http___www.imi-hydronic.com_hr_products-solutions_Pressurisation-and-Water-quality_Odravanje-tlaka_Ureaj-za-odravanje-pritiska-s-kompresorima_Compresso-Connect-F__1.xml
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 9.2 10.1 10.2 11.1 12.1 12.2 13.1 13.2 14.1 15.1 16.1 18.1 19.1 20.1 21.1 22.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 38.2 39.1 39.2 40.1 41.1 41.2 42.1 42.2 43.1 44.1 44.2 45.1 45.2 46.1 47.1 47.2 48.1 49.1 50.1 51.1 52.1 53.1 54.1 54.2 55.1 55.2
For heating systems up to 12 MW and cooling systems up to 18 MW Compresso is a precision pressurisation system with compressors for heating, solar and chilled water systems. It is especially suitable in situations where compactness and precision are required. The system capacity range lies between pressurisation with Statico and Transfero. The new BrainCube Connect control panel allows a new level of connectivity, enabling communication with the BMS system, other BrainCubes as well as remote operation of the pressurisation system through live viewing. Technical description – Control unit TecBox Applications: Heating, solar and chilled water systems. For systems according to EN 12828, SWKI 93-1, solar systems according to EN 12976, ENV 12977 with on-site excess temperature protection in case of power blackout. Pressure: Min. admissible pressure, PSmin: 0 bar Max. admissible pressure, PS: see Articles Temperature: Max. admissible ambient temperature, TA: 40°C Min. admissible ambient temperature, TAmin: 5°C Accuracy: Precision pressure maintenance ±0,1 bar. Supply voltage: Electric load: See Articles. Enclosure class: IP 22 according to EN 60529 Silent-run Compressors: Material: Main materials include steel, brass and bronze. Transportation and storing: In frostless, dry places. Approvals: CE-tested according to the requirements of the European Directives 2004/108/EC, 2006/95/EC. Technical description – Expansion vessels Applications: Only together with Control unit TecBox. See Applications under Technical description - Control unit TecBox. Media: Non-aggressive and non-toxic system media. Addition of antifreeze agent up to 50%. Pressure: Min. admissible pressure, PSmin: 0 bar Max. admissible pressure, PS: see Articles Temperature: Max. admissible bag temperature, TB: 70°C Min. admissible bag temperature, TBmin: 5°C For PED purposes: Max. admissible temperature, TS: 120°C Min. admissible temperature, TSmin: -10°C Material: Steel. Color beryllium. Airproof butyl bag according to EN 13831. Transportation and storing: In frostless, dry places. Approvals: CE design-tested according to PED/DEP 97/23/EC. Warranty: Compresso CG, CG... E: 5-year warranty for the airproof butyl bag. Compresso CU, CU... E: 5-year warranty for the vessel.
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 51.1 52.1 53.1 54.1 55.1 56.1 56.2
For heating systems up to 4 MW and cooling systems up to 6 MW Compresso je uređaj za precizno održavanje tlaka sa kompresorima u sustavima grijanja, hlađenja i solarnim sustavima. Posebno je pogodan za korištenje gdje se zahtijeva kompaktnost i preciznost. Po kapacitetu otplinjavanja nalazi se između Statico i Transfero uređaja. The new BrainCube Connect control panel allows a new level of connectivity, enabling communication with the BMS system, other BrainCubes as well as remote operation of the pressurisation system through live viewing. Tehnički opis – Regulacijska jedinica TecBox Primjene: Sustavi grijanja, hlađenja i solarni sustavi. Za sustave prema EN 12828, SWKI 93-1, solarne sustave prema EN 12976, ENV 12977 sa zaštitom od nekontroliranog rasta temperature u slučaju nestanka struje. Tlak: Min. dopušteni tlak, PSmin: 0 bar Max. dopušteni tlak, PS: ovisno o tipu Temperature: Max. dopuštena temperatura okoline, TA: 40°C Min. dopuštena temperatura okoline, TAmin: 5°C Točnost: Precizno održavanje tlaka ±0,1 bar. Napon: Strujno opterećenje: Ovisno o tipu. Klasa zaštite: IP 22 prema EN 60529 Razina buke: 59 dB(A) /1bar Materijal: Olovo, mesing i aluminij Transport i skladištenje: Na suhom mjestu, zaštićeno od smrzavanja. Atestirano: CE-atestirano prema zahtjevima evropskih normi 2004/108/EC, 2006/95/EC. Tehnički opis – Ekspanzijske posude Primjene: Samo uz regulacijsku jedinicu TecBox. Vidi primjene pod tehničkim opisom – Regulacijska jedinica TecBox. Medij: Neagresivni i netoksični mediji. Dodatak antifriza do 50%. Tlak: Min. dopušteni tlak, PSmin: 0 bar Max. dopušteni tlak, PS: ovisno o tipu Temperatura: Max. dopuštena temperature mjeha, TB: 70°C Min. dopuštena temperature mjeha, TBmin: 5°C For PED purposes: Max. dopuštena temperatura, TS: 120°C Min. dopuštena temperatura, TSmin: -10°C Materijal: Olovo. boja berilij. Nepropusni mjeh iz butila prema EN 13831 i Pneumatex internom standardu. Transport i skladištenje: Na suhom mjestu, zaštićeno od smrzavanja. Atestirano: CE-atestirano prema PED/DEP 97/23/EC. Jamstvo: Compresso CG, CG...E: 5-godišnje jamstvo na nepropusni mjeh iz butila. Compresso CU, CU...E: 5-godišnje jamstvo na posudu. Proizvodi, tekstovi, fotografije, crteži i dijagrami u ovoj brošuri podložni su promjenama od strane IMI Hydronic Engineering, bez prethodne obavijesti ili obrazloženja. Za više informacija o proizvodima i specifikacijama molimo posjetite nas na www.imi-hydronic.com.