http___www.imi-hydronic.com_srb-rs_products-solutions_Termostatska_kontrola_Termostatske-glave-i-radijatorski-ventili_Termostatski-radijatorski-ventili_Eclipse__1.xml
1.1 2.1 2.2 2.3 2.4 2.5 2.6 2.7 2.8 2.9 2.10 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 21.1 23.1 24.1 24.2 25.1 25.2 26.1 27.1 29.1 30.1 31.1 31.2 33.1 33.2 34.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 50.2 51.1 52.1 53.1 54.1 55.1 56.1 56.2 56.3 56.4 56.5 56.6 56.7 57.1 57.2
with two-point connection, angle and straight type, for R 1/2 and G 3/4 connection, with automatic flow limitation The Multilux 4-Eclipse-Set is connected in 2-pipe systems to radiators with a lower 2-point connection such as bathroom radiators, design radiators, universal radiators or radiators with integrated valves. The valve has a unique integrated flow limiter that eliminates over flows. The required flow rate can be adjusted with one twist directly at the valve. The adjusted flow will not be exceed even if there are load changes in the system, due to other valves closing or during morning start up. The valve controls the flow rate independently from differential pressure. Therefore, complicated calculations to determine settings are not necessary. Centre-to-centre distance of connections 50 mm. The Multilux 4-Eclipse-Set is suitable for installation as angle or straight form. Thermostatic insert and shut-off insert are interchangeable. Therefore the valve is suitable for installation both left and right side of the radiator. Key features Integrated flow limiter eliminates over flows Suitable for installation as angle or straight form for pipe connection to the wall or vertical to the floor Thermostatic insert and shut-off insert are interchangeable the valve is suitable for installation both left and right side of the radiator Sets with white or chrome cover easy to install Technical description Applications area: 2-pipe heating systems Function: Control Flow limitation Shut-off Dimensions: Pressure class: Temperature: Max. working temperature: 120 °C, with cover 90 °C. Min. working temperature: –10 °C Flow range: The flow can be stepless pre-set within the range: Delivery setting 150 l/h. Differential pressure (ApV): Max. differential pressure: Min. differential pressure: 10 – 100 l/h = 10 kPa 100 – 150 l/h = 15 kPa Materials: Valve body: Corrosion resistant Gunmetal. O-rings: EPDM rubber Valve disc: EPDM rubber Return spring: Stainless steel Valve insert: Brass, PPS (polyphenylsulphide) Spindle: Niro-steel spindle with double O-ring sealing. Cover: ABS Surface treatment: Valve body gunmetal, fittings are nickel-plated. Marking: THE and II+ Designation. Protection cap orange. Radiator connection: Adapters for R1/2 and G3/4, for radiator connections. Tolerance compensation ±1,0 mm with special union nuts and flexible flat seal system for installation free of tension. Pipe connection: G3/4 male thread for compression fittings for plastic, copper, precision steel or multi-layer pipe. Connection to thermostatic head and actuator: IMI Heimeier M30x1.5 Thermostatic head DX: Thermostatic head DX with closed graduation cap and liquidfilled thermostat. High actuating force, minimum hysteresis, optimum closing time. Stable control response even with minor calculated p-band variations (<1 K). Conforming to German EnEV and/or DIN V 4701-10. Setting numbers 1–5. Frost protection. Temperature range 6 °C to 28 °C. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 2.4 2.5 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 23.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 49.2 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 59.1 59.2
Termostatski radijatorski ventil sa automatskim ograničenjem protoka Termostatski radijatorski ventil Eclipse ima jedinstveni ograničivač protoka koji eliminiše bilo kakvo prekoračenje protoka. Zahtevani protok se podešava direktno na ventilu. Podešeni protok neće biti veći čak ni kada postoje znatne promene u instalaciji bilo da neki ventili zatvaraju bilo da je reč o jutarnjem startovanju sistema grejanja. Ventil reguliše protok nezavisno od promene diferencijalnog pritiska. Prema tome, nisu potrebni komplikovani proračuni za određivanje pozicije predregulacije. Ključne karakteristike Integrisani ograničivač protoka Ne dozvoljava prekoračenje protoka Jednostavno podešavanje Kako bi se postigao projektovani protok Opseg protoka od 10 do 150 l/h Za veću fleksibilnost Sva tela ventila označena sa ‘’II’’ mogu biti modifikovana kao Eclipse Pr: Calypso exact, Calypso, Mikrotherm F, Multilux, Multilux 4-Set Perfect for renovation Standard dimensions and easy flow sizing Tehnički opis Namena: Sistemi grejanja. Funkcija: Kontrola Regulacija protoka Zatvaranje Dimenzije: Nazivni pritisak: Temperatura: Max. radna temperatura: 120°C, sa zaštitnom kapom ili aktuatorom 100°C. Min. radna temperatura: -10°C Opseg protoka: Protok se može predregulisati u opsegu: 10-150 l/h. Podešavanje protoka do 150 l/h. (Max. nominalni ptorok qmN na 10 kPa prema EN 215: 115 l/h) Diferencijalni pritisak (ApV): Max. differencijalni pritisak: Min. differencijalni pritisak: 10 – 100 l/h = 10 kPa 100 – 150 l/h = 15 kPa Materijal: Telo ventila: Mesing O-prsten: EPDM guma Disk ventila: EPDM guma Povratna opruga: Nerđajući čelik Uložak ventila: Mesing, PPS (polyphenylsulphide) Ceo termostatski uložak može se zameniti korišćenjem IMI Heimeier alata bez pražnjenja instalacije. Vreteno: Niro čelik sa duplim O-prstenastim zaptivanjem. Površinska obrada: Telo ventila i fiting su niklovani. Označavanje: THE, DN, oznaka zemlje, smer protoka i KEYMARK-oznaka. II+ oznaka. Narandžasta zaštitna kapa. Standardi: Telo ventila prema sledećim zahtevima: – KEYMARK sertifikovano i testirano prema DIN EN 215. Cevni priključci: Unutrašnji navoj je projektovan za povezivanje na cevi sa navojem, ili u kombinaciji sa kompresionim spojnicama, na bakarne ili precizne čelične cevi. U kombinaciji sa duplom zateznom spojnicom pogodan je za povezivanje na višeslojne cevi. Priključak na termostatsku glavu i aktuator: IMI Heimeier M30x1.5 Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.