http___www.kotlovi.hr_proizvodi_kotlovi_na_biomasu_default.aspx_1.xml
1.1 2.1 2.2 3.1 3.2 4.1 4.2 5.1 5.2 6.1 7.1 9.1 11.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 22.2 23.1 24.1 25.1 25.2 26.1 27.1 27.2 28.1 29.1 30.1 30.2 31.1 32.1 33.1 34.1 35.1 35.2 36.1 37.1 37.2 38.1 38.2 39.1 40.1 41.1 42.1 44.1 46.1 47.1 49.1 50.1 52.1 53.1 55.1 56.1 58.1 59.1
ĐĐ Kotlovi produced and mounted hot water biomass plant with maximum heat capacity of 4 MW at sawmill MMM-Vukelić, Novska, Croatia.. The plant is intended for the production of thermal energy from wood residues. It is aimed for supplying technological consumers with thermal energy. In this case, client already had boiler whose performances were not as declared one. Instead of 4 MW that boiler could barely reach 1.5 MW, which was insufficient for the needs of production. Client's demands: Ensured heat capacity of the boiler and equipment in the range 3-4 MW Provided heat to the water outlet of the boiler in the range 160-170oC Ensured safe and reliable performance of sawdust burning Project solution: The subject facility should be conceptualized so that the combustion of wood residues release available thermal energy in the form of hot water in order to fulfill the set of energy and temperature regimes of technological consumers exploitation, under optimal technical, and statutory environmental requirements. The available wood residues, used as energy fuel, are stored in the floor depot of 36m3 working volume, which is sufficient for 16 working hours of thermal power plants at consumers' nominal load of cca 3200 kW. Fuel is transported by the floor extractor and the worm gear conveyor to the dosing container, and from it to the hot water boilers adiabatic swirling furnace by dosing worm gear conveyor and flow of primary air. After entering the furnace, initiated by the accumulated heat and the temperature of fireclays walling up to 650/1000oC, comes to self-ignition of fuel. The end goal of fuel burning process are flue gases temperature up to 1000/1150oC which produce hot water by passing through the boilers heating surfaces, and when they get cold being drain into the atmosphere by the exhaust ventilator through the flue gas over the chimney. Separation of ash is done within cyclone filter as a part of the flue gas tract, and the same being collected in the portable ashes containers. Auto maintenance of overpressure and expansions, and if necessary, supplementing of hot water system with water is done by system which consists of a pump, atmospheric vessel and overflow valve. All devices and segments of the plant are connected in the functional unit of automatic controlled mechanized fuel supply through equipment of the control cabinet. All vital functions of plants could be controlled manually. The plant is placed in the space (LxWxH) 18x12x8 m. Project provided: - Water temperature at the outlet of the boiler is 165oC. Operation of the boiler plant is fully automatic. Flue gas temperatures are very low (185-195oC) and boiler efficiency rate is very high. Fuel handling, combustion and filtering flue gases are automatic control. Economical operation of the boiler (low consumption of biofuels). Increased production of veneer for 10 to 15% compared to the previous state. Safe and reliable operation of automatic boiler achievement automatically
1.1 2.1 3.1 4.1 5.1 6.1 7.1 7.2 8.1 8.2 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 29.2 30.1 30.2 31.1 32.1 33.1 34.1 34.2 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 42.2 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 51.1 52.1 53.1 54.1 55.1 56.1
Kotlovi na biomasu Vrelovodni kotao na biomasu ĐĐ Kotlovi su pilani MMM-Vukelić isporučili i ugradili vrelovodnu kotlovnicu na biomasu maksimalnog toplinskog kapaciteta Predmetno postrojenje je namijenjeno proizvodnji toplinske energije iz drvnih ostataka, a u svrhu podmirenja potreba tehnoloških potrošača za toplinskom energijom u drvnoj industriji. Naime, korisnik je već posjedovao kotao inozemnog dobavljača čije performanse nisu bile u skladu s deklariranim. Umjesto obećanih 4 MW toplinskog kapaciteta kupljeni kotao mogao je postići jedva 1,5 MW što je bilo nedovoljno za potrebe proizvodnje. Zahtjev kupca je bio slijedeći: - osigurati toplinski kapacitet kotla i opreme u rasponu 3-4 MWPredloženo rješenje projektnog zadatka: - osigurati toplinu vode na izlazu kotla u rasponu 160-170oC - osigurati siguran i pouzdan rad pri loženju suhom piljevinom Predmetno postrojenje koncipirati tako da se sagorijevanjem raspoloživih drvnih ostataka oslobodi toplinska energija u vidu vrele vode u svrhu kvalitetnog ispunjavanja postavljenih energetskih i temperaturnih režima eksploatacije tehnoloških potrošača, a pod optimalnim tehničkim, te zakonom propisanim ekološkim uvjetima. Raspoloživi drvni ostaci, koji se koriste kao energetsko gorivo, skladište se u podnom deponiju radnog volumena 36 m3, što je dovoljno za 16h rada termoenergetskog postrojenja kod nominalnog opterećenja potrošača od cca 3200 kW. Pomoću podnog izvlakača i pužnog transportera gorivo se transportira u dozirni spremnik, a iz istog se pomoću dozirnog puža i strujanja primarnog zraka dozira u adijabatsko vrtložno ložište vrelovodnog kotla. Nakon ulaska u ložište, inicirano akumuliranom toplinom i temperaturom šamotnih ozida od 650/1000oC, dolazi do samozapaljenja goriva. Krajnji produkt procesa sagorijevanja goriva su dimni plinovi temperature 1000/1150 oC koji prolaskom kroz ogrjevne površine kotla proizvode vrelu vodu, a ohlađeni se pomoću odsisnog ventilatora kroz dimovodni trakt preko dimnjaka odvode u atmosferu. Izdvajanje pepela vrši se unutar ciklonskog filtera u sklopu dimovodnog trakta, a isti se sakuplja u prijenosne posude za pepeo. Automatsko održavanje pretlaka i ekspanzija, te po potrebi dopunjavanje vrelovodnog sistema vodom vrši se diktir sistemom koji se sastoji od crpke, atmosferske posude i prestrujnog ventila.Preko opreme upravljačkog ormara svi uređaji i segmenti postrojenja povezani su u funkcionalnu cjelinu mehaniziranog loženja s automatskim kontinuiranim upravljanjem u odnosu na izuzimanje toplinske energije iz kotla uvjetovano potrebama potrošača, uz mogućnost ručnog upravljanja svim vitalnim funkcijama postrojenja. Postrojenje se smješta u prostor (DxŠxV)18x12x8m. Zadovoljenje korisnikovih potreba i njegove koristi ugrađenim kotlom ogledaju se u slijedećem: - Temperatura vode na izlazu iz kotla je 165oC. - Rad kotla i kotlovnice je potpuno automatski. - Temperature dimnih plinova su vrlo niske ( 185-195oC) i stupanj korisnog djelovanja kotla vrlo visok. - Manipulacije gorivom, sagorijevanje i filtriranje dimnih plinova vrše se mehanizirano automatskim upravljanjem. - Postignut ekonomičan rad kotla (mala potrošnja biogoriva). - Povećanje proizvodnje furnira za 10 do 15 % u odnosu na prethodno stanje. - Siguran i pouzdan automatski rad kotla Vrelovodni kotao na biomasu - 4MW Ložište kotla na biomasu Vrelovodni kotao na biomasu s ložištem Ekspanziona posuda s pumpom za održavanje tlaka Cikloni Cikloni - odvajači pepela Doziranje i upuhivanje goriva Podni izvlakač goriva