http___www.imi-hydronic.com_hr_products-solutions_Balancing-and-control_Balansirajui-ventili_Balansirajui-ventili_STAD__1.xml
1.1 2.1 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 12.1 13.1 14.1 15.1 15.2 16.1 16.2 17.1 17.2 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 35.2
Ball valve – DN 10-50 Used in heating, cooling and tap water systems, the TA 500 is made of AMETAL®, minimising the risk of leakage and maximising product lifetime. Technical description Applications: Heating and cooling systems Tapwater systems Process systems where the media does not affect the incoming material. Function: Shut-off Dimensions: Pressure class: PN 25 (see below) Temperature: Max. working temperature: 185°C Min. working temperature: -50°C NOTE! DN 25-50 with smooth ends max working temperature 120°C and min working temperature -20°C irrespective of pressure. Pressure and temperature limits: Material: Body: AMETAL® Spindle: AMETAL® Ball: PTFE coated AMETAL® Spindle seal springs: Stainless steel Seal rings: PTFE Lever (blue): Epoxy painted die-cast aluminium. Reduction unit: Nickel-plated die-cast zinc alloy and handwheel (blue) of glass fibre re-inforced plastic. AMETAL® is the dezincification resistant alloy of IMI Hydronic Engineering. Surface treatment: Article No 58 500/58 503: Nickel-plated The rest of the product range not treated (yellow). Insulation: Use valves with a spindle extension or with a reduction unit when using insulation. Installation: The lever and the reduction unit can easily be removed if necessary. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 15.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 34.2
Balansirajući ventili STAD balansirajući ventil omogućava precizni učinak toplovodnog grijanja u impresivnom području primjena. Idealno je prikladan za primjenu na sekundarnom dijelu sustava grijanja i hlađenja i vodovodnih sustava. Tehnički opis Primjena: Sustavi grijanja i hlađenja Vodovodni sustavi Funkcije: Balansiranje Prethodno podešavanje Mjerenje Zatvaranje Ispuštanje (opcija) Dimenzije: Razred tlaka: Temperatura: Max. radna temperatura: 120°C Za više temperature do max. 150° molimo savjetovati se s najbližim zastupništvom. NAPOMENA: DN 25-50 s ravnim krajevima, max. radna temperatura 120°C. Min. radna temperatura: -20°C Materijal: Ventili su izrađeni od AMETAL® Brtva sjedišta ventila: Vreteno ventila s EPDM O-brtvenim prstenom. Brtva vretena: EPDM O-brtveni prsten. Ručno kolo: Poliamid i TPE. Ravni krajevi cijevi: Navojna spojnica: AMETAL® Brtvila (DN 25-50): EPDM O-brtveni prsten AMETAL® je IMI Hydronic Engineering legura otporna na decinifikaciju. Označavanje: Tijelo ventila: TA, PN 20/150, DN i veličina u inčima. Ručno kolo: Tip ventila i DN Proizvodi, tekstovi, fotografije, crteži i dijagrami u ovoj brošuri podložni su promjenama od strane IMI Hydronic Engineering, bez prethodne obavijesti ili obrazloženja. Za više informacija o proizvodima i specifikacijama molimo posjetite nas na www.imi-hydronic.com.