http___www.imi-hydronic.com_srb-rs_products-solutions_Termostatska_kontrola_Termostatske-glave-i-radijatorski-ventili_Termostatski-radijatorski-ventili_Eclipse__1.xml
1.1 2.1 2.2 2.3 2.4 2.5 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 21.1 23.1 24.1 25.1 26.1 27.1 28.1 28.2 30.1 30.2 31.1 32.1 33.1 34.1 34.2 35.1 35.2 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 51.1 51.2 52.1 54.1 54.2
Thermostatic radiator valve with automatic flow limitation The thermostatic radiator valve Eclipse S has a unique integrated flow limiter that eliminate over flows. The required flow rate can be adjusted directly at the valve with a twist. The adjusted flow will not be exceed even if there are load changes in the system, due to other valves closing or during morning start up. The valve controls the flow rate independently from differential pressure. Therefore, complicated calculations to determine settings are not necessary. Key features Integrated flow limiter Eliminates over flows Easy adjustment Just a twist to reach design flow Flow range from 10 to 150 l/h For high flexibility Perfect for renovation Standard dimensions and easy flow sizing Technical description Applications area: Heating systems. Function: Control Flow limitation Shut-off Dimensions: Pressure class: Flow range: The flow can be stepless pre-set within the range: 10-150 l/h. Delivery setting 150 l/h. nominal flow qmN at 10 kPa concerning EN 215: 115 l/h) Differential pressure (ApV): Max. differential pressure: Min. differential pressure: 10 – 100 l/h = 10 kPa 100 – 150 l/h = 15 kPa Temperature: Max. working temperature: 120°C, with protection cap or actuator 100°C. Min. working temperature: -10°C. Materials: Valve body: Brass O-rings: EPDM rubber Valve disc: EPDM rubber Return spring: Stainless steel Valve insert: Brass, PPS (polyphenylsulphide) The complete thermostatic insert can be replaced using the IMI Heimeier fitting tool without draining the system. Spindle: Niro-steel spindle with double O-ring sealing. Surface treatment: Valve body and fittings are nickel-plated. Marking: TA, country code, flow direction arrow, size and KEYMARK symbol. Orange protection cap. Standards: Eclipse valves meet the following requirements: – KEYMARK certified and tested to DIN EN 215. (Applied for for KEYMARK certification and testing) Connection to thermostatic head: The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 2.4 2.5 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 23.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 49.2 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 59.1 59.2
Termostatski radijatorski ventil sa automatskim ograničenjem protoka Termostatski radijatorski ventil Eclipse ima jedinstveni ograničivač protoka koji eliminiše bilo kakvo prekoračenje protoka. Zahtevani protok se podešava direktno na ventilu. Podešeni protok neće biti veći čak ni kada postoje znatne promene u instalaciji bilo da neki ventili zatvaraju bilo da je reč o jutarnjem startovanju sistema grejanja. Ventil reguliše protok nezavisno od promene diferencijalnog pritiska. Prema tome, nisu potrebni komplikovani proračuni za određivanje pozicije predregulacije. Ključne karakteristike Integrisani ograničivač protoka Ne dozvoljava prekoračenje protoka Jednostavno podešavanje Kako bi se postigao projektovani protok Opseg protoka od 10 do 150 l/h Za veću fleksibilnost Sva tela ventila označena sa ‘’II’’ mogu biti modifikovana kao Eclipse Pr: Calypso exact, Calypso, Mikrotherm F, Multilux, Multilux 4-Set Perfect for renovation Standard dimensions and easy flow sizing Tehnički opis Namena: Sistemi grejanja. Funkcija: Kontrola Regulacija protoka Zatvaranje Dimenzije: Nazivni pritisak: Temperatura: Max. radna temperatura: 120°C, sa zaštitnom kapom ili aktuatorom 100°C. Min. radna temperatura: -10°C Opseg protoka: Protok se može predregulisati u opsegu: 10-150 l/h. Podešavanje protoka do 150 l/h. (Max. nominalni ptorok qmN na 10 kPa prema EN 215: 115 l/h) Diferencijalni pritisak (ApV): Max. differencijalni pritisak: Min. differencijalni pritisak: 10 – 100 l/h = 10 kPa 100 – 150 l/h = 15 kPa Materijal: Telo ventila: Mesing O-prsten: EPDM guma Disk ventila: EPDM guma Povratna opruga: Nerđajući čelik Uložak ventila: Mesing, PPS (polyphenylsulphide) Ceo termostatski uložak može se zameniti korišćenjem IMI Heimeier alata bez pražnjenja instalacije. Vreteno: Niro čelik sa duplim O-prstenastim zaptivanjem. Površinska obrada: Telo ventila i fiting su niklovani. Označavanje: THE, DN, oznaka zemlje, smer protoka i KEYMARK-oznaka. II+ oznaka. Narandžasta zaštitna kapa. Standardi: Telo ventila prema sledećim zahtevima: – KEYMARK sertifikovano i testirano prema DIN EN 215. Cevni priključci: Unutrašnji navoj je projektovan za povezivanje na cevi sa navojem, ili u kombinaciji sa kompresionim spojnicama, na bakarne ili precizne čelične cevi. U kombinaciji sa duplom zateznom spojnicom pogodan je za povezivanje na višeslojne cevi. Priključak na termostatsku glavu i aktuator: IMI Heimeier M30x1.5 Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.