http___radyator.nedir.com__1.xml
1.1 2.1 2.2 2.3 3.1 3.2 3.3 3.4 3.5 5.1 5.2 6.1 6.2 6.3 6.4 6.5 7.1 8.1 9.1 9.2 9.3 11.1 11.2 11.3 12.1 13.1 14.1 15.1 16.1 16.2 16.3 16.4 16.5 18.1 19.1
This section is from the book "Cyclopedia Of Architecture, Carpentry, And Building", by James C. et al. Also available from Amazon: Cyclopedia Of Architecture, Carpentry And Building>. The efficiency of a radiator, that is, the B. T. U. which it gives off per square foot of surface per hour, depends upon the difference in temperature between the steam in the radiator and the surrounding air, the velocity of the air over the radiator, and the quality of the surface, whether smooth or rough. In ordinary low-pressure heating the first condition is practically constant, but the second varies somewhat with the pattern of the radiator. An open design which allows the air to circulate freely over the radiating surfaces is more efficient than a close pattern and for this reason a pipe coil is more efficient than a radiator. In a large number of tests of cast iron radiators, working under usual conditions, the heat given off per square foot of surface per hour, for each degree difference in temperature between the steam and surrounding air, was found to vary from about 1.3 to 1.7 B. T. U. The temperature of steam at 3 pounds pressure is 220 degrees, and 220 - 70 = 150, which may be taken as the average difference between the temperature of the steam and the air of the room, in ordinary low-pressure work. If we take the mean of the above results, that is, 1.5 we shall have 150 X 1.5 = 225 B. T. U. as the efficiency of an average cast iron radiator. A circulation coil made up of pipes from 1 to 2 inches in diameter will easily give off 300 B. T. U. under the same conditions, and a shallow pipe radiator of standard height may be safely counted upon to give 260. These efficiencies are lower than are given by some engineers, but if the sizes are taken from trade catalogues it is not safe to go much above these figures. If the radiator is to be used for warming rooms which are to be kept at a temperature above or below 70 degrees, the radiating surface may be changed in the same proportion as the difference in temperature between the steam and the air. For example - if a room is to be kept at a temperature of 60° the efficiency of the radiator becomes 160/150 X 225 = 240; that is the efficiency varies directly as the difference in temperature between the steam and the air of the room. It is not customary to consider this unless the steam pressure should be raised to 10 or 15 pounds or the temperature of the rooms changed 15 or 20 degrees from the normal. From the above it is easy to compute the size of radiator for any given room. First compute the heat loss per hour by radiation and conduction, in the coldest weather, then divide the result by 225 for cast iron radiators, 260 for pipe radiators and 300 for pipe coils. It is customary to make the radiators of such size, that they will warm the rooms to 70 degrees in the coldest weather. This varies a good deal in different localities, even in the same state, and the lowest temperature for which we wish to provide must be settled upon before any calculations are made. In New England and through the Middle and Western States it is usual to figure on warming a building to 70 degrees when the outside temperature is from zero to 10 degrees below. The makers of radiators publish in their catalogues, tables giving the square feet of heating surface for different styles and heights, and these can be used in determining the number of sections required for all special cases. If pipe coils are to be used, it becomes necessary to reduce