http___www.imi-hydronic.com_srb-rs_products-solutions_pressurisation-and-water-quality_Kvalitet-vode_Automatski-odzrani-ventil_Zeparo-Cyclone__1.xml
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 7.2 8.1 8.2 9.1 10.1 11.1 12.1 12.2 13.1 14.1 14.2 15.1 16.1 16.2 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 24.2
Pressure stabilisation for potable water Expansion vessels with fixed gas cushion for drinking water systems. The airproof butyl bag, made from special butyl rubber and suitable for drinking water, is legendary. Together with the full flowthrough, the vessels offer a unique standard of hygiene. Technical description Application: Potable water heating systems, pressure-boosting systems, max. chloride content 125 mg/l (70 °C), 250 mg/l (45 °C). Pressure: Min. admissible pressure, PSmin: 0 bar Max. admissible pressure, PS: see Articles Limit value for the pressure maintenance (P0), factory setting: 4 bar Temperature: Max admissible temperature, TS: 120 °C Min. admissible temperature, TSmin: -10 °C Max admissible bag temperature, TB: 70 °C Min. admissible bag temperature, TBmin: 5 °C Material: Steel. Colour beryllium. All metallic parts in contact with water in stainless steel. Transportation and storing: In frostless, dry places. Approvals: Drinking water inspection according to the rules of SVGW, PZH. CE design-tested according to PED/DEP 97/23/EC. Local drinking water legislations apply. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 7.2 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 23.2
Automatski separator nečistoća Sveobuhvatni asortiman proizvoda za odvajanje taloga u vodenim grejnim i rashladnim sistemima. Raznovrsnost primene kao i njihova modularna konstrukcija su jedinstveni. Nova ciklonska tehnologija – podizanje efikasnosti separacije nečistoća na sledeći nivo. Tehnički opis Namena: Grejni i sistemi hladne vode. Medij: Neagresivan, netoksičan fluid. Dodatak antifriza do 50%. Pritisak: Max. dopušteni pritisak, PS: 10 bar Min. dopušteni pritisak, PSmin: 0 bar Temperatura: Max. dopuštena temperatura, TS: 120 °C Min. dopuštena temperatura, TSmin: -10 °C Materijal: Kućište ventila: Mesing Uložak ciklona: PPS Ryton Zaptivke: EPDM Označavanje: Telo: PN, DN, i smer protoka. Etiketa sa TS i TSmin. Transport i skladištenje: Na suvim mestima. Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.