http___www.imi-hydronic.com_hr_products-solutions_Thermostatic-control_Termostatske-glave-i-radijatorski-ventili_Termostatski-radijatorski-ventil_A-exact__1.xml
1.1 2.1 2.2 2.3 2.4 2.5 2.6 2.7 2.8 2.9 2.10 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 12.1 14.1 15.1 15.2 16.1 16.2 17.1 18.1 20.1 21.1 22.1 22.2 23.1 24.1 24.2 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 41.2 42.1 43.1 44.1 45.1 46.1 47.1 47.2 47.3 47.4 47.5 47.6 47.7 48.1 49.1 49.2
with two-point connection, angle and straight type, for R 1/2 and G 3/4 connection, with automatic flow limitation The Multilux 4-Eclipse-Set is connected in 2-pipe systems to radiators with a lower 2-point connection such as bathroom radiators, design radiators, universal radiators or radiators with integrated valves. The valve has a unique integrated flow limiter that eliminates over flows. The required flow rate can be adjusted with one twist directly at the valve. The adjusted flow will not be exceed even if there are load changes in the system, due to other valves closing or during morning start up. The valve controls the flow rate independently from differential pressure. Therefore, complicated calculations to determine settings are not necessary. Centre-to-centre distance of connections 50 mm. The Multilux 4-Eclipse-Set is suitable for installation as angle or straight form. Thermostatic insert and shut-off insert are interchangeable. Therefore the valve is suitable for installation both left and right side of the radiator. Technical description Applications area: 2-pipe heating systems Function: Control Flow limitation Shut-off Dimensions: Pressure class: Temperature: Max. working temperature: 120 °C, with cover 90 °C. Min. working temperature: –10 °C Flow range: The flow can be stepless pre-set within the range: Delivery setting 150 l/h. Differential pressure (ApV): Max. differential pressure: 60 kPa Min. differential pressure: 10 – 100 l/h = 10 kPa 100 – 150 l/h = 15 kPa Materials: Valve body: Corrosion resistant Gunmetal. O-rings: EPDM rubber Valve disc: EPDM rubber Return spring: Stainless steel Valve insert: Brass, PPS (polyphenylsulphide) Spindle: Niro-steel spindle with double O-ring sealing. Cover: ABS Surface treatment: Valve body gunmetal, fittings are nickel-plated. Marking: THE and II+ Designation. Protection cap orange. Radiator connection: Adapters for R1/2 and G3/4, for radiator connections. Tolerance compensation ±1,0 mm with special union nuts and flexible flat seal system for installation free of tension. Pipe connection: G3/4 male thread for compression fittings for plastic, copper, precision steel or multi-layer pipe. Connection to thermostatic head and actuator: IMI Heimeier M30x1.5 Thermostatic head DX: Thermostatic head DX with closed graduation cap and liquidfilled thermostat. High actuating force, minimum hysteresis, optimum closing time. Stable control response even with minor calculated p-band variations (<1 K). Conforming to German EnEV and/or DIN V 4701-10. Setting numbers 1–5. Frost protection. Temperature range 6 °C to 28 °C. See technical leaflet “Thermostatic heads”. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 12.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 38.2 39.1 40.1 41.1 41.2
Termostatski radijatorski ventil s automatskom regulacijom protoka Termostatski radijatorski ventil A-exact ima integriran jedinstveni regulator protoka koji spriječava višak protoka. Željeni protok se može namjestiti direktno na ventilu zakretanjem. Namješteni protok neće biti premašen čak ni kod promjena opterećenja sustava, kada drugi ventili zatvaraju ili za vrijeme početka grijanja tijekom jutra. Tehnički opis Primjena: Sustavi grijanja Funkcije: Regulacija Regulacija protoka Zatvaranje Dimenzije: Razred tlaka: Temperatura: Max. radna temperatura: 90 °C Min. radna temperatura: 10 °C Diferencijalni tlak (ApV): Max. diferencijalni tlak: 60 kPa Min. diferencijalni tlak: 10 – 100 l/h = 10 kPa 100 – 150 l/h = 15 kPa Raspon protoka: Protok se može namiještati stupnjevito : 10-150 l/h. Tvorničko namještanje 150 l/h. Materijal: Kućište ventila: Bronca otporna na koroziju O-ring: EPDM guma Disk ventila: EPDM guma Povratna pruga: Nehrđajući čelik Umetak ventila: Brass, PPS (polifenilsulfid) Vreteno: Nehrđajući čelik s duplom O-ring brtvom. Površinska zaštita: Tijelo ventila je presvučeno niklom. Označavanje: TAH, DN i strelica smjera strujanja. Narančasta zaštitna kapa. Spajanje: Verzija s unutarnjim navojem je dizajnirana za spajanje na cijevni navoj, ili s kompresijskim fitingom, na bakrene precizne čelične cijevi i višeslojne cijevi (DN 15). Verzija s vanjskim navojem, u kombinaciji s prikladnim kompresijskim fitingom, omogućava spajanje na plastične cijevi. Spoj s termostatskom glavom i pogonom: IMI Heimeier M30x1.5 Proizvodi, tekstovi, fotografije, crteži i dijagrami u ovoj brošuri podložni su promjenama od strane IMI Hydronic Engineering, bez prethodne obavijesti ili obrazloženja. Za više informacija o proizvodima i specifikacijama molimo posjetite nas na www.imi-hydronic.com.