http___www.imi-hydronic.com_hr_products-solutions_Balancing-and-control_Regulacijski-ventili_Balansirajui-i-regulacijski-ventili_TA-Modulator__1.xml
1.1 2.1 2.2 2.3 2.4 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 23.1 25.1 26.1 26.2 27.1 28.1 28.2 31.1 31.2 32.1 33.1 34.1 35.1 40.1 41.1 42.1 42.2 43.1 43.2 44.1 45.1 46.1 49.1 50.1 50.2 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 59.1 60.1 61.1 62.1 63.1 64.1 65.1 66.1 67.1 68.1 69.1 71.1 72.1 73.1 74.1 75.1 75.2
Pressure independent balancing and control valve for modulating control The new uniquely shaped EQM characteristics provide highly precise temperature control. The valve is compatible with linear proportional or 3-point actuators. A built-in differential pressure controller provides high control authority, control stability and automatic limitation of design flow. Measurement of flow and available pressure enables system optimisation and diagnostics. Key features Precise temperature control Uniquely shaped EQM characteristic provides an up to 6 times larger operating stroke than linear valves. Quick hydronic balancing Automatic flow limitation when actuator is fully open protects entire system against overflows. Easy troubleshooting Flow and differential pressure measuring helps to reduce pump consumption and provides all necessary data for system diagnostics. High reliability AMETAL® and stainless steel guarantees high corrosion resistance and reduces the risk of leakage. Technical description Application: Heating and cooling systems. Functions: Control (EQM) Pre-setting (max. flow) Differential pressure control Measuring (AH, T, q) Shut-off (for isolation during system maintenance – see also Leakage rate) Dimensions: Pressure class: Differential pressure (ApV): Max. differential pressure (ApVmax): 400 kPa = 4 bar Min. differential pressure (ApVmin): (Valid for position 10, fully open. Other positions will require lower differential pressure, check with the software HySelect.) ApVmax = The maximum allowed pressure drop over the valve, to fulfill all stated performances. ApVmin = The minimum recommended pressure drop over the valve, for proper differential pressure control. Flow range: The flow (qmax) can be set within the range: qmax = l/h at each setting and fully open valve plug. Temperature: Max. working temperature: 90°C Min. working temperature: -10°C Media: Water or neutral fluids, water-glycol mixtures. Lift: Leakage rate: Leakage flow ≤ 0,01% of max. qmax (setting 10) and correct flow direction. (Class IV according to EN 60534-4). Characteristics: Uniquely shaped EQM, best suited for modulating control. Material: Valve body: AMETAL® Valve insert: AMETAL® and PPS Valve plug: Stainless steel Spindle: Stainless steel Spindle seal: EPDM O-ring Ap insert: PPS Membrane: EPDM and HNBR Springs: Stainless steel O-rings: EPDM AMETAL® is the dezincification resistant alloy of IMI Hydronic Engineering. Marking: TA, IMI, PN 16, DN and flow direction arrow. Grey handwheel and black identification ring on measuring point: TA-Modulator and DN. Connection: Male thread according to ISO 228. Connection to actuator: Actuators: DN 15-20: TA-Slider 160, EMO TM DN 25-32: TA-Slider 160 See separate information on EMO TM and TA-Slider 160. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 2.4 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 23.1 25.1 26.1 27.1 30.1 30.2 31.1 32.1 33.1 34.1 39.1 40.1 41.1 42.1 43.1 44.1 45.1 48.1 49.1 49.2 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 59.1 60.1 61.1 62.1 63.1 64.1 65.1 66.1 67.1 68.1 70.1 71.1 72.1 73.1 74.1 74.2
Regulacijsko balansirajući ventil neovisan o promjeni dinamičkog tlaka, za modulacijsku regulaciju Nove, jedinstveno oblikovane EQM karakteristike omogućavaju preciznu regulaciju temperature. Ventil je kompatibilan s linearno proporcionalnim ili 3-položajnim pogonima. Ugrađen regulator vođen diferencijalnim tlakom omogućava visok autoritet regulacijskog ventila, stabilnost regulacije i automatsko ograničenje projektiranog protoka. Mjerenje protoka i raspoloživog tlaka omogućava optimalizaciju i dijagnostiku sustava. Glavne značajke Precizna regulacija temperature Jedinstveno oblikovane EQM karakteristike omogućavaju do 6 puta veće radne hodove u odnosu na linearne ventile. Brzo balansiranje sustava toplovodnog grijanja i hlađenja Sustav se štiti od prekoračenja protoka automatskim ograničenjem protoka dok je pogon potpuno otvoren. Jednostavno pronalaženje i otklanjanje smetnji u radu Mjerenjem protoka i diferencijalnog tlaka postiže se smanjenje potrošnje struje crpke i dobivaju se svi potrebni podaci za dijagnostiku sustava. Visoka pouzdanost AMETAL® i nehrđajući čelik garantiraju visoku otpornost na koroziju i smanjuju rizik od curenja. Tehnički opis Primjena: Sustavi grijanja i hlađenja. Funkcije: Regulacija (EQM) Predpodešavanje (maks. protok) Kontrola diferencijalnog tlaka Mjerenje (AH, T, q) Zaporna funkcija (za odvajanje tijekom održavanja sustava – vidi također u Nepropusnost) Dimenzije: Razred tlaka: Diferencijalni tlak (ApV): Max. diferencijalni tlak (ApVmax): 400 kPa = 4 bar Min. diferencijalni tlak (ApVmin): (Vrijedi za poziciju 10, potpuno otvoreno. Ostale pozicije zahtijevaju manji diferencijalni tlak, provjeriti u programu HySelect.) ApVmax = Maksimalno dozvoljeni pad tlaka na ventilu, kako bi zadovoljili navedene vrijednosti. ApVmin = Minimalno preporučeni pad tlaka na ventilu, za ispravnu kontrolu diferencijalnog tlaka. Raspon protoka: Protok (qmax) može biti prednamješten u rasponu: qmax = l/h za svaku prednamještenu poziciju i potpuno otvorenom ventilu. Temperatura: Max. radna temperatura: 90°C Min. radna temperatura: 0°C Radni medij: Voda ili neutralne tekućine, mješavine vode i glikola. Hod: Nepropusnost: Propusnost ≤ 0,01% od max. qmax (pozicija 10) i ispravan smjer protoka. (Klasa IV prema EN 60534-4). Karakteristike: Jedinstveno oblikovane EQM karakteristike, aliprilagođenezamodulacijskukontrolu. Materijal: Kućište ventila: AMETAL® Uložak ventila: AMETAL® i PPS Klip ventila: Nehrđajući čelik Vreteno: Nehrđajući čelik Brtva vretena: EPDM O-brtveni prsten Ap uložak: PPS Membrana: EPDM i HNBR Opruge: Nehrđajući čelik O-brtveni prsteni: EPDM AMETAL® je IMI Hydronic Engineering legura otporna na decinifikaciju. Označavanje: TA, IMI, PN 16, DN i smjer protoka. Sivi rukohvat i crni identifikacijski prsten na mjernom priključku: TA-Modulator i DN. Priključak: Vanjski navoj prema ISO 228. Priključak na pogon: Pogoni: DN 15-20: TA-Slider 160, EMO TM DN 25-32: TA-Slider 160 Vidjeti zasebnu informaciju na EMO TM i TA-Slider 160. Proizvodi, tekstovi, fotografije, crteži i dijagrami u ovoj brošuri podložni su promjenama od strane IMI Hydronic Engineering, bez prethodne obavijesti ili obrazloženja. Za više informacija o proizvodima i specifikacijama molimo posjetite nas na www.imi-hydronic.com.