http___www.imi-hydronic.com_srb-rs_products-solutions_Balansiranje_i_kontrola_Balansni-ventili_Balansni-ventili_STAD__1.xml
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 14.1 16.1 17.1 17.2 18.1 19.1 19.2 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 29.2
Balancing valve The STAD-C balancing valve has been specially developed for use in indirect cooling systems but performs just as effectively in refrigerated counters and cold-storage rooms. Whatever the application, the STAD-C delivers TA’s unrivalled hydronic performance. Technical description Application: Heating and cooling systems Tap water systems Functions: Balancing Pre-setting Measuring Shut-off Dimensions: Pressure class: Temperature: Max. working temperature: 150°C (At temperatures higher than 120°C, the handwheel should be removed.) Min. working temperature: -20°C Material: The valves are made of AMETAL® Seat seal: Stem with EPDM or FPM (Viton®) O-ring Spindle seal: EPDM or FPM (Viton®) O-ring Handwheel: Polyamide and TPE AMETAL® is the dezincification resistant alloy of IMI Hydronic Engineering. Marking: Body: TA, PN 20/150, DN and inch size. Handwheel: Valve type and DN. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 15.1 17.1 18.1 19.1 19.2 19.3 19.4 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 33.2
Balansni ventil STAD sa izuzetnim hidrauličkim performansama i impresivnim opsegom primene. Idealan za upotrebu u intstalacijama grejanja i hlađenja i sistemima potrošne vode. Tehnički opis Namena: Sistemi grejanja i hlađenja Sistemi potrošne vode Funkcija: Balansiranje Predregulacija Merenje Zatvaranje Ispuštanje (opciono) Dimenzije: Klasa pritiska: Temperatura: Max. radna temperatura: 120°C. Za vise temperature max. (max. 150°C), molimo Vas kontaktirajte IMI Hydronic Engineering. UPOZORENJE! DN 25-50 sa ravnim krajevima max. radna tempertatura 120°C. Min. radna temperatura: -20°C Materijal: Ventili su napravljeni od AMETAL® Sedište ventila: Osnova sa EPDM prstenom Vreteno: EPDM prsten Ručica: Polyamid i TPE Ravni krajevi: Nastavci: AMETAL® Zaptivanje (DN 25-50): EPDM prsten AMETAL® je legura otporna na koroziju i zaštićena od strane IMI Hydronic Engineering. Označavanje: Telo: TA, PN 20/150, DN i veličina u inčima. Ručica: Tip ventila i DN. Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.