http___www.imi-hydronic.com_ba_products-solutions_Thermostatic-control_Termostati-i-pogoni_Termostati_Sobni-termostat__1.xml
1.1 2.1 3.1 4.1 5.1 5.2 6.1 7.1 7.2 7.3 8.1 9.1 9.2
Electro-mechanical room thermostat for thermal actuators The room thermostat is used in connection with the corresponding actuators in the fields of heating, ventilation and air-conditioning technology. Technical description The room thermostat is an electromechanical controller with two-point behaviour and is used in connection with e. g. thermal actuators to control the room temperature. The setting value can be set at between 5°C (41°F) and 30°C (86°F). This range can be adjusted as required by two setting rings in the setting value adjuster, e. g. min. 8°C (46°F), max. 23°C (73°F). Models with an operating voltage of 230 V and 24 V, with and without temperature set-back, each with change-over contact and thermal recirculation. For the model with temperature set-back (approx. 5 K (9°F)), a connection to the Thermostat P or an external switch clock is possible. An operating mode switch makes it possible to select from day, set-back or automatic mode. A control lamp indicates whether heating or cooling mode is active. The room thermostat is designed for installation on the wall and on switch boxes. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 3.1 4.1 5.1 5.2 6.1 7.1 7.2 7.3 8.1 9.1 9.2
Elektromehanički sobni termostat za termičke pogone Sobni termostati se koriste u sustavima grijanja i klimatizacije. Tehnički opis Sobni termostat je elektromehanički regulator s dvopoložajnom regulacijom i koristi se u kombinaciji s npr. termičkim pogonima, za regulaciju temperature prostorije. Vrijednost podešavanja može se namjestiti između 5 °C i 30 °C. Ovo se područje može podesiti prema potrebi pomoću dva prstena za namještanje, u podešivaču namještene vrijednosti, npr. min. 8 °C, max. 23°C. Modeli s radnim naponom, sa i bez temperaturne zadrške, svaki s prespojnim kontaktom i toplinskom recirkulacijom. Za model s temperaturnom zadrškom (cca. 5 K), moguće je spajanje na Thermostat P ili na vanjski uklopni sat. Režim rada prebacivanja omogućava biranje dana, zadrške ili automatskog načina rada. Kontrolna lampica pokazuje da li je aktivan režim grijanja ili hlađenja. Sobni termostat namijenjen je za instaliranje na zid i na rasklopni ormarić. Proizvodi, tekstovi, fotografije, crteži i dijagrami u ovoj brošuri podložni su promjenama od strane IMI Hydronic Engineering, bez prethodne obavijesti ili obrazloženja. Za više informacija o proizvodima i specifikacijama molimo posjetite nas na www.imi-hydronic.com.