http___www.trox.hr_stru_C4_8Dnost_projektiranje-dcb5fcd39eaa68ba_1.xml
1.1 2.1 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 11.2 12.1 13.1 14.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 25.2 26.1 27.1 27.2 28.1 29.1 30.1 31.1 32.1 33.1 34.1 34.2 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 45.1 46.1 47.1 48.1 49.1 50.1 51.1 52.1 53.1 54.1 55.1 56.1 57.1 58.1 59.1 60.1 61.1 62.1 63.1 64.1 65.1 66.1 67.1 68.1 70.1 71.1 72.1 73.1 74.1 76.1 77.1 78.1 80.1 81.1 82.1 83.1 84.1
Circular disc valves with manually adjustable annular gap Application Special characteristics Nominal sizes Parts and characteristics Materials and surfaces Standards and guidelines Maintenance Functional description Extract air valves extract air from rooms and lead it into the extract air part of the air conditioning system. Type LVS disc valves have a valve disc that can be turned. This valve disc facilitates volume flow rate balancing for commissioning. Quick sizing tables provide a good overview of the volume flow rates and corresponding sound power levels and differential pressures. Sizing example Given data Extract air valve Maximum sound power level 30 dB(A) Quick sizing Type LVS Selectable nominal sizes: 125, 160, 200 Selected: LVS/125 LVS/100, LVS/125, sound power level and total differential pressure LVS/160, sound power level and total differential pressure LVS/200, sound power level and total differential pressure Circular disc valves as extract air devices, preferably for small rooms. For installation into walls and suspended ceilings. Ready-to-install component which consists of a valve casing with cross bar, a valve disc with threaded spindle, and an installation subframe. The valve disc can be turned for volume flow rate balancing. The valve setting can be fixed with a lock nut. Spigot suitable for ducts to EN 1506 or EN 13180. Sound power level of the air-regenerated noise measured according to EN ISO 5135. Special characteristics Materials and surfaces Technical data Sizing data This specification text describes the general properties of the product. Texts for variants can be generated with our Easy Product Finder design programme. Order example: LVS/160 Installation and commissioning These are only schematic diagrams to illustrate installation details. Installation opening Principal dimensions ØD [mm] Outer diameter of the spigot ØD₁ [mm] Outer diameter of the diffuser face L₁ [mm] Length of the face cover ring L₂ [mm] Installed length m [kg] Weight Nomenclature LWA [dB(A)] A-weighted sound power level of air-regenerated noise V [m³/h] and [l/s] Volume flow rate Atz [K] Supply air to room air temperature difference Apt [Pa] Total differential pressure All sound power levels are based on 1 pW. Share page Recommend this page Recommend this page by sending a link by mail. Share page Thank you for your recommendation! Your recommendation has been sent and should arrive shortly. Contact We are here for you Please specify your message and type of request Contact Thank you for your message! Your message is send and will be processed shortly. Our department for Service-Requests will contact you asap. For general question regarding products or services you can also call: Contact We are here for you Please specify your message and type of request Contact Thank you for your message! Your message is send and will be processed shortly. Our department for Service-Requests will contact you asap. For general question regarding products or services you can also call:
1.1 2.1 3.1 4.1 4.2 4.3 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 15.1 16.1 17.1 18.1 19.1 20.1 21.1 22.1 23.1 24.1 25.1 26.1 27.1 28.1 30.1 31.1 32.1 33.1 34.1 36.1 37.1 38.1 40.1 41.1 42.1 43.1 44.1
Jednostavno, precizno i učinkovito Tri optimirane kontrolne jedinice odlikuju se najvišom kvalitetom, jednostavnim instaliranjem i preciznim radom. Projektiranje tehničkih usluga u građevinarstvu složen je zadatak. Očekivanja vlasnika često su jednaka: ekološka i ekonomska održivost uz istodobno visoku udobnost i male troškove ulaganja. Ne postoje međutim dva potpuno jednaka objekta ‑ različiti tipovi građevina i njihovo korištenje, bilo da se radi o novoj gradnji ili obnovi, zahtijevaju individualne koncepte. Pronađite najbolja klimatizacijska i ventilacijska rješenja za svoje objekte! Ovdje možete saznati više o sljedećim temama: U kupovini Uredi Laboratoriji Hoteli Zračne luke Škole, centri za dnevnu skrb i druge obrazovne ustanove Bolnice Stadioni Muzeji Čisti zrak Naši priručnici za projektiranje pomažu vam u individualiziranom projektiranju klimatizacijskih sustava. Uz pomoć kriterija projektiranja, zakonskih propisa i standarda, objašnjenja o korištenju pojedinih proizvoda, studija ekonomske izvodljivosti, arhitektonskih mogućnosti i detaljnih pregleda proizvoda možete odabrati komponente, uređaje i sustave koji najbolje odgovaraju vašem projektu. Priručnik za projektiranje AIRFLOWCONTROL Priručnik za projektiranje sustava zrak-voda Kontakt Tu smo za vas Preporučite ovu stranicu slanjem poveznice poštom. Podijeli stranicu Zahvaljujemo na preporuci! Vaša je preporuka poslana i trebala bi stići uskoro. Kontakt Tu smo za vas Navedite svoju poruku i vrstu zahtjeva Kontakt Zahvaljujemo na vašoj poruci! Vaša je poruka poslana i ubrzo će biti obrađena. Naš odjel za servisne zahtjeve što skorije će vas kontaktirati. Za opća pitanja u vezi s proizvodima ili uslugama možete i nazvati: Kontakt Tu smo za vas Navedite svoju poruku i vrstu zahtjeva Kontakt Zahvaljujemo na vašoj poruci! Vaša je poruka poslana i ubrzo će biti obrađena. Naš odjel za servisne zahtjeve što skorije će vas kontaktirati. Za opća pitanja u vezi s proizvodima ili uslugama možete i nazvati: