http___www.imi-hydronic.com_srb-rs_products-solutions_Balansiranje_i_kontrola_Balansni-ventili_Balansni-ventili_STAD__1.xml
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 12.1 14.1 16.1 16.2 17.1 17.2 19.1 19.2 20.1 20.2 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 35.2
Ball valve – DN 10-50 Soft-sealing for complete ease-of-use, the TA 900 iSi ball valve is suitable for use in heating, cooling and tap water systems. KOMBI connections enable smooth installation. Technical description Applications: Heating and cooling systems Tapwater systems Process systems where the media does not affect the incoming material. Function: Shut-off Dimensions: Pressure class: Temperature: Max. working temperature: 120°C Min. working temperature: -20°C Max. working temperature: 90°C Min. working temperature: -20°C Material: Valve body: Die cast AMETAL® Ball: Chrome plated AMETAL®, double nickel Handle: Glass fibre re-inforced polyamid plastic Rating plate: Acetal plastic Cover screws: Stainless steel (The valve has cover screws for DN 32-50, DN 10-25 has a threaded top section) Seat elements and O-rings: 58 940: EPDM rubber, 58 950: Nitrile rubber Handle reduction unit: Nickel-plated die-cast zinc alloy Control handle: Glass fibre re-inforced plastic AMETAL® is the dezincification resistant alloy of IMI Hydronic Engineering. Surface treatment: Nickel plated Marking: TA, DR, DN, PN The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 15.1 17.1 18.1 19.1 19.2 19.3 19.4 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 33.2
Balansni ventil STAD sa izuzetnim hidrauličkim performansama i impresivnim opsegom primene. Idealan za upotrebu u intstalacijama grejanja i hlađenja i sistemima potrošne vode. Tehnički opis Namena: Sistemi grejanja i hlađenja Sistemi potrošne vode Funkcija: Balansiranje Predregulacija Merenje Zatvaranje Ispuštanje (opciono) Dimenzije: Klasa pritiska: Temperatura: Max. radna temperatura: 120°C. Za vise temperature max. (max. 150°C), molimo Vas kontaktirajte IMI Hydronic Engineering. UPOZORENJE! DN 25-50 sa ravnim krajevima max. radna tempertatura 120°C. Min. radna temperatura: -20°C Materijal: Ventili su napravljeni od AMETAL® Sedište ventila: Osnova sa EPDM prstenom Vreteno: EPDM prsten Ručica: Polyamid i TPE Ravni krajevi: Nastavci: AMETAL® Zaptivanje (DN 25-50): EPDM prsten AMETAL® je legura otporna na koroziju i zaštićena od strane IMI Hydronic Engineering. Označavanje: Telo: TA, PN 20/150, DN i veličina u inčima. Ručica: Tip ventila i DN. Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.