http___www.imi-hydronic.com_srb-rs_products-solutions_pressurisation-and-water-quality_Odravanje-pritiska_Ureaj-za-odravanje-pritiska-s-pumpama_Transfero-T___1.xml
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 11.2 12.1 12.2 13.1 14.1 14.2 15.1 15.2 16.1 16.2 17.1 17.2 18.1 18.2 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 36.1 37.1 38.1 39.1 40.1 40.2 41.1 41.2 42.1 43.1 44.1 44.2 45.1 45.2 46.1 46.2 47.1 48.1 48.2 49.1 50.1 51.1 52.1 53.1 54.1 55.1 55.2 56.1 56.2 57.1 57.2
Pressure maintenance systems up to 10 MW with pumps Transfero T_ is a precision pressure maintenance device up to 10 MW with pumps for heating, solar and chilled water systems. Its use is particularly recommended where high performance, compact design and precision are required. In the medium performance range with tight budgets, they can also be used as combination devices with integrated degassing and water make-up. Technical description – Control unit TecBox Applications: Heating, solar and chilled water systems. For systems according to EN 12828, solar systems according to EN 12976, ENV 12977 with on-site excess temperature protection in case of power blackout. Media: Non-aggressive and non-toxic system media. Addition of antifreeze agent up to 50%. Pressure: Min. admissible pressure, PSmin: 0 bar Max. admissible pressure, PS: see Articles Temperature: Max. admissible temperature, TS: 70°C Min. admissible temperature, TSmin: 0°C Max. admissible ambient temperature, TU: 40°C Min. admissible ambient temperature, TUmin: 5°C Max. admissible temperature for water make-up, TW: 30°C (TP, TPV, TPV... Accuracy: Precision pressure maintenance ±0,2 bar. Supply voltage: 230 V/50 Hz (T, TP, TV, TPV) and 60 Hz (TPV) P), see Articles. Enclosure class: IP 54 according to EN 60529 Material: Main materials include steel, brass and bronze. Transportation and storing: In frostless, dry places. Approvals: CE-tested according to the requirements of the European Directives PED/DEP 97/23/EC, 2004/108/EC, 2006/95/EC. Technical description – Expansion vessels Applications: Only together with Control unit TecBox. See Applications under Technical description - Control unit TecBox. Media: Non-aggressive and non-toxic system media. Addition of antifreeze agent up to 50%. Pressure: Min. admissible pressure, PSmin: 0 bar Max. admissible pressure, PS: 2 bar Temperature: Max admissible temperature, TS: 120°C Min. admissible temperature, TSmin: -10°C Max. admissible bag temperature, TB: 70°C Min. admissible bag temperature, TBmin: 5°C Material: Steel. Color beryllium. Airproof butyl bag according to EN 13831 and IMI Pneumatex internal standard. Transportation and storing: In frostless, dry places. Approvals: CE design-tested according to PED/DEP 97/23/EC. Warranty: Transfero TU, TU... E: 5-year warranty for the vessel. Transfero TG, TG... E: 5-year warranty for the airproof butyl bag. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 3.1 3.2 4.1 5.1 6.1 6.2 7.1 8.1 8.2 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 34.1 35.1 35.2 36.1 37.1 38.1 39.1 40.1 41.1 41.2 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 50.2
Sistem za održavanje pritiska sa pumpama do 10 MW Transfero T_ je precizni uređaj za održavanje pritiska sa pumpama za solarne sisteme i instalacije grejanja i hlađenja do 10 MW. Preporučuje se za instalacije gde se zahtevaju visoke performanse, kompaktni dizajn i izuzetna preciznost u radu. Mogu se koristiti u kombinaciji sa integrisanim uređajima za degazaciju i dopunu vode. Tehnički opis – Kontrolna jedinica TecBox Namena: Instalacije grejanja, hlađenja i solarni sistemi. Za sisteme prema EN 12828, solarne sisteme prema EN 12976, ENV 12977 sa direktnom temperaturskom zaštitom u trenutku nestanka električne energije. Medij: Neagresivan, netoksičan fluid. Dodatak antifriza do 50%. Pritisak: Min. dopušten pritisak, PSmin: 0 bar Max. dopušten pritisak, PS: pogledajte deo Artikli Temperature: Max. dopuštena temperatura, TS: 70°C Min. dopuštena temperatura, TSmin: 0°C Max. dopuštena temperatura okoline, TU: 40°C Min. dopuštena temperatura okoline, TUmin: 5°C Max. dopuštena temperatura za dopunu vode, TW: 30°C (TP, TPV, TPV...P) Tačnost: Precizno održavanje pritiska ±0,2 bar. Napon: V/50 Hz (T, TP, TV, TPV) 3x400/50 ili 3x400/60 (TPV...P), Pogledajte deo Artikli. Zaštita: IP 54 prema EN 60529 Materijal: Uopšteno: čelik, mesing i aluminijum Transport i skladištenje: U prostorijama koje se greju, suvim prostorijama. Sertifikati: CE-testirano prema Evropskim Direktivama PED/DEP 97/23/EC, 2004/108/EC, 2006/95/EC. Tehnički opis – Ekspanzione posude Namena: Samo zajedno sa kontrolnom jedinicom TecBox. Pogledajte Primenu u tehničkom opisu-kontrolna jedinica TecBox. Medij: Neagresivan, netoksičan fluid. Dodatak antifriza do 50%. Pritisak: Min. dopušten pritisak, PSmin: 0 bar Max. dopušten pritisak, PS: 2 bar. Temperatura: Max. dopuštena temperatura, TS: 120°C Min. dopuštena temperatura, TSmin: -10°C Max. dopuštena temperatura vreće, TB: 70°C Min. dopušten temperatura vreće, TBmin: 5°C Materijal: Čelik. Boja berilijum. Vazdušno nepropusna butil vreća prema EN 13831 i IMI Pneumatex internom standardu. Transport i skladištenje: U prostorijama koje se greju, suvim prostorijama. Sertifikati: CE projektovano i testirano prema PED/DEP 97/23/EC. Garantni period: Transfero TG, TG...E: 5 godina garancije na vazdušno nepropusnu vreću. Transfero TU, TU...E: 5 godina garancije na posudu. Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.