http___www.kbarmature.rs_proizvodi_proizvodi-od-plasticnih-masa_separatori_1.xml
1.1 2.1 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 22.2 22.3 22.4 22.5 22.6 22.7 22.8 22.9 22.10 23.1 24.1 25.1 26.1 27.1 28.1 28.2 28.3 29.1 30.1 30.2 30.3 30.4 30.5 30.6 30.7 30.8 31.1 31.2 31.3 31.4 31.5 32.1 32.2 32.3
Separators Polyethylene separators Euro - norm EN 858, for underground installation, with integrated sludge separator, with safety float against the spilling of mineral oil calibrated for fluid density 0.85 to 0.95 g/cm3, with coalescent filter that allows the residual oil content to be lower than 5 mg/l which is maximum allowed according to DIN EN 858. Product advantages: - Tested for strength, - Lightweight, durable construction, - Low cost of installation, - Low cost of cleaning due to optimum construction of the chamber volume, - Low maintenance cost and easy cleaning of the interior, - Coalescent cartridge is easily removed, cleaned or changed, - Indication of mineral oil fill, - Emptying the separators is performed as needed and according to the signal indicator - Absolute protection against oil spills at the exit of the separator (safety float). - Supply of waste water - Drain for the purified water - Sludge separator - Tank for the separated mineral oil - Automatic shutter - The top section of the lid - Coalescent filters (coarse and fine) - Pane for taking samples - Alarm devices Polyethylene product can be placed directly in the excavation place. It is necessary to perform excavation of appropriate dimensions, which we get by increasing the dimensions that are given in the table for the product we intend to install for 20 cm on each side or depth obtained by increasing the height of product for 40 cm. Prepare a moistened sandy bedding at least 20 cm thick at the bottom of the trench, so that the device can be placed on a homogeneous material. Lay the device in the excavation, connect and test provided input and output pipes. Fill the device with water and fill in sides with sand: filling is performed in layers of 15 to 20 cm in the way that the water is poured to the desired level first, and then the sides are filled with wet sand. Filling with sand is carried to a height of 20 cm above the device with light compaction. The rest of the trench is filled to the top with the soil freed of stones or elements that can penetrate to the device. It is necessary that compaction of the sand around the device is 95% by Proctor. If the device is placed underneath the road that is designed for heavy flow of freight traffic it is necessary to install additional reinforced concrete (relief) plate. If there is groundwater in the area of the installation, concrete base should be done on the sand bedding. When installing take into account that: - Separator should not be installed directly below the place it serves - Separator must be available for inspection and emptying, - Pipes connected to the separator must not be equipped with fragrance catchers (siphons), - Separator lids shall never be physically connected with the separator using screws, bolts, locks, etc.., - Wastewater should be entering the separator with the help of the force of gravity. Pumping stations can not be used to deliver the water directly into the separator. Pumping stations can be used after the separator drain opening to drain the purified wastewater to sewer pipes, - Pane for taking samples (installed after the separator in the direction of flow) must always be installed. Coalescent filter is integrated within the set and installed near the separator drain and carries out the separation of the finer and difficult separable oil particles from waste water. These finer particles are catched in the filter where they combine with others, creating a larger / heavier droplets which are then separated from the coalescent filter and rise to the surface of the separator. Separators are equipped with self-activating float which closes the separator drain completely when SEPARATOR ACHIEVES MAXIMUM AMOUNT OF MINERAL OIL. Float is calibrated to float on the water and sink in the oil / fuel (it withstands all substances with specific density between 0.85 and 0.95 g/cm3). When the maximum amount of mineral oil is reached it overwhelms the chamber and causes rapid sinking of the float, which completely closes the drain of the separator. To reduce the possibility of closing the separator flow because of excessive amounts of oil in the tank, alarm unit that monitors the level of mineral oil can be installed, so that the contents of the separator can be emptied on time. Pane for taking samples is designed to allow fast, easy and accurate taking of samples of the output water that flows out from the separator. Pane for taking samples allows the owner or the inspection agency to take the water sample that flows out in the purpose of supervision of the separator. Concentration of cleaning agents and detergents in wastewater entering the separator should be kept to a minimum. Cleaning agents / detergents used for washing, and are therefore present in wastewater entering the separator should be neutral and free of hydrogen chloride. Chlorinated hydro / carbonates are not allowed in the cleaning agents. If more than one detergents or cleaning agents are used, they should be compatible. If in doubt, contact the manufacturer of the cleaning agent / detergent for further information. Under improper use of washing devices or when the cleaning agents / detergents are directly injected into the washer and are then sprayed to the surface contaminated with mineral oil EMULSIFICATION can occur. Untreated emusificators present in wastewater that enters the separator can not be separated using mineral oil separator with coalescent filter. In cases when emusificators are present in wastewater, emulsification devices can be installed which can process wastewater before it enters the separator.
