs_products-solutions_Balansiranje_i_kontrola_Balansni-ventili_Balansni-ventili_STAD__1.xml
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 11.1 13.1 14.1 14.2 15.1 15.2 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 30.2
Thermostatic valve body with pressure-compensated valve cone Multi V is a thermostatic valve body with IMI Heimeier M 30 x 1.5 connection, intended for temperature control in heating and cooling systems with thermostatic heads, return temperature limiter, or actuators. The valve cone is pressure-compensated, so the Multi V is especially suitable for applications at high differential pressure. Sizes from DN 10 up to DN 50 with female or male thread, or press-connection, ensure the widest possible range of applications. Technical description Applications: Heating and cooling systems Functions: Control Shut-off Dimensions: Pressure class: Temperature: Max. working temperature: 120 °C, with press connection 110 °C Min. working temperature: –10 °C Material: Valve body: Gunmetal Seat seal: Sealing of EPDM, Cone of brass. Spindle seal: EPDM O-ring Valve insert: Brass Return spring: Stainless steel Spindle: Stainless steel Marking: Body: THE, PN 16, DN, flow direction arrow. Thermostatic heads and actuators: - Thermostatic heads - RTL return temperature limiter (see accessories) - Thermal actuator EMO T, EMOtec - Motorized actuators EMO 1, EMO 3, EMO EIB and EMOLON The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 15.1 17.1 18.1 19.1 19.2 19.3 19.4 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 33.2
Balansni ventil STAD sa izuzetnim hidrauličkim performansama i impresivnim opsegom primene. Idealan za upotrebu u intstalacijama grejanja i hlađenja i sistemima potrošne vode. Tehnički opis Namena: Sistemi grejanja i hlađenja Sistemi potrošne vode Funkcija: Balansiranje Predregulacija Merenje Zatvaranje Ispuštanje (opciono) Dimenzije: Klasa pritiska: Temperatura: Max. radna temperatura: 120°C. Za vise temperature max. (max. 150°C), molimo Vas kontaktirajte IMI Hydronic Engineering. UPOZORENJE! DN 25-50 sa ravnim krajevima max. radna tempertatura 120°C. Min. radna temperatura: -20°C Materijal: Ventili su napravljeni od AMETAL® Sedište ventila: Osnova sa EPDM prstenom Vreteno: EPDM prsten Ručica: Polyamid i TPE Ravni krajevi: Nastavci: AMETAL® Zaptivanje (DN 25-50): EPDM prsten AMETAL® je legura otporna na koroziju i zaštićena od strane IMI Hydronic Engineering. Označavanje: Telo: TA, PN 20/150, DN i veličina u inčima. Ručica: Tip ventila i DN. Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.