http___www.imi-hydronic.com_ba_products-solutions_Thermostatic-control_Termostatske-glave-i-radijatorski-ventili_Termostatski-ventili-sa-prikljukom-za-radijatore-u-dvije-toke_E-Z-Ventil__1.xml
1.1 2.1 2.2 3.1 4.1 4.2 4.3 5.1 5.2 5.3 6.1 6.2 6.3 7.1 8.1 9.1 10.1 11.1 11.2
For single and two-pipe heating systems E-Z Valve with immersion pipe is connected to radiators with a lower one-point connection, e.g. bathroom radiators, column radiators, etc.. Centre-to-centre distance of pipe connections 50 mm. Technical description E-Z Valve, nickel-plated with corrosion-resistant gunmetal, immersion pipe, for radiators with a lower singlepoint connection. Available in angle and straight versions for both single and two-pipe systems. The single-pipe design has been created with a radiator portion of 35%. E-Z Valves work with all IMI Heimeier thermostatic heads and IMI Heimeier and IMI TA actuators. The stainless spindle is equipped with a double O-ring seal. The outer O-ring and the complete thermostatic insert can be changed without draining-off the system. The return shut-off is actuated with a hexagon key, size 8. With a two-pipe system, the return shut-off also assumes the presetting function. The spindle is sealed with an EPDM O-ring. Pipe connector G 3/4, with compression fittings for plastic, copper, precision steel, or composite pipes. For IMI Heimeier valves, use only the IMI Heimeier compression fittings which have been designed and indicated for the particular application (e.g. ID no. 15 THE). Permitted operating temperature 120°C. Permitted operating pressure 10 bar. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 3.1 4.1 4.2 4.3 5.1 5.2 5.3 6.1 6.2 6.3 7.1 8.1 8.2 9.1 10.1 11.1 11.2
Za jednocijevne i dvocijevne sustave grijanja E-Z VALVE s uronskom cijevi priključuje se na radijatore s donjim priključkom, npr. kupaonski radijatori, stupni radijatori, itd. Razmak osi je 50 mm. Tehnički opis E-Z ventili od poniklane bronce, otporni na koroziju, s uronskom cijevi, za radijatore s donjim priključkom. Dostupni su u varijantama kao kutni i ravni, za jednocijevne i dvocijevne sustave. Jednocijevna izvedba izvedena je s udjelom radijatora od 35%. E-Z ventili funkcioniraju sa svim termostatskim regulatorima i pogonima. Vreteno od nehrđajućeg čelika opremljeno je s dvostrukim O-brtvenim prstenom. Vanjski O-brtveni prsten i kompletni termostatski insert mogu se zamijeniti bez pražnjenja sustava. Zatvaranje protoka povratnog voda aktivira se s šesterokutnim ključem, veličine 8. S dvocijevnim sustavom, zatvaranje protoka povratnog voda poprima funkciju predpodešavanja. Vreteno je zabrtvljeno s EPDM O-brtvenim prstenom. Cijevna spojnica G3/4 s pres fitinzima za plastične, bakrene, precizne čelične ili višeslojne cijevi. Za IMI Heimeier ventile treba koristiti samo IMI Heimeier pres fitinge, izvedene i namijenjene za posebne slučajeve primjene (npr. DN 15 THE). Dopuštena radna temperatura 120°C. Dopušteni radni tlak 10 bar. Proizvodi, tekstovi, fotografije, crteži i dijagrami u ovoj brošuri podložni su promjenama od strane IMI Hydronic Engineering, bez prethodne obavijesti ili obrazloženja. Za više informacija o proizvodima i specifikacijama molimo posjetite nas na www.imi-hydronic.com.