http___www.imi-hydronic.com_hr_znanje-alati_ta-scope__1.xml
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 16.2 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 44.2
Wireless transmission relay TA-SCOPE relay is a long-range transmission relay for measuring, balancing and diagnosing hydronic systems with multiple TA-SCOPE sensors. It is to be used in particular for applying the TA-Wireless method with the TA-SCOPE in large buildings. Key features Long range wireless transmission Range between two relays reaches 5 to 6 floors indoor. Easy configuration A software wizard integrated in the TA-SCOPE takes you step-by-step through an illustrated configuration process. Long-standing batteries Fully charged TA-SCOPE relays provide three days of power-efficient wireless performance. Technical description Applications: TA-SCOPE relay is a long-range transmission relay for measuring, balancing and diagnosing hydronic systems with multiple TA-SCOPE sensors. It is to be used in particular for applying the TA-Wireless method with the TA-SCOPE in large buildings. Configuration: In order to configure long-distance transmission with the optional TA-SCOPE Relays select Configure Relays in the Options menu. A software wizard takes you step-by-step through the configuration process. The option Add intermediate Relays allows adding more intermediate Relays to an existing relay configuration. Ambient temperature: During operation: 0°C – +40°C During charging: 0°C – +40°C During storage: -20°C – +60°C Humidity: Ambiant humidity: max 90% RH Battery capacity, operating and charge times: Capacity: 4 400 mAh Operating time: >25 h Charge time to full capacity: 6-7 h Remark: Replacing the battery by another type is strictly forbidden and could lead to an explosion. Wireless: Between two relays: 868 MHz – EC version. 915 MHz – FCC version. Range in open space: approx. 500 m. Range indoors: approx. 5-6 floors. Enclosure class: Colour: Black Charger: Output voltage: 5,2 V DC (minimum 5,0 V, maximum 5,3 V) Output current: Minimum 1 A. Isolation: Class II. Certification: IEC (868 MHz) and/or UL, CSA (915 MHz). Complying with the LPS (Low Power Source) regulation. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 3.1 3.2 3.3 4.1 5.1 6.1 7.1 8.1 8.2
U svom prvom izdanju TA-SCOPE je podignuo ljestvicu u hidroničkom balansiranju – a sada je ovaj jedinstveni instrument unaprijeđen sa još više karakteristika. TA-SCOPE omogućuje balansiranje KGH sustava brže, jednostavnije i precizinije, uz smanjenje utroška energije i troškova. Bez obzira koliko je objekt velik ili koliko je sustav kompleksan, potrebna je jedna osoba i jedan instrument TA-SCOPE da biste obavili svoj posao. Dinamično sučelje omogućuje vam jednostavnu kontrolu sustava putem napredne metode balansiranje i dijagnostičkih funkcija. Imate potpunu kontrolu sustava na dlanu ruke. TA-SCOPE čak određuje ispravne radne točke pumpe. Sve potrebne funkcije u jednom instrumentu - TA-Wireless metoda – sada samo jedna osoba s jednim instrumentom može pouzdano balansirati kompleksne sustave a potrebno je samo jedno podešavanje po ventilu. - TA-SCOPE relej – u kombinaciji sa TA-Wireless čini balanisranje sustava u velikim zgradama jednostavnijim. - TA-Dijagnostika – otkriva greške sustava, omogućujući jednostavno održavanje, pronalaženje grešaka i izradu izvještaja o balansiranju. - Samobrtvljujuće igle s integriranim senzorom temperature čine mjerenje sigurnijim i točnijim. Djelovanje sustava se unaprijeđuje, i omogućeno je kontinuirano snimanje opterećenja pri grijanju/hlađenju.