http___www.imi-hydronic.com_srb-rs_products-solutions_Termostatska_kontrola_Termostatske-glave-i-radijatorski-ventili_Termostatski-radijatorski-ventili_Eclipse__1.xml
1.1 2.1 2.2 2.3 2.4 2.5 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 29.1 30.1 30.2 31.1 32.1 33.1 34.1 36.1 37.1 38.1 39.1 40.1 40.2 41.1 41.2 42.1 43.1 44.1 45.1 46.1 47.1 48.1 48.2 49.1 49.2 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 58.2 59.1 60.1 60.2 61.1 62.1 63.1 64.1 65.1 66.1 67.1 67.2
Flush-mounted individual room control with automatic flow limitation for floor heating systems The Multibox AFC is used for decentralized individual room temperature control or maximum limitation of the return temperature in the case of floor heating systems. The integrated flow limiter guarantee the requested flow is not exceeded. Equalization in the event of out-of-true installation, offsetting up to 6° on each side. Cover with concealed screw fastening. Flexible fitting for all wall structures, 30 mm depth compensation. Key features Integrated flow limiter Eliminates over flows Simple adjustment of the flow to various heating loads For out-of-true installation offsetting up to 6° on each side Adjustable fitting for all wall structures 30 mm depth compensation Technical description Applications: Floor heating systems, wall heating systems, combined floor/radiator heating systems Functions: Multibox AFC K: Individual room temperature control, Automatic flow limiting, Shut-off, Venting Multibox AFC RTL: Maximum limitation of the return temperature, Automatic flow limiting, Shut-off, Venting Multibox AFC K-RTL: Individual room temperature control, Maximum limitation of the return temperature, Automatic flow limiting, Shut-off Dimensions: Valve body DN 15. The flush box has an overall depth of 60 mm. Flexible mounting thanks to variable spacing between flush box and cover of up to 30 mm. The cover can compensate for slanted mounting of the flush box of up to 6° on each side. See also Dimensions. Pressure class: Setting range: Thermostatic head K: 6°C to 28°C Return temperature limiter RTL: 0°C to 50°C Temperature: Max. working temperature: 90°C Min. working temperature: 2°C For all Multibox models, ensure that the system supply temperature is suitable for setting up the floor heating system. See also Information! Flow range: The flow can be stepless pre-set within the range: 30-200 l/h. Delivery setting 200 l/h. Differential pressure (ApV): Max. differential pressure: 60 kPa Min. differential pressure: 30 – 140 l/h = 15 kPa 140 – 200 l/h = 20 kPa Material: Valve body: Corrosion resistant Gunmetal O-rings: EPDM rubber Valve disc: EPDM rubber Return spring: Stainless steel Valve insert: Brass, PPS (polyphenylsulphide) Spindle: Niro-steel spindle with double O-ring sealing. The outer O-ring can be replaced under pressure. Plastic parts of ABS and PA. Sensor element: Thermostatic head K with liquid filled sensor. Return temperature limiter (RTL) filled with an expansible medium. Surface treatment: Cover and visible graduation cap in white RAL 9016. Marking: TAH, flow direction arrows, II-Designation. Pipe connection: Pipe-side G 3/4 adaptor with cone suitable for compression fittings for plastic, copper, precision steel and multi-layer pipe. The products, texts, photographs, graphics and diagrams in this document may be subject to alteration by IMI Hydronic Engineering without prior notice or reasons being given. For the most up to date information about our products and specifications, please visit www.imi-hydronic.com.
1.1 2.1 2.2 2.3 2.4 2.5 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 23.1 25.1 26.1 27.1 28.1 29.1 30.1 31.1 32.1 33.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 49.2 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 59.1 59.2
Termostatski radijatorski ventil sa automatskim ograničenjem protoka Termostatski radijatorski ventil Eclipse ima jedinstveni ograničivač protoka koji eliminiše bilo kakvo prekoračenje protoka. Zahtevani protok se podešava direktno na ventilu. Podešeni protok neće biti veći čak ni kada postoje znatne promene u instalaciji bilo da neki ventili zatvaraju bilo da je reč o jutarnjem startovanju sistema grejanja. Ventil reguliše protok nezavisno od promene diferencijalnog pritiska. Prema tome, nisu potrebni komplikovani proračuni za određivanje pozicije predregulacije. Ključne karakteristike Integrisani ograničivač protoka Ne dozvoljava prekoračenje protoka Jednostavno podešavanje Kako bi se postigao projektovani protok Opseg protoka od 10 do 150 l/h Za veću fleksibilnost Sva tela ventila označena sa ‘’II’’ mogu biti modifikovana kao Eclipse Pr: Calypso exact, Calypso, Mikrotherm F, Multilux, Multilux 4-Set Perfect for renovation Standard dimensions and easy flow sizing Tehnički opis Namena: Sistemi grejanja. Funkcija: Kontrola Regulacija protoka Zatvaranje Dimenzije: Nazivni pritisak: Temperatura: Max. radna temperatura: 120°C, sa zaštitnom kapom ili aktuatorom 100°C. Min. radna temperatura: -10°C Opseg protoka: Protok se može predregulisati u opsegu: 10-150 l/h. Podešavanje protoka do 150 l/h. (Max. nominalni ptorok qmN na 10 kPa prema EN 215: 115 l/h) Diferencijalni pritisak (ApV): Max. differencijalni pritisak: Min. differencijalni pritisak: 10 – 100 l/h = 10 kPa 100 – 150 l/h = 15 kPa Materijal: Telo ventila: Mesing O-prsten: EPDM guma Disk ventila: EPDM guma Povratna opruga: Nerđajući čelik Uložak ventila: Mesing, PPS (polyphenylsulphide) Ceo termostatski uložak može se zameniti korišćenjem IMI Heimeier alata bez pražnjenja instalacije. Vreteno: Niro čelik sa duplim O-prstenastim zaptivanjem. Površinska obrada: Telo ventila i fiting su niklovani. Označavanje: THE, DN, oznaka zemlje, smer protoka i KEYMARK-oznaka. II+ oznaka. Narandžasta zaštitna kapa. Standardi: Telo ventila prema sledećim zahtevima: – KEYMARK sertifikovano i testirano prema DIN EN 215. Cevni priključci: Unutrašnji navoj je projektovan za povezivanje na cevi sa navojem, ili u kombinaciji sa kompresionim spojnicama, na bakarne ili precizne čelične cevi. U kombinaciji sa duplom zateznom spojnicom pogodan je za povezivanje na višeslojne cevi. Priključak na termostatsku glavu i aktuator: IMI Heimeier M30x1.5 Proizvodi, tekstovi, fotografije, grafikoni i dijagrami u ovom dokumentu mogu biti predmet promene od strane IMI Hydronic Engineering-a bez prethodnog obaveštenja ili obrazloženja. Za najažurnije informacije o našim proizvodima i specifikacijama, molimo Vas posetite www.imi-hydronic.com.