http___www.trox.hr_stru_C4_8Dnost_projektiranje-dcb5fcd39eaa68ba_1.xml
1.1 2.1 3.1 3.2 4.1 4.2 5.1 6.1 7.1 7.2 8.1 8.2 8.3 9.1 9.2 10.1 11.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 27.1 28.1 29.1 30.1 31.1 33.1 34.1 35.1 37.1 38.1 39.1 40.1 41.1
Differential pressure transducers based on the dynamic measurement principle for volume flow rate measuring units Type VMR or VME Application Standard filtration in comfort air conditioning systems allows for use of the transmitter in the supply air without additional dust protection. Since a partial volume flow is passed through the differential pressure transducer in order to measure the volume flow rate, please note: For this application the Universal controller is only used for measuring the differential pressure and for transforming the measured value into a linear voltage signal. Connections for setpoint value signal and actuator are not relevant, and neither are the corresponding technical data. Parts and characteristics Functional description The volume flow rate is determined by measuring the effective pressure. For this reason the measuring unit is fitted with an effective pressure sensor. The integral differental pressure transducer transforms the effective pressure into a voltage signal. The volume flow rate actual value is hence available as a voltage signal. The factory setting is such that 10 V DC always corresponds to the nominal volume flow rate (Vnom). Voltage ranges are factory stored in the controller. Changes on the customer's site can easily be carried out using an adjustment device or a notebook with service tool. Volume flow controller VRD3 Any attachments are to be defined with the order code of the volume flow rate measuring unit. Application Signal voltage range Parts and characteristics Dynamic differential pressure transducers for volume flow rate measuring units Share page Recommend this page Recommend this page by sending a link by mail. Share page Thank you for your recommendation! Your recommendation has been sent and should arrive shortly. Contact We are here for you Please specify your message and type of request. Contact Thank you for your message! Your message is send and will be processed shortly. Our department for Service-Requests will contact you asap. For general question regarding products or services you can also call: Contact We are here for you Please specify your message and type of request. Contact Thank you for your message! Your message is send and will be processed shortly. Our department for Service-Requests will contact you asap. For general question regarding products or services you can also call:
1.1 2.1 3.1 4.1 4.2 4.3 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 30.1 31.1 32.1 33.1 34.1 36.1 37.1 38.1 40.1 41.1 42.1 43.1 44.1
Jednostavno, precizno i učinkovito Tri optimirane kontrolne jedinice odlikuju se najvišom kvalitetom, jednostavnim instaliranjem i preciznim radom. Projektiranje tehničkih usluga u građevinarstvu složen je zadatak. Očekivanja vlasnika često su jednaka: ekološka i ekonomska održivost uz istodobno visoku udobnost i male troškove ulaganja. Ne postoje međutim dva potpuno jednaka objekta ‑ različiti tipovi građevina i njihovo korištenje, bilo da se radi o novoj gradnji ili obnovi, zahtijevaju individualne koncepte. Pronađite najbolja klimatizacijska i ventilacijska rješenja za svoje objekte! Ovdje možete saznati više o sljedećim temama: U kupovini Uredi Laboratoriji Hoteli Zračne luke Škole, centri za dnevnu skrb i druge obrazovne ustanove Bolnice Stadioni Muzeji Čisti zrak Naši priručnici za projektiranje pomažu vam u individualiziranom projektiranju klimatizacijskih sustava. Uz pomoć kriterija projektiranja, zakonskih propisa i standarda, objašnjenja o korištenju pojedinih proizvoda, studija ekonomske izvodljivosti, arhitektonskih mogućnosti i detaljnih pregleda proizvoda možete odabrati komponente, uređaje i sustave koji najbolje odgovaraju vašem projektu. Priručnik za projektiranje AIRFLOWCONTROL Priručnik za projektiranje sustava zrak-voda Kontakt Tu smo za vas Preporučite ovu stranicu slanjem poveznice poštom. Podijeli stranicu Zahvaljujemo na preporuci! Vaša je preporuka poslana i trebala bi stići uskoro. Kontakt Tu smo za vas Navedite svoju poruku i vrstu zahtjeva Kontakt Zahvaljujemo na vašoj poruci! Vaša je poruka poslana i ubrzo će biti obrađena. Naš odjel za servisne zahtjeve što skorije će vas kontaktirati. Za opća pitanja u vezi s proizvodima ili uslugama možete i nazvati: Kontakt Tu smo za vas Navedite svoju poruku i vrstu zahtjeva Kontakt Zahvaljujemo na vašoj poruci! Vaša je poruka poslana i ubrzo će biti obrađena. Naš odjel za servisne zahtjeve što skorije će vas kontaktirati. Za opća pitanja u vezi s proizvodima ili uslugama možete i nazvati: