http___www.imi-hydronic.com_srb-rs_products-solutions_Termostatska_kontrola_Termostatske-glave-i-radijatorski-ventili_Termostatski-radijatorski-ventili_Eclipse__1.xml
1.1 2.1 2.2 2.3 2.4 2.5 2.6 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 21.1 23.1 24.1 24.2 25.1 25.2 26.1 27.1 28.1 29.1 30.1 31.1 32.1 32.2 33.1 34.1 35.1 36.1 37.1 37.2 38.1 39.1 40.1 41.1 43.1 44.1 44.2 45.1 46.1 47.1 48.1 49.1 50.1 51.1 52.1 52.2 53.1 54.1 55.1 56.1 57.1 57.2
Thermostatic valve and lockshield with tube-bend for the installation as angle form or axial form with press- or sliding sleeve The IMI Heimeier Kit Hydrocâblé with thermostatic valve and lockable lockshield is applied in two-pipe pumped hot-water heating systems with normal to high temperature spread. The continuously presetable V-exact II thermostatic valve body has a wide flow range as well as optimised noise behaviour and very tight flow tolerances. It is possible to flow the thermostatic valve and lockshield from both sides. Thus, it is suitable for mounting as an angle or axial form. Versions with press connection or sliding sleeve allow an easy tube connection. Because of its sets with different tube-bend lengths, the IMI Heimeier Kit Hydrocâblé fits all panel radiators. Key features Angle or axial connection with one kit for various installation options Pipe connection with press- or sliding sleeve practical and quick to install "V-exact II" precision-presetting for precise balancing Various pipe-bend lengths this fits all panel radiators Technical description Applications area: Heating systems Function: Control Stepless presetting Shut-off Dimensions: Pressure class: Temperature: Max. working temperature: 90 °C Min. working temperature: -10 °C Materials: Valve bodies: Brass O-rings: EPDM rubber Valve disc thermostatic valve body: EPDM rubber Return spring: Stainless steel Valve inserts: Brass, PPS (polyphenylsulphide) Spindle: Niro-steel spindle with double O-ring sealing. The outer O-ring can be replaced under pressure. Pipe-bend: Copper, nickel-plated Surface treatment: Valve body and fittings are nickel-plated. Marking: TAH, flow direction arrow. II-Designation. White protection cap. Pipe connection: With press sleeve or sliding sleeve for PER-pipe Ø 12 x 1,1. Connection to thermostatic head: Thermostatic head K: Liquid-filled thermostat. High pressure power, lowest hysteresis, optimal closing time. Stable control behavior even in the case of small calculated p-band variation (<1K). Meet all requirements of the German EnEV and DIN V 4701-10. White cover RAL 9016 printed with scale. Valve stroke limiter. With two energy saving clips. Setting numbers 1 to 5. Frost protection. Max. sensor temperature 50°C (122°F). Hysteresis 0.15 K. Water temperature influence 0.3 K. Differential pressure influence 0.2 K. Closing time 19 min. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 2.4 2.5 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 23.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 49.2 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 59.1 59.2
Termostatski radijatorski ventil sa automatskim ograničenjem protoka Termostatski radijatorski ventil Eclipse ima jedinstveni ograničivač protoka koji eliminiše bilo kakvo prekoračenje protoka. Zahtevani protok se podešava direktno na ventilu. Podešeni protok neće biti veći čak ni kada postoje znatne promene u instalaciji bilo da neki ventili zatvaraju bilo da je reč o jutarnjem startovanju sistema grejanja. Ventil reguliše protok nezavisno od promene diferencijalnog pritiska. Prema tome, nisu potrebni komplikovani proračuni za određivanje pozicije predregulacije. Ključne karakteristike Integrisani ograničivač protoka Ne dozvoljava prekoračenje protoka Jednostavno podešavanje Kako bi se postigao projektovani protok Opseg protoka od 10 do 150 l/h Za veću fleksibilnost Sva tela ventila označena sa ‘’II’’ mogu biti modifikovana kao Eclipse Pr: Calypso exact, Calypso, Mikrotherm F, Multilux, Multilux 4-Set Perfect for renovation Standard dimensions and easy flow sizing Tehnički opis Namena: Sistemi grejanja. Funkcija: Kontrola Regulacija protoka Zatvaranje Dimenzije: Nazivni pritisak: Temperatura: Max. radna temperatura: 120°C, sa zaštitnom kapom ili aktuatorom 100°C. Min. radna temperatura: -10°C Opseg protoka: Protok se može predregulisati u opsegu: 10-150 l/h. Podešavanje protoka do 150 l/h. (Max. nominalni ptorok qmN na 10 kPa prema EN 215: 115 l/h) Diferencijalni pritisak (ApV): Max. differencijalni pritisak: Min. differencijalni pritisak: 10 – 100 l/h = 10 kPa 100 – 150 l/h = 15 kPa Materijal: Telo ventila: Mesing O-prsten: EPDM guma Disk ventila: EPDM guma Povratna opruga: Nerđajući čelik Uložak ventila: Mesing, PPS (polyphenylsulphide) Ceo termostatski uložak može se zameniti korišćenjem IMI Heimeier alata bez pražnjenja instalacije. Vreteno: Niro čelik sa duplim O-prstenastim zaptivanjem. Površinska obrada: Telo ventila i fiting su niklovani. Označavanje: THE, DN, oznaka zemlje, smer protoka i KEYMARK-oznaka. II+ oznaka. Narandžasta zaštitna kapa. Standardi: Telo ventila prema sledećim zahtevima: – KEYMARK sertifikovano i testirano prema DIN EN 215. Cevni priključci: Unutrašnji navoj je projektovan za povezivanje na cevi sa navojem, ili u kombinaciji sa kompresionim spojnicama, na bakarne ili precizne čelične cevi. U kombinaciji sa duplom zateznom spojnicom pogodan je za povezivanje na višeslojne cevi. Priključak na termostatsku glavu i aktuator: IMI Heimeier M30x1.5 Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.