1.1 2.1 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 22.2 22.3 22.4 22.5 22.6 22.7 22.8 22.9 22.10 23.1 24.1 25.1 26.1 27.1 28.1 28.2 28.3 29.1 30.1 30.2 30.3 30.4 30.5 30.6 30.7 31.1 31.2 31.3 31.4 31.5 32.1 32.2 32.3
Separatori Polietilenski separatori Euro - normi EN 858, za podzemnu ugradnju, sa integrisanim separatorom mulja sigurnosnim plovkom protiv prelivanja mineralnih ulja kalibrisanim za tečnosti gustine 0.85 do 0.95 g/cm3, sa koalescentnim filterom koji omogućava da je sadržaj zaostalog ulja niži od 5 mg/l što je prema DIN EN 858 najviše dozvoljeno. Prednosti proizvoda: - Ispitan na čvrstoću, - Mala težina, izdržljiva konstrukcija, - Mali troškovi ugradnje, - Niski troškovi čišćenja zahvaljujući optimalno kostruisanoj zapremini komore, - Niski troškovi održavanja i lako čišćenje unutrašnjosti, - Koalescentni uložak se lako uklanja, čisti ili menja, - Indikacija zapunjenosti mineralnim uljem, - Pražnjenje separatora se vrši po potrebi a prema signalu indikatora - Apsolutna zaštita od izlivanja ulja na izlazu iz separatora (sigurnosni plovak). - Dovod odpadne vode - Odvod prečišćene vode. - Separator mulja. - Spremnik separiranog mineralnog ulja. - Automatski zatvarač. - Gornja sekcija poklopca. - Koalescentni filteri (grubi i fini). - Okno za uzimanje uzoraka. - Alarmni uređaji. Polietilenski proizvod može se postaviti direktno u samom iskopu. Potrebno je izvesti iskop odgovarajućih dimenzija koje dobijamo povećavši gabarite date u tablici proizvoda kojeg nameravamo ugraditi za 20 cm sa svake strane odnosno dubine dobijene povećavši visinu proizvoda od 40 cm. Uraditi ovlaženu peščanu posteljicu od debljine barem 20 cm na dnu rova kako bi se uređaj mogao položiti na homogeni materijal. Položiti uređaj u iskop, priključiti i ispitati predviđene ulazne i izlazne cevi. Napuniti uređaj vodom i uporedno zatrpavati bokove peskom: zatrpavanje izvesti u slojevima od 15 do 20 cm na način da se najpre ulije voda u toj visini pa nakon toga zatrpati bok vlažnim peskom. Zatrpavanje peskom izvesti do visine 20 cm iznad uređaja sa laganim zbijanjem. Ostatak rova do vrha popuniti zemljom bez ubacivanja kamenja i elemenata koji mogu prodreti do uređaja. Neophodno je da zbijanje peska oko uređaja bude 95% po Proktoru. Ukoliko se uređaj postavlja ispod saobraćajnice koja je predviđena za odvijanje teškog teretnog saobraćaja potrebno je ugraditi dodatnu armiranu betonsku (rasteretnu) ploču. U slučaju prisutnosti podzemnih voda na mestu nameravane ugradnje na posteljici od peska uraditi betonsku podlogu. Prilikom ugradnje obavezno voditi računa da: - Separator ne sme biti ugrađen direktno ispod mesta kojem služi, - Mora biti dostupan za inspekciju i pražnjenje, - Cevi spojene na separator ne smeju biti opremljene hvatačima mirisa (sifonima), - Poklopci separatora ne