http___www.imi-hydronic.com_srb-rs_products-solutions_pressurisation-and-water-quality_Kvalitet-vode_Automatski-odzrani-ventil_Zeparo-Cyclone__1.xml
1.1 2.1 3.1 4.1 5.1 6.1 7.1 8.1 9.1 9.2
Retrofit thermostatic insert with presetting and thermostatic head Suitable for "Standard" thermostatic valve bodies with connection thread directly at the valve body made from late 1982 and "without" colored marking on the stuffing box. Technical description Retro S – Set with retrofit thermostatic insert and thermostatic head. The Retro S thermostatic insert with precision presetting is suitable for: "Standard" thermostatic valve bodies with connection thread directly at the valve body made from late 1982 and "without" colored marking on the stuffing box. The Retro S flow rates correspond to the flow rates of V-exakt valves to late 2011. With the fitting tool (Article No. 9721-00.000) the thermostatic inserts can be replaced without the need to drain off the system. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 7.2 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 23.2
Automatski separator nečistoća Sveobuhvatni asortiman proizvoda za odvajanje taloga u vodenim grejnim i rashladnim sistemima. Raznovrsnost primene kao i njihova modularna konstrukcija su jedinstveni. Nova ciklonska tehnologija – podizanje efikasnosti separacije nečistoća na sledeći nivo. Tehnički opis Namena: Grejni i sistemi hladne vode. Medij: Neagresivan, netoksičan fluid. Dodatak antifriza do 50%. Pritisak: Max. dopušteni pritisak, PS: 10 bar Min. dopušteni pritisak, PSmin: 0 bar Temperatura: Max. dopuštena temperatura, TS: 120 °C Min. dopuštena temperatura, TSmin: -10 °C Materijal: Kućište ventila: Mesing Uložak ciklona: PPS Ryton Zaptivke: EPDM Označavanje: Telo: PN, DN, i smer protoka. Etiketa sa TS i TSmin. Transport i skladištenje: Na suvim mestima. Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.