http___www.imi-hydronic.com_srb-rs_products-solutions_Termostatska_kontrola_Termostatske-glave-i-radijatorski-ventili_Termostatski-radijatorski-ventili_Eclipse__1.xml
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 22.2 23.1 23.2 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 38.2 39.1 40.1 40.2 41.1 42.1 42.2 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 59.1 60.1 60.2
Underfloor heating circuit manifold with flow meter Dynalux adjusts the flow rate in the individual heating circuits directly in l/min. Hydraulic balancing is achieved in simple operations. This makes Dynalux heating circuit manifolds a time and cost-saving solution especially for system commissioning. Key features Hydraulic balancing by direct setting of the flow rate Manifold made of stainless steel corrosion-resistant, durable and safe Thermostatic insert with double O-ring seal For durable and maintenance free operation Time and cost-saving commissioning solution Technical description Application: Floor heating systems Function: Individual room temperature control with actuator or thermostatic head Flow adjustment Shut off Filling Draining Flushing Venting Temperature: Max. working temperature: 60°C Min. working temperature: -5°C Flow range: The flow can be stepless pre-set within the range: 0-5 l/min Pressure class: PN 6 Material: Manifold: Stainless steel 1.4301 Connection fittings: Nickel-plated brass. Thermostatic insert: Brass O-rings: EPDM Valve disc: EPDM Spring: stainless steel Thermostatic insert: Brass Spindle: Niro-steel spindle with double O-ring seal. The outer O-ring is replaceable under pressure. Flow meter: Heat-resistant plastic and stainless steel. EPDM seals. Filling, draining, flushing and venting device: Nickel-plated brass and plastic. EPDM seals. Connection kits: The following manifold connection kits are available: - Connection kit 1 with Globo ball valves - Connection kit 2 with STAD balancing valve and Globo ball valve - Connection kit 3 with Zeparo Vent air separator in supply pipe and Zeparo Dirt sludge separator in return - Connection kit 4 with Globo ball valve, including spacer for heat meter in return and Globo ball valve with connection for direct measurement in supply and return pipe. - Connection kit 5 fixed value control station with high-efficiency pump for controlling the supply temperature. Pipe connection: Manifold with flat-sealing connection, 1" union nut. Heating circuit connection G 3/4 adaptor with Eurocone suitable for compression fittings for plastic, copper, precision steel and multi-layer pipe. See also accessories. Manifold boxes: Manifold boxes available as surface-mounted and flush-mounted versions. Marking: IMI Heimeier Connection to thermostatic head and actuator: IMI Heimeier M30x1.5 The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 2.4 2.5 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 23.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 49.2 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 59.1 59.2
Termostatski radijatorski ventil sa automatskim ograničenjem protoka Termostatski radijatorski ventil Eclipse ima jedinstveni ograničivač protoka koji eliminiše bilo kakvo prekoračenje protoka. Zahtevani protok se podešava direktno na ventilu. Podešeni protok neće biti veći čak ni kada postoje znatne promene u instalaciji bilo da neki ventili zatvaraju bilo da je reč o jutarnjem startovanju sistema grejanja. Ventil reguliše protok nezavisno od promene diferencijalnog pritiska. Prema tome, nisu potrebni komplikovani proračuni za određivanje pozicije predregulacije. Ključne karakteristike Integrisani ograničivač protoka Ne dozvoljava prekoračenje protoka Jednostavno podešavanje Kako bi se postigao projektovani protok Opseg protoka od 10 do 150 l/h Za veću fleksibilnost Sva tela ventila označena sa ‘’II’’ mogu biti modifikovana kao Eclipse Pr: Calypso exact, Calypso, Mikrotherm F, Multilux, Multilux 4-Set Perfect for renovation Standard dimensions and easy flow sizing Tehnički opis Namena: Sistemi grejanja. Funkcija: Kontrola Regulacija protoka Zatvaranje Dimenzije: Nazivni pritisak: Temperatura: Max. radna temperatura: 120°C, sa zaštitnom kapom ili aktuatorom 100°C. Min. radna temperatura: -10°C Opseg protoka: Protok se može predregulisati u opsegu: 10-150 l/h. Podešavanje protoka do 150 l/h. (Max. nominalni ptorok qmN na 10 kPa prema EN 215: 115 l/h) Diferencijalni pritisak (ApV): Max. differencijalni pritisak: Min. differencijalni pritisak: 10 – 100 l/h = 10 kPa 100 – 150 l/h = 15 kPa Materijal: Telo ventila: Mesing O-prsten: EPDM guma Disk ventila: EPDM guma Povratna opruga: Nerđajući čelik Uložak ventila: Mesing, PPS (polyphenylsulphide) Ceo termostatski uložak može se zameniti korišćenjem IMI Heimeier alata bez pražnjenja instalacije. Vreteno: Niro čelik sa duplim O-prstenastim zaptivanjem. Površinska obrada: Telo ventila i fiting su niklovani. Označavanje: THE, DN, oznaka zemlje, smer protoka i KEYMARK-oznaka. II+ oznaka. Narandžasta zaštitna kapa. Standardi: Telo ventila prema sledećim zahtevima: – KEYMARK sertifikovano i testirano prema DIN EN 215. Cevni priključci: Unutrašnji navoj je projektovan za povezivanje na cevi sa navojem, ili u kombinaciji sa kompresionim spojnicama, na bakarne ili precizne čelične cevi. U kombinaciji sa duplom zateznom spojnicom pogodan je za povezivanje na višeslojne cevi. Priključak na termostatsku glavu i aktuator: IMI Heimeier M30x1.5 Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.