square feet of heating surface to linear feet of pipe; this can be done by means of the factors given below. The size of radiator is only made sufficient to keep the room warm after it is once heated, and no allowance is made for "warming up," that is, the heat given off by the radiator is just equal to that lost through walls and windows. This condition is offset in two ways - first, when the room is cold, the difference in temperature between the steam and air of the room is greater and the radiator is more efficient, and second the radiator is proportioned for the coldest weather so that for a greater part of the time it is larger than necessary. This last condition is one of the disadvantages of direct steam heating; if steam is on the radiator at all it will give off the same amount of heat regardless of the outside temperature. Example. - A schoolroom is to be warmed with circulation coils of 1 1/4-inch pipe. The heat loss is 30,000 B. T. U. per hour; what length of pipe will be required? The heating surface of a pipe coil will be 30,000 = 100 square feet. Therefore we need 2.3 X 100 = 230 linear feet of 11/4-inch pipe. Location. Radiators should be placed in the coldest part of the room if possible, as under windows or near outside doors. In living rooms it is often desirable to keep the windows free, in which case the radiators may be placed at one side. Circulation coils are run along the outside walls of a room under the windows. Sometimes the position of the radiators is decided by the necessary location of the pipe risers, so that a certain amount of judgment must be used in each special case as to the best arrangement to suit all requirements. Continue to: architecture, carpentry, building, superintendence, contracts, specifications, building law, stair-building, estimating, masonry, reinforced concrete, structural engineering, architectural drawing, sheet metal work, heating, ventilating
1.1 2.1 3.1 4.1 5.1 6.1 7.1 8.1 9.1 10.1 11.1 12.1 13.1 14.1 23.1 33.1 34.1 35.1 36.1 37.1 38.1 39.1 40.1 41.1 42.1 43.1 44.1 45.1
Radyatör nedir? Sıcak sulu ısıtma sistemlerinde, ısıtılacak mahallin uygun bir yerine yerleştirilen ısıtıcı yüzeyi geniş cihaz. Günümüzde çok yaygın olarak kullanılan kaloriferli, sıcak sulu ısıtma sistemlerinde, kazan dairesinde ısınan sıcak su; daha çok pencere önlerindeki radyatörlere üstten girerek alttan dönüş yapar ve dönüş kolon boruları ile tekrar kazan dairesine gelir. Dönen su sıcaklığı, giden sıcak suya göre ortalama 20°C daha azdır. En düşük dış hava sıcaklığına göre Max.90°C sıcaklıkta su radyatöre girer ve 70°C’de radyatörden çıkar. Bu sebeple radyatörlerin üst kısmı alttan daha fazla sıcaktır. Çünkü, radyatöre üstten giren sıcak su, alta inene kadar sıcaklığı azalmakta, ısısını odanın havasına vermektedir. Isıtılan havayı bir akışkan olarak kabul edersek, radyatör petekleri arasında alttan üste doğru ısınan hava yükselmekte, konveksiyon ısı transferi gerçekleşmektedir. Radyatörlerin verdiği toplam ısının % 80’i konveksiyon, % 20’si de radyasyon yoluyla oda havasına intikal eder Radyatör üzerinde meydana gelen hava akımı neticesinde, mahallin bütün havası radyatör üzerinden geçerek ısıtılmış olur. Ancak hava içindeki görülmeyen toz zerrecikleri, radyatörün üzerindeki tavan yüzeyinde yoğunlaşan neme yapışarak, zamanla is lekesi yapmaktadır. Radyatörler, demir dilimlerinin birbirine eklenmiş şeklidir. malzeme cinsine ve biçimlerine göre bağlı olarak aşağıdaki şekilde sınıflandırılırlar. 1) Dökme demir radyatörler, 2) Çelik radyatörler, 3) Dilimli radyatörler, 4) Panolu radyatörler. Kalorifer tesisatı hesabında, ısıtılacak mahallin konfor sıcaklığı ve ısı kaybına göre dilim sayısı değişik olabilir. 30, 50, 100 cm boylarında çok değişik tip radyatörler vardır. Radyatörlerin cazip görünüşlü ve daha yüksek ısı verimli olabilmesi için, alüminyum pres dökümlü kanatlı radyatörlerle, panel tip çelik radyatörler imal edilmiştir. Radyatörlerin giriş ve çıkışında mutlaka birer ventil ve havasını almak için pürjör olmalıdır. Radyatör grubu alttan iki adet konsol ve üstten bir adet kelepçe ile duvara tespit edilmiştir. Radyatörlerin yerleştirilmesinde dikkat edilecek önemli hususlar şunlardır: 1. Radyatörler pencere altındaki duvarlara yerleştirilmelidir. İç duvarlara yerleştirilmeleri mahzurludur. 2. Radyatörler yerleştirildikleri duvarda en az 5 cm ve tabandan ise 7 cm mesafede olmalıdır. Bu şekilde yapılmazsa, çevre havası radyatör yüzeylerini iyi bir şekilde yalayamaz ve radyatörün verimi düşer. 3. Radyatörlerin önleri, yanları ve üstleri süs, dekarasyon gibi maksatlarla hiçbir şekilde kapatılmamalıdır. Bu kapatmaların derecesine bağlı olarak radyatörün ısıtma verimi % 10 ile % 40 arasında azalır. Böylece radyatörler konulduğu mahalleri ısıtamaz hale gelirler. 4. Radyatörlerin önleri tavandan aşağıya kadar sarkan perdelerle kapanmamalıdır. Çünkü alttan girip ısınan hava, perde ile önü kapalı olduğu için oda içine geri dönemez, ısı camdan boşu boşuna gider. 5. Radyatörlerin arka kısmına isabet eden dış duvar 3 cm kalınlığında strafor veya cam yünüyle kaplanmalıdır. Isıtma gayesiyle, elektrik enerjisiyle çalışan tek radyatörler içinde ısıtıcı rezistans ve ısı transfer yağı vardır. Bu tip radyatörler büro ve iş yerlerinde kullanılmaktadır. Radyatörler çok uzun ömürlü olmakla beraber, içindeki suyun donması halinde çatlar ve tahrip olur. Onun için de kullanılmayan ev veya odalardaki radyatörlerin kapalı kalması doğru değildir. Giriş ventilinden kısık vaziyette sıcak su radyatöre girerse, don tehlikesine karşı tedbir alınmış olur. Isı enerjisinden (yakıttan) tasarruf etmek ve odalarda normal konfor sıcaklığını sağlamak gayesiyle, dış hava sıcaklığındaki değişimlere göre, radyatörlere giren su sıcaklığını ayarlamak gerekir. Bu ayarı otomatik olarak yapan otomatik kontrollu cihazlar olduğu gibi; sistemde ısıtıcı eşanjör üzerindeki termostatik vanadan da elle ayarlamak mümkündür. Eşanjör olmayan sistemde, kalorifer kazanı üzerindeki termostat aletini dış hava sıcaklığına göre ayarlamalıdır. Dış Hava sıcaklığı °C -20 -16 Termostat ayarı °C Kışın en düşük sıcaklığı -20°C olan bir bölge için, kazan çıkış suyu sıcaklığı tablosu. Isıtılan mahalde normal konfor sıcaklığını 20,22°C sabit tutmak ve enerjiden (yakıttan) tasarruf edebilmek için dış hava sıcaklığına göre yapılacak termostat ayarı ve radyatörlere gidecek kazan çıkış suyu sıcaklığı çizelgede gösterilmiştir. Benzinli ve su soğutmalı otomobil motorlarında bulunan radyatör, motoru soğutma gayesiyle kullanılır. Soğutma yüzeyi çok geniş olup, ince küçük peteklerden müteşekkildir. Motor gövdesinde ısınan su, devridaim pompası tarafından radyatöre girer ve çıkar. Radyatör önündeki krank miline bağlı pervane, radyatörün petekleri arasından hava geçmesini sağlar. Radyatöre üstten giren sıcak su alta inene kadar bir miktar soğumuş olur. Arızalara sebebiyet vermemek için radyatöre, kireçten arındırılmış sular koymak gerekir. Soğuk havada motor çalıştıktan sonra su konulmalı, motor sıcak iken radyatöre soğuk su konulmamalıdır. Sözlükte "radyatör" ne demek? 1. Bir akaryakıtın yanmasından ya da sıcak bir akışkandan aldığı ısıyı dışarı ileten dilimli borulardan oluşan ısıtma aygıtı. 2. Bağlı bulunduğu motordaki ısı derecesinin yükselmesini önleyen soğutucu. Cümle içinde kullanımı Radyatörün suyunu tazeledikten sonra virajlı yokuşu tırmanmaya başladı. - A. Gündüz Radyatör kelimesinin ingilizcesi n. radiator Köken: Fransızca