http___www.imi-hydronic.com_srb-rs_products-solutions_Termostatska_kontrola_Termostatske-glave-i-radijatorski-ventili_Termostatski-radijatorski-ventili_Eclipse__1.xml
1.1 2.1 2.2 2.3 2.4 2.5 2.6 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 12.1 14.1 15.1 15.2 16.1 16.2 17.1 18.1 19.1 20.1 21.1 22.1 22.2 24.1 24.2 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 41.2 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 51.1 51.2 51.3 51.4 51.5 51.6 52.1 52.2
Thermostatic raditor valve with automatic flow control, head and lockshield The IMI Heimeier radiator pack, consists of an automatic flow control TRV body , DX head and lockshield. Designed for application in a two-pipe pumped heating system. The required design flow for each radiator is set directly on the Eclipse valve. This automatic flow limitation is done with a twist and the adjusted flow will then not be exceeded. Even if there is an oversupply of pressure, due to load changes in the system, for example other valves closing or during morning start up, Eclipse will guarantee the desired flow. The thermostatic head with our incompressible liquid-filled sensor guarantees a reliable and precise room temperature control. Technical description Applications area: Heating systems Function: Control Flow limitation Shut-off Dimensions: Pressure class: Temperature: Max. working temperature: 120°C, with protection cap or actuator 100°C. Min. working temperature: -10°C. Flow range Eclipse: The flow can be stepless pre-set within the range: 10-150 l/h. Delivery setting 150 l/h. nominal flow qmN at 10 kPa respecting EN 215: 115 l/h) Differential pressure (ApV) Eclipse: Max. differential pressure: Min. differential pressure: 10 – 100 l/h = 10 kPa 100 – 150 l/h = 15 kPa Materials: Valve body: Brass O-rings: EPDM rubber Valve disc: EPDM rubber Return spring: Stainless steel Valve insert: Brass, PPS (polyphenylsulphide) The complete thermostatic insert can be replaced using the IMI Heimeier fitting tool without draining the system. Spindle: Niro-steel spindle with double O-ring sealing. Material thermostatic head: ABS, PA6.6GF30, brass, steel, Liquid-filled thermostat. Surface treatment: Valve body and fittings are nickel-plated. Marking: IMI, country code, flow direction arrow, KEYMARK-Designation. II+ Designation. Orange protection cap. Standards: The thermostatic valve bodies meet the following requirements: – KEYMARK certified and tested to DIN EN 215. Pipe connection: G1/2 male thread with 15 mm compression fitting for copper or precision steel pipe. Connection to thermostatic head and actuator: IMI Heimeier M30x1.5 Thermostatic head DX: Thermostatic head DX with closed graduation cap and liquidfilled thermostat. High actuating force, minimum hysteresis, optimum closing time. Stable control response even with minor calculated p-band variations (<1 K). Setting numbers 0–IIIII. Frost protection. Temperature range 0 °C to 28 °C. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 2.4 2.5 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 23.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 49.2 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 59.1 59.2
Termostatski radijatorski ventil sa automatskim ograničenjem protoka Termostatski radijatorski ventil Eclipse ima jedinstveni ograničivač protoka koji eliminiše bilo kakvo prekoračenje protoka. Zahtevani protok se podešava direktno na ventilu. Podešeni protok neće biti veći čak ni kada postoje znatne promene u instalaciji bilo da neki ventili zatvaraju bilo da je reč o jutarnjem startovanju sistema grejanja. Ventil reguliše protok nezavisno od promene diferencijalnog pritiska. Prema tome, nisu potrebni komplikovani proračuni za određivanje pozicije predregulacije. Ključne karakteristike Integrisani ograničivač protoka Ne dozvoljava prekoračenje protoka Jednostavno podešavanje Kako bi se postigao projektovani protok Opseg protoka od 10 do 150 l/h Za veću fleksibilnost Sva tela ventila označena sa ‘’II’’ mogu biti modifikovana kao Eclipse Pr: Calypso exact, Calypso, Mikrotherm F, Multilux, Multilux 4-Set Perfect for renovation Standard dimensions and easy flow sizing Tehnički opis Namena: Sistemi grejanja. Funkcija: Kontrola Regulacija protoka Zatvaranje Dimenzije: Nazivni pritisak: Temperatura: Max. radna temperatura: 120°C, sa zaštitnom kapom ili aktuatorom 100°C. Min. radna temperatura: -10°C Opseg protoka: Protok se može predregulisati u opsegu: 10-150 l/h. Podešavanje protoka do 150 l/h. (Max. nominalni ptorok qmN na 10 kPa prema EN 215: 115 l/h) Diferencijalni pritisak (ApV): Max. differencijalni pritisak: Min. differencijalni pritisak: 10 – 100 l/h = 10 kPa 100 – 150 l/h = 15 kPa Materijal: Telo ventila: Mesing O-prsten: EPDM guma Disk ventila: EPDM guma Povratna opruga: Nerđajući čelik Uložak ventila: Mesing, PPS (polyphenylsulphide) Ceo termostatski uložak može se zameniti korišćenjem IMI Heimeier alata bez pražnjenja instalacije. Vreteno: Niro čelik sa duplim O-prstenastim zaptivanjem. Površinska obrada: Telo ventila i fiting su niklovani. Označavanje: THE, DN, oznaka zemlje, smer protoka i KEYMARK-oznaka. II+ oznaka. Narandžasta zaštitna kapa. Standardi: Telo ventila prema sledećim zahtevima: – KEYMARK sertifikovano i testirano prema DIN EN 215. Cevni priključci: Unutrašnji navoj je projektovan za povezivanje na cevi sa navojem, ili u kombinaciji sa kompresionim spojnicama, na bakarne ili precizne čelične cevi. U kombinaciji sa duplom zateznom spojnicom pogodan je za povezivanje na višeslojne cevi. Priključak na termostatsku glavu i aktuator: IMI Heimeier M30x1.5 Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.