http___www.imi-hydronic.com_srb-rs_products-solutions_Balansiranje_i_kontrola_Regulatori-diferencijalnog-pritiska_Regulatori-diferencijalnog-pritiska_TA-PILOT-R__1.xml
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 17.1 20.1 21.1 21.2 22.1 22.2 23.1 24.1 25.1 26.1 26.2 27.1 28.1 28.2 29.1 30.1 31.1 31.2 32.1 33.1 34.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 43.2 44.1 45.1 46.1 47.1 47.2 47.3 48.1 48.2 51.1 51.2
Pressure independent balancing and control valve – DN 15-125 High-performing and compact, these pressure-independent control valves for variable flow heating and cooling systems are particularly effective in situations requiring high temperatures and/or pressure drops. They are also suitable for use on the secondary side in district heating and comfort cooling systems. Rust protection is assured due to the electrophoretically painted ductile iron body, while the plug delivers valve characteristic, suitable for modulating control. Key features Inline design Inline flow allows high pressure drops without noise. Adjustable flow Ensures the design flow. Adapters For use with most available actuators. Technical description Application: Heating and cooling systems. Functions: Differential pressure control over the built-in control valve and flow control. Dimensions: Pressure class: Differential pressure (ApV): Max. differential pressure: 1600 kPa = 16 bar (AHmax) Min. differential pressure: Low flow (LF): 24 kPa (AHmin) Normal flow (NF): 40 kPa (AHmin) High flow (HF): 80 kPa (AHmin) (Valid for max. position, fully open. Other positions will require lower differential pressure, check with the software HySelect.) Temperature: Max. working temperature: - with measuring points: 120°C - without measuring points: 150°C Min. working temperature: -10°C Media: Water or neutral fluids, water-glycol mixtures. Material: Valve body: Ductile iron EN-GJS-400 Diaphragms and gaskets: EPDM Valve plug: EPDM/Stainless steel Surface treatment: Electrophoretic painting. Marking: TA, DN, PN, Kvs, material and flow direction arrow. Connection: DN 15-50: Male threads according to EN-1092-2: 1997, type 16. Separate connections with ANSI flanges and UNC threads. DN 65-125: According to ASME/ANSI B 16.42 Class 150. Actuators: KTM 512 can be equipped with adapters for the most common actuators - see "Adapters for actuators". The max. lift of the actuator must be checked. In the case of a shorter lift the maximum achieved flow will be decreased. Consult your local sales office for details. Max. lift of the control valve: The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 2.4 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 20.1 21.1 22.1 24.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 61.1 62.1 63.1 64.1 65.1 65.2
Regulator diferencijalnog pritiska upravljan Pilot ventilom sa podesivim vrednostima TA-PILOT-R je regulator diferencijalnog pritiska visokih perfomansi konstruisan da održava stabilan diferencijalni pritisak na opterećenju. Sa vrhunskom tačnošću TA-PILOT-R pruža precizne i stabilne uslove za superiorni autoritet modulovano kontrolisanih kontrolnih ventila, dodatno on ograničava buku i pojednostavljuje balansnu proceduru. TA-PILOT-R je regulator diferencijalnog pritiska koji se instalira na povratni cevovod. Merni niplovi omogućuju merenje pritiska u cilju dijagnostike. Ključne karakteristike Jednostavno rukovanje i ugradnja Vrlo mala težina i mala ukupna dimenzija ventila. Precizna i stabilna regulacija diferencijalnog pritiska Neprevaziđena tačnost zahvaljujući novoj PILOT tehnologiji. Merenje i dijagnostika sistema Jedinstvene karakteristike za validaciju i bolje razumevanje ponašanja sistema za smanjenje potrošnje energije. Tehnički opis Namena: Sistemi grejanja i hlađenja. Ugradnja na povratnoj cevi. Funkcija: Regulacija diferncijalnog pritiska Predregulacija Ap na opterećenju (ApL) Merenje (ApL) Dimenzije: Klasa pritiska: PN 16 i PN 25 Maksimalni diferencijalni pritisak (ApV): Područje podešavanja: *) Fabrički podešene vrednosti Veličina propuštanja: Nepropusno zatvaranje Temperatura: Maksimalna radna temperatura: - sa mernim niplovima, standardna verzija: 120°C - sa mernim niplovima, dvostruko obezbeđenim: 150°C Min. radna temperatura: -20°C Radni fluid: Voda ili neutralne tečnosti, mešavine vode i glikola. (za ostale radne fluide kontaktirati IMI Hydronic Engineering.) Materijal: Kućište ventila: Nodularni liv EN-GJS-400 Kućište Pilot-a: AMETAL® O-rings: EDPM Zaptivka sedišta ventila: EPDM/Nerđajući čelik Mehanizam vretena ventila: Nerđajući čelik i mesing Membrana: EPDM Opruge: Nerđajući čelik Vijci i navrtke: Nerđajući čelik AMETAL® je legura otporna na koroziju i zaštićena od strane IMI Hydronic Engineering. Obrada površine: Kućište Pilot-a: Nije tretirano. Kućište ventila: elektroforetsko bojenje. Označavanje: TA, IMI, DN, PN, Kvs, Tmin/max, serijski broj, materijal kućišta ventila i strelica smera strujanja, nalepnica, ApL opseg. Identifikacija boje na vrhu pilota: 10-50 kPa: Plava 30-150 kPa: Narandžasta 80-400 kPa: Siva CE-označavanje: *) Označeno na kućištu. Prirubnice: PN 16, PN 25: Prirubnice prema EN-1092-2, tipa 21. Razmak čeonih površina, prema EN 558 serija 3. Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.