http___www.imi-hydronic.com_hr_products-solutions_Balancing-and-control_Regulacijski-ventili_Balansirajui-i-regulacijski-ventili_TA-COMPACT-P__1.xml
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 14.1 16.1 17.1 17.2 18.1 18.2 21.1 21.2 22.1 23.1 24.1 25.1 27.1 32.1 33.1 34.1 35.1 35.2 36.1 36.2 37.1 38.1 39.1 40.1 41.1 42.1 42.2 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 58.2 59.1 60.1 61.1 63.1 64.1 65.1 65.2
Pressure independent balancing and control valve (PIBCV) The pressure independent balancing and control valve TA-COMPACT-P ensures optimum performance over a long life. Adjustable maximum flow enables design flow and eliminates over flows for accurate hydronic control. The TA-COMPACT-P together with our balancing instruments enables advanced measuring and diagnostics. Technical description Application: Heating and cooling systems. Functions: Control Pre-setting (max. flow) Differential pressure control Measuring (AH, T, q) Shut-off (for isolation during system maintenance – see also Leakage rate) Dimensions: Pressure class: Differential pressure (ApV): Max. differential pressure (ApVmax): 400 kPa = 4 bar Min. differential pressure (ApVmin): (Valid for position 10, fully open. Other positions will require lower differential pressure, check with the software HySelect.) ApVmax = The maximum allowed pressure drop over the valve, to fulfill all stated performances. ApVmin = The minimum recommended pressure drop over the valve, for proper differential pressure control. Flow range: The flow (qmax) can be set within the range: DN 15 LF: 44 - 245 l/h qmax = l/h at each setting and fully open valve plug. LF = Low flow Temperature: Max. working temperature: 90°C Min. working temperature: 0°C Media: Water or neutral fluids, water-glycol mixtures. Lift: 4 mm Leakage rate: Leakage flow ≤ 0,01% of max. qmax (setting 10) and correct flow direction. (Class IV according to EN 60534-4). Characteristics: Linear, best suited for on/off control. Material: Valve body: AMETAL® Valve insert: AMETAL® Valve plug: Stainless steel Spindle: Stainless steel Spindle seal: EPDM O-ring Ap insert: PPS Membrane: EPDM and HNBR Springs: Stainless steel O-rings: EPDM AMETAL® is the dezincification resistant alloy of IMI Hydronic Engineering. Marking: TA, IMI, PN 16, DN and flow direction arrow. Grey handwheel: TA-COMPACT-P and DN. For low flow version also LF. Connection: Male thread according to ISO 228. Connection to actuator: Actuators: See separate information on EMO T. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 14.1 16.1 17.1 18.1 21.1 21.2 22.1 23.1 24.1 25.1 27.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 42.2 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 58.2 59.1 60.1 61.1 63.1 64.1 65.1 65.2
Regulacijsko balansirajući ventil neovisan o promjeni dinamičkog tlaka (PIBCV) Regulacijsko balansirajući ventil neovisan o promjeni dinamičkog tlaka TA-COMPACT-P osigurava optimalne perfomanse u dugom vremenskom periodu. Podesiva vrijednost maksimalnog protoka omogućava projektirani protok i spriječava prekoračenje protoka za preciznu hidroničku kontrolu. TA-COMPACT-P zajedno s našim mjernim uređajima omogućava napredno mjerenje i dijagnostiku. Tehnički opis Primjena: Sustavi grijanja i hlađenja. Funkcije: Regulacija Predpodešavanje (maks. protok) Kontrola diferencijalnog tlaka Mjerenje (AH, T, q) Zaporna funkcija (za odvajanje tijekom održavanja sustava – vidi također u Nepropusnost) Dimenzije: Razred tlaka: Diferencijalni tlak (ApV): Max. diferencijalni tlak (ApVmax): 400 kPa = 4 bar Min. diferencijalni tlak (ApVmin): (Vrijedi za poziciju 10, potpuno otvoreno. Ostale pozicije zahtijevaju manji diferencijalni tlak, provjeriti u programu HySelect.) ApVmax = Maksimalno dozvoljeni pad tlaka na ventilu, kako bi zadovoljili navedene vrijednosti. ApVmin = Minimalno preporučeni pad tlaka na ventilu, za ispravnu kontrolu diferencijalnog tlaka. Raspon protoka: Protok (qmax) može biti prednamješten u rasponu: DN 15 LF: 44 - 245 l/h qmax = l/h za svaku prednamještenu poziciju i potpuno otvorenom ventilu. LF = mali protok Temperatura: Max. radna temperatura: 90°C Min. radna temperatura: 0°C Radni medij: Voda ili neutralne tekućine, mješavine vode i glikola. Hod: 4 mm Nepropusnost: Propusnost ≤ 0,01% od max. qmax (pozicija 10) i ispravan smjer protoka. (Klasa IV prema EN 60534-4). Karakteristike: Linearna, ali prilagođena za on/off kontrolu. Materijal: Kućište ventila: AMETAL® Uložak ventila: AMETAL® Klip ventila: Nehrđajući čelik Vreteno: Nehrđajući čelik Brtva vretena: EPDM O-brtveni prsten Ap uložak: PPS Membrana: EPDM i HNBR Opruge: Nehrđajući čelik O-brtveni prsteni: EPDM AMETAL® je IMI Hydronic Engineering legura otporna na decinifikaciju. Označavanje: TA, IMI, PN 16, DN i smjer protoka. Sivi rukohvat: TA-COMPACT-P i DN. Za verziju s malim protokom LF. Priključak: Vanjski navoj prema ISO 228. Priključak na pogon: Pogoni: Vidjeti zasebnu informaciju na EMO T. Proizvodi, tekstovi, fotografije, crteži i dijagrami u ovoj brošuri podložni su promjenama od strane IMI Hydronic Engineering, bez prethodne obavijesti ili obrazloženja. Za više informacija o proizvodima i specifikacijama molimo posjetite nas na www.imi-hydronic.com.