Palm kernel shells are widely used in fluidized bed combustion-based power plants in Japan and South Korea. The key advantages of fluidized bed combustion (FBC) technology are higher fuel flexibility, high efficiency and relatively low combustion temperature. FBC technology, which can either be bubbling fluidized bed (BFB) or circulating fluidized bed (CFB), is suitable for plant capacities above 20 MW. Palm kernel shells (PKS) is more suitable for CFB-based power plant because its size is less than 4 cm.
With relatively low operating temperature of around 650 – 900 oC, the ash problem can be minimized. Certain biomass fuels have high ash levels and ash-forming materials that can potentially damage these generating units. In addition, the fuel cleanliness factor is also important as certain impurities, such as metals, can block the air pores on the perforated plate of FBC unit. It is to be noted that air, especially oxygen, is essential for the biomass combustion process and for keeping the fuel bed in fluidized condition.
The requirements for clean fuel must be met by the provider or seller of the biomass fuel. Usually the purchasers require an acceptable amount of impurities (contaminants) of less than 1%. Cleaning of PKS is done by sifting (screening) which may either be manual or mechanical.
In addition to PKS, biomass pellets from agricultural wastes or agro-industrial wastes, such as EFB pellets which have a high ash content and low melting point, can also be used in CFB-based power plants. More specifically, CFBs are more efficient and emit less flue gas than BFBs.
The disadvantages of CFB power plant is the high concentration of the flue gas which demands high degree of efficiency of the dust precipitator and the boiler cleaning system. In addition, the bed material is lost alongwith ash and has to be replenished regularly.
The commonly used bed materials are silica sand and dolomite. To reduce operating costs, bed material is usually reused after separation of ash. The technique is that the ash mixture is separated from a large size material with fine particles and silica sand in a water classifier. Next the fine material is returned to the bed.
Currently power plants in Japan that have an efficiency of more than 41% are only based on ultra supercritical pulverized coal. Modification of power plants can also be done to improve the efficiency, which require more investments. The existing CFB power plants are driving up the need to use more and more PKS in Japan for biomass power generation without significant plant modifications.