http___www.imi-hydronic.com_srb-rs_products-solutions_pressurisation-and-water-quality_Kvalitet-vode_Automatski-odzrani-ventil_Zeparo-Cyclone__1.xml
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 11.2 12.1 12.2 13.1 14.1 14.2 15.1 15.2 16.1 17.1 17.2 18.1 18.2 19.1 20.1 21.1 22.1 23.1 23.2
Automatic air vents and separators (micro bubble, dirt, combined) Comprehensive range of products for venting and separation of micro bubbles, sludge, oxygen and magnetite in heating, solar and cooling water systems. The diversity of the applications as well as their modular construction is unique. The helistill separator – a brand new development – makes these products incredibly efficient. Technical description Application: Heating, solar and chilled water systems. Media: Non-aggressive and non-toxic system media. Addition of antifreeze agent up to 50%. Zeparo ZUR: Water without inhibitors. Pressure: Max. admissible pressure, PS: 10 bar Min. admissible pressure, PSmin: 0 bar Temperature: Max. admissible temperature, TS: 110 °C Min. admissible temperature, TSmin: -10 °C Zeparo ZUTS, ZUVS, ZUVLS solar: Max. admissible temperature, TS: 160 °C Min. admissible temperature, TSmin: -10 °C Material: Brass Transportation and storing: In frostless, dry places. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 7.2 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 23.2
Automatski separator nečistoća Sveobuhvatni asortiman proizvoda za odvajanje taloga u vodenim grejnim i rashladnim sistemima. Raznovrsnost primene kao i njihova modularna konstrukcija su jedinstveni. Nova ciklonska tehnologija – podizanje efikasnosti separacije nečistoća na sledeći nivo. Tehnički opis Namena: Grejni i sistemi hladne vode. Medij: Neagresivan, netoksičan fluid. Dodatak antifriza do 50%. Pritisak: Max. dopušteni pritisak, PS: 10 bar Min. dopušteni pritisak, PSmin: 0 bar Temperatura: Max. dopuštena temperatura, TS: 120 °C Min. dopuštena temperatura, TSmin: -10 °C Materijal: Kućište ventila: Mesing Uložak ciklona: PPS Ryton Zaptivke: EPDM Označavanje: Telo: PN, DN, i smer protoka. Etiketa sa TS i TSmin. Transport i skladištenje: Na suvim mestima. Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.