smeju se nikada fizički spajati sa separatorom pomoću vijaka, klinova, brava ili sl., - Otpadna voda u separator treba da dotiče silom gravitacije. Stanice za prepumpavanje se ne mogu koristiti da bi dopremale vodu direktno u separator. Stanice za prepumpavanje se mogu koristiti iza odvoda separatora za odvod očišćene otpadne vode do kanalizacijskih cevi, - Okno za uzimanje uzoraka (instalira se iza separatora u smeru protoka) mora biti uvek ugrađeno. Koalescentni filter je integrisan u sklopu i postavljen blizu odvoda iz separatora i provodi separaciju finijih i teže odvojivih čestica ulja iz otpadne vode. Te finije čestice zaostaju u filteru gde se spajaju sa drugima i tako čine veće/teže kapljice koje se zatim odvajaju od koalescentnog filtera i uzdižu se na površinu separatora. Separatori su opremljeni samoaktivirajućim plovkom koji potpuno zatvara izlaz separatora kad SEPARATOR POSTIGNE MAKSIMALNU KOLIČINU MINERALNOG ULJA. Plovak je kalibriran da pluta po vodi, a tone u ulju/gorivu (podnosi sve materije sa specifičnom gustinom između 0.85 i 0.95 g/cm3). Kada se postigne maksimalna količina mineralnog ulja, ono preplavljuje komoru i uzrokuje brzo potonuće plovka koji potpuno zatvara odvod iz separatora. Kako bi se smanjila mogućnost zatvaranja protoka separatora zbog prekomerne količine ulja u spremniku, može se ugraditi alarmna jedinica koja nadzire nivo mineralnog ulja tako da se sadržaj separatora može isprazniti na vreme. Okno za uzimanje uzoraka je konstruisano tako da omogućava brzo, lako i tačno uzimanje uzoraka izlazne vode koja ističe iz separatora.Okno za uzimanje uzoraka omogućava vlasniku ili inspekcijskoj službi da uzme uzorak vode koja ističe u svrhu nadzora rada separatora. Koncentraciju sredstava za čišćenje i deterdženata u otpadnoj vodi koja ulazi u separator treba održavati na minimumu. Sredstva za čišćenje/deterdženti koji se koriste za pranje i zbog toga su prisutni u otpadnoj vodi te ulaze u separator trbaju biti neutralni i bez hidrogen-hlorida. U sredstvima za čišćenje nisu dozvoljeni hlorirani hidro/karbonati. U slučaju gde se korisi više od jednog sredstva za pranje i deterdženata, oni moraju biti kompatabilni. Uslučju nedoumice, za daljnje informacije kontaktirajte proizvođača sredstava za pranje/deterdženta. Pri nepravilnom korišćenju uređaja za pranje ili kada se sredstva za pranje/deterdženti direktno ubrizgavaju u uređaj za pranje i onda rasprskavaju na površinu zaprljanu mineralnim uljem može doći do EMULZIFIKACIJE. Netretirani emulzifikatori prisutni u otpadnoj vodi koja ulazi u separator ne mogu se separirati separatorom mineralnog ulja sa koalescentnim filterom. U slučajevima kada su emulzifikatori prisutni u otpadnoj vodi, mogu se instalirati emulzifikacijski uređaji koji će obraditi otpadnu vodu pre nego što ona uđe u separator.