http___www.imi-hydronic.com_srb-rs_products-solutions_pressurisation-and-water-quality_Kvalitet-vode_Automatski-odzrani-ventil_Zeparo-Cyclone__1.xml
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 10.2 11.1 11.2 12.1 13.1 13.2 14.1 14.2 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 26.2 27.1 28.1 28.2 29.1 29.2 30.1 30.2
Dirt and magnetite separator with Cyclonic technology Comprehensive range of products fof sludge and magnetite separation in heating and cooling water systems. The number of potential applications as well as their modular construction is unique. Its new cyclonic technology takes dirt separation efficiency to the next level Technical description Application: Heating and chilled water systems. Media: Non-aggressive and non-toxic system media. Addition of antifreeze agent up to 50%. Pressure: Max. admissible pressure, PS: 10 bar Min. admissible pressure, PSmin: 0 bar Temperature: Max. admissible temperature, TS: 120 °C Min. admissible temperature, TSmin: -10 °C Material: Body: Brass Cyclone insert: PPS Ryton. Gaskets: EPDM Marking: Body: PN, DN, flow direction arrow. Label with TS and TSmin. Transportation and storing: In dry places. Magnet and Thermal insulation: Magnet: NdFeB with Ni-Cu-Ni cover/protection against rust. Insulation: Expanded polypropylene (EPP), anthracite. Insulation value approx. 0.035 W/mk. Fire rating B2 to DIN 4102 and E in acc. Max. temperature: 110 °C. Min. temperature: 6-8 °C (above dew point). The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 3.1 4.1 5.1 6.1 7.1 7.2 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 23.2
Automatski separator nečistoća Sveobuhvatni asortiman proizvoda za odvajanje taloga u vodenim grejnim i rashladnim sistemima. Raznovrsnost primene kao i njihova modularna konstrukcija su jedinstveni. Nova ciklonska tehnologija – podizanje efikasnosti separacije nečistoća na sledeći nivo. Tehnički opis Namena: Grejni i sistemi hladne vode. Medij: Neagresivan, netoksičan fluid. Dodatak antifriza do 50%. Pritisak: Max. dopušteni pritisak, PS: 10 bar Min. dopušteni pritisak, PSmin: 0 bar Temperatura: Max. dopuštena temperatura, TS: 120 °C Min. dopuštena temperatura, TSmin: -10 °C Materijal: Kućište ventila: Mesing Uložak ciklona: PPS Ryton Zaptivke: EPDM Označavanje: Telo: PN, DN, i smer protoka. Etiketa sa TS i TSmin. Transport i skladištenje: Na suvim mestima. Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.