http___www.imi-hydronic.com_srb-rs_products-solutions_Balansiranje_i_kontrola_Regulaciioni-ventili-i-Pogoni_Kombinovani-kontrolni-i-balansni-ventili-za-male-terminalne-potroae_TA-COMPACT-T__1.xml
1.1 2.1 3.1 4.1 5.1 6.1 7.1 8.1 9.1 11.1 12.1 15.1 16.1 16.2 17.1 17.2 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 38.2
Butterfly valves, DN 50-350, spheroidal graphite, with high speed actuators Control and shut-off butterfly valves for open and closed circuits with electric quater-turn actuator for HVAC systems, sanitary and industrial plants. Technical description Application: Chilled-, hot- and industrial water, low pressure steam, water with antifreeze and anticorrosive compounds (approx. 50%): glycol, glycerine, ethyl alcohol, propylene dichloride alcohol, mono ethyl alcohol, ethyl, methyl alcohol, antidichloride fluor methane® N+L. Function: DR16 EVSA: Shut-off DR16 EVSR: Control Dimensions: Pressure class: DN 50-125: PN 6 - PN 16 (PN 6 please state when ordering) Temperature: Max. working temperature: 110°C Min. working temperature: -10°C For lower and higher temperatures please contact IMI Hydronic Engineering. Material: Body: Spherioidal graphite EN-JS1030 Seat ring: EPDM Flap: CrNi-steel 1.4581 Shaft: CrNi-steel 1.4021 Shaft sealing: EPDM Marking: DN and PN. Flow direction: Optionally from both side. Connection type: Flangeless wafer type PN 6-16. Face to face: According to EN 558-1 basic series 20. Leakage rate: EN 1349 – seat-leakage VI G1 (tight sealing). Valve variants: - Technical silicon free version. - Special varnish, max. 80°C The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 2.4 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 14.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 40.1 41.1 42.1 42.2
Kontrolni ventil sa regulatorom povratne temperature za rashladne sisteme TA-COMPACT-T je on/off kontrolni ventil sa ugrađenim regulatorom povratne temperature koji osigurava zahtevanu povratnu temperaturu iz terminalnih jedinica u rashladnim sistemima. Pravilno podešena povratna temperatura zadržava visoku efikasnost celog sistema i štiti čilere od sindroma niske povratne temperature. Hidronično balansiranje bazirano na osnovu regulacije povratne temperature ograničava protoke i pruža uštedu energije. Merni nipl omogućava merenje temperature. Tehnički opis Namena: Rashladni sistemi sa promenljivim protokom. Ugradnja na povratnoj cevi. Funkcija: Kontrola Regulacija povratne temperature Merenje temperature Zatvaranje Dimenzije: Nazivni pritisak: Temperaturni opseg: Povratna temperatura: 8°C - 18°C Fabrički predpodešena vrednost: 12°C Temperatura: Max. radna temperatura: 50°C Min. radna temperatura: -10°C Radni fluid: Voda ili neutralne tečnosti, mešavine vode i glikola. (za ostale radne fluide kontaktirati IMI Hydronic Engineering.) Hod: 4 mm Materijal: Kućište: Na koroziju otporna legura bakra O-rings: EPDM Zaptivka sedišta ventila: EPDM Povratna opruga: Nerđajući čelik Uložak ventila: Mesing Vreteno: Čelično vreteno sa duplim O-ring zaptivanjem. Ručica: ABS Oznaka: TAH, PN 16, DN i strelica smera strujanja. Crna šatitna kapa. Priključak za pogon: Pogoni: Pogledajte više informacija u EMO T-u. Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.