http___www.imi-hydronic.com_ba_products-solutions_Pressurisation-and-Water-quality_Odravanje-tlaka_Ekspanzijske-posude-sa-zranim-jastukom_Ekspanzijska-posuda-s-membranom-__1.xml
1.1 2.1 2.2 2.3 2.4 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 11.2 12.1 12.2 13.1 14.1 14.2 15.1 15.2 16.1 16.2 17.1 17.2 18.1 18.2 19.1 20.1 21.1 22.1 23.1 24.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 33.2
Vacuum degassing system Pressure drop degasser according to the vacusplit principle. Through the atomizing process of the water in a special vacuum vessel, the gases are separated completely from the water. A water makeup system may be integrated as an option. It is used in heating, solar and cooling water systems to facilitate central venting of the system and minimise corrosion. Technical description Applications: Heating, solar and chilled water systems. For systems according to EN 12828, EN 12976, ENV 12977, EN 12952, EN 12953. Media: Non-aggressive and non-toxic system media. Addition of antifreeze agent up to 50%. Pressure: Min. admissible pressure, PSmin: -1 bar Max. admissible pressure, PS: see Articles Temperature: Max. admissible temperature, TS: see Articles Min. admissible temperature, TSmin: 0 °C Max. admissible ambient temperature, TU: 40 °C Min. admissible ambient temperature, TUmin: 0°C Max. admissible temperature for water make-up, TW: 30 °C (VP) Supply voltage: 230 V/50 Hz and 60 Hz 3 x 400 V/50 Hz (VP...PEC) Enclosure class: IP 54 according to EN 60529 Sound pressure level: 74 dB(A) (VP .2 EC) Material: In essence: steel, brass and gunmetal. Transportation and storing: In frostless, dry places. Approvals: CE-tested according to the requirements of the European Directives PED/DEP 97/23/EC, 2004/108/EC, 2006/95/EC. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 21.2
Od 6L do 750L Linija ekspanzijske posude s fiksnom membranom su idealne za manje sustave grijanja i hlađenja do 750 L. Linija ovih posuda ima jednostavan dizajn i robusnu konstrukciju. Tehnički opis Primjene: Sustavi grijanja i hlađenja. Medij: Neagresivni i netoksični mediji. Dodatak antifriza do 49%. Tlak: Min. dopušteni tlak, PSmin: 0 bar Max. dopušteni tlak, PS: ovisno o tipu Radna temperatura: Material: Posuda : Čelik Gumena membrane : SBR Transport i skladištenje: Na suhom mjestu, zaštićeno od smrzavanja. Approvals: CE testirano prema PED/DEP 97/23/EC. Proizvodi, tekstovi, fotografije, crteži i dijagrami u ovoj brošuri podložni su promjenama od strane IMI Hydronic Engineering, bez prethodne obavijesti ili obrazloženja. Za više informacija o proizvodima i specifikacijama molimo posjetite nas na www.imi-hydronic